phpp Passive House Verification 110 S Race St # 202 Urbana, IL 61801 USA Certificate THE PASSIVE HOUSE INSTITUTE US certifies Building: Passive House in the Woods Passive House in the Woods, 908 Kirkwood Way North, Town of Hudson, WI 54016 Location and Climate: Town of Hudson, WI Minneapolis TMY3 Owner: Gary Konkol Street: 908 Kirkwood Way North Postcode/City: Town of Hudson, WI 54016 Architect/Designer : Tim Eian/TE Studio, Ltd., Minneapolis MN Country: USA Mechanical Systems: TE Studio, Ltd. & Luefta GmbH, Minneapolis MN Building Type: Single Family Detached Builder: Morr Construction Services, Inc., Shoreview, MN Home Owner(s) / Client(s): Gary Konkol Street: 1 Kinsman as a Postcode/City: Hudson, WI 54016 Architect: Street: Tim Eian/TE Studio, Ltd. 3429 Benjamin St. NE Quality Approved Passive House Postcode/City: Minneapolis, MN 55418 The planning of this building meets the criteria for Passive Houses established by Mechanical System: TE Studio, Ltd. & Luefta GmbH the Passive House Institute. Street: 3429 Benjamin St. NE If built as specified, the building will meet the following performance standards: Postcode/City: Minneapolis, MN 55418 • The building features excellent insulation all around and best-practice detailing of component connection Year of Construction: 2010 0.20 with regard to building physics. Appropriate summer shading has been considered. Heating and cooling A/V Ratio: demands each are limited to Number of Dwelling Units: 1 Interior Temperature: 20.0 °C 15 kWh per m² living area and year [4.75 kBTU/ft²yr] or 10 W/m² [3.17 BTU/ft²] peak Enclosed Volume Ve: 820.5 m3 Internal Heat Gains: 2.1 W/m2 load Number of Occupants: 2.0 • The building envelope features excellent air tightness in accordance with ISO 9972, thereby guaranteeing the minimization of ventilation losses and an interior free of drafts. The air change rate of the buildingSpecific Demands with Reference to the Treated Floor Area envelope at 50 Pascal pressure differential is limited to Treated Floor Area: 164.5 m2 0.6 ACH, in reference to the building’s volume Applied: #N/A PH Certificate: Fulfilled? • The building features a balanced ventilation system with high-rate filters, highly efficient heat recovery Specific Space Heat Demand: 11 kWh/(m2 a) 15 kWh/(m2 a) Yes and low electric power consumption. The result is excellent indoor air quality as well as an exceptionally low energy consumption overall. Annual Heat Demand QH 1740 kWh/a • The primary energy demand for space conditioning, domestic hot water, ventilation and household Pressurization Test Result: 0.3 h -1 0.6 h-1 Yes electricity, under normal conditions, is below Specific Primary Energy Demand 120 kWh per m² living area and year [38 kBTU/ft²yr] (DHW, Heating, Cooling, Auxiliary and Household Electricity) : 65 kWh/(m2 a) 120 kWh/(m2a) Yes Specific Primary Energy Demand This certificate is valid only in conjunction with the requisite supporting documents containing the exact (DHW, Heating and Auxiliary Electricity) : 41 kWh/(m2 a) specifications and values upon which certification is based. Passive Houses are highly comfortable in Specific Primary Energy Demand summer as well as in winter and can be conditioned with very little energy input, e.g. by fresh air heating and Energy Conservation by Solar Electricity: 79 kWh/(m2 a) cooling. The building shell of a Passive House has uniformly warm interior surfaces: interior surface Heating Load: 17 W/m2 temperatures of exterior shell components differ insignificantly from the indoor air temperatures. Under Heating Load PH 2869 W normal conditions, the occurrence of drafts has been eliminated completely by means of the superior air Frequency of Overheating: 2 % over 25 °C tightness. The ventilation system steadily assures excellent indoor air quality. Space conditioning costs in a 1 15 kWh/(m2a) Yes Passive House are very low. Due to the extremely low energy consumption, Passive Houses offer a security Specific Useful Cooling Energy Demand: kWh/(m2 a) against future rise in energy prices and energy scarcity. Moreover the environment is ideally protected as Cooling Load: 7 W/m 2 energy resources are spent very economically and only small amounts of carbon dioxide (CO2) and other pollutants are emitted.We confirm that the values given herein have been Issued on: Issued: Urbana, Sep 19, 2010determined following the PHPP methodology and basedon the characteristic values of the building. The calculations signed: Katrin Klingenberg, Executive Director, PHIUSwith PHPP are attached to this application.
heating load10.6 kWh/(m2 a) [3.36 kBTU/sf yr](limit: 15 kWh or 4.75 kBTU)about 30% less than Passive House requirement
heating load2,869 Watts or 17W/m2Does not meet PH limit of 10W/m2 for heatingover the air: Cold-climate conundrum
source energy 106 kWh/(m 2 a) [33.6 kBTU/sf yr] Verification with 4.7 people 65 kWh/(m2 a) [20.6 kBTU/sf yr] Design with 2 people (limit: 120 kWh or 38.05 kBTU)
managing protrusions SOUTH FACE OF LATTICE WALL (EXTERIOR) SCHEDULE EXTERIOR EAST ELEVATION 1. PV INVERTER (EC) AT FRONT ENTRY - MIRRORED! 13.8"H X 17.8" W X 9.3"D 2. 100-AMP SERVICE FOR PV SYSTEMS (EC) 7-10" 13"H X 14"W X 4.25"D 4" 4" 3. 300-AMP ELECTRICAL PANEL (EHS) 2" 9" 8" 1-3" 4" 4 SIZE T.B.D. 4. PHONE/CABLE BOX (EHS) SIZE T.B.D. 5. 320-AMP ELECTRICAL METER (EHS) 7 6 5 4 30"H X 15"W 6. 100-AMP SOLAR PRODUCTION METER (EC) 12"H X 8"W 7. 60-AMP SOLAR AC DISCONNECT (EC) OUTSIDE 3/4" CONDUIT DC FROM POLE PV (EC) 14"H X 9"W 3/4" CONDUIT: AC TO POLE PV (EC) INCOMING AC FROM METER (EHS) INSIDE TO EXTERIOR GROUND (EHS) 1" CONDUIT: TO AC DISCONNECT (EC) FROM ROOF PV (EC) CONDUIT TO GARAGE NOTES - SCHEMATIC LAYOUT - VERIFY DIMENSIONS IN THE FIELD TO LOW VOLTAGE PANEL - RUN EXPOSED EXTERIOR CONDUIT PLUMB TO PROTRUSION, AVOID BENDS AND OFFSETS KEY OUTBOUND LINE SPACE FOR CL LUTRON 1 2 3 SYSTEM INBOUND LINE 8-3 3/8" 1 1 CONNECTION MIN. INVERTER CLEARANCE (PER EC) (EC) = ENERGY CONCEPTS (EHS) = ENHANCED HOME SYSTEMS 5 10-3 1/4" INTERIOR EAST ELEVATION AT MECHANICAL ROOM NOTE: DETAIL IS SUBJECT TO PRIOR REVIEW AND APPROVAL BY SUPPLIER AND INSTALLER, MAINTAIN AIR-TIGHTNESS! TE STUDIO, LTD. PASSIVE HOUSE IN THE WOODS A-7.3.1 3429 BENJAMIN ST. NE MECHANICAL ROOM EAST SCALE: 1/2" = 1-0" MINNEAPOLIS, MN 55418 Date printed: 11/2/10 612-246-4670 office 612-605-3200 fax PH-01 Konkol [testudioserver] www.teStudio.com Drawn by: JCC, TDE
managing protrusions REFERENCE DETAILS: SUGGESTED INSTALLATION: - STO W 260 1) INSTALL PIPE 2) INSTALL COMPRESSION TAPE NOTE: 3) INSULATE TIGHT TO PIPE AND COMPRESS TAPE - USE ONLY STO CERTIFIED SEALANT 4) INSTALL FINISH SYSTEM - COLOR MATCH CAULK TO FACADE COLOR 11" EIFS 11" ICF EXTERIOR INTERIOR 12" PE PIPE, SLEEVE FILL GAPS WITH EXPANSION FOAM STO GUARD SCHEDULED WALL FINISH WET FLASHING SYSTEM SEALANT JOINT BRING INSULATION TAPE ICF TO DUCT, TIGHT TO PIPE AIR-TIGHT CONNECTION 2" ARMAFLEX PIPE INSULATION COMPRESSION TAPE INSULATED DUCT O.D. 180MM (LUEFTA) CUT BACK FINISH AND CAULK NOTE: DETAIL IS SUBJECT TO PRIOR REVIEW AND APPROVAL BY SUPPLIER AND INSTALLER, MAINTAIN AIR-TIGHTNESS! TE STUDIO, LTD. PASSIVE HOUSE IN THE WOODS A-8.2.3 3429 BENJAMIN ST. NE TYPICAL DUCT WALL PROTRUSION SCALE: 1 1/2"= 1-0" MINNEAPOLIS, MN 55418 Date printed: 11/2/10 612-246-4670 office 612-605-3200 fax PH-01 Konkol [testudioserver] www.teStudio.com Drawn by: TDE
making connections EXTERIOR INTERIOR STO GUARD 11" 3" WET-FLASHING SYSTEM 4" 4" X 4" MOUNTING BRACKET INSULATED PANEL FOR WAREMA SHADE (OPTIWIN) SYSTEM (OPTIWIN) VACUUM INSULATED PANEL TALLEST ASSEMBLY (OPTIWIN), HANDLE WITH -SHOWN EXTREME CARE! DO NOT APPROX. 13-5/8" PUNCTURE, STRESS, OR BEND SHORTEST ASSEMBLY -NOT SHOWN AIR TIGHT CONNECTION APPROX. 11-1/16" DOUBLE SIDED BUTYL TAPE PER MANF. (OPTIWIN) STO EIFS ICE & WATER SHIELD SUBSTRATE (OPTIWIN) 1 1/4" LSL FRAMING BUCK WAREMA SHADING UNIT, SHOWN FOR REFERENCE ONLY REFERENCE DETAILS: - STO W 710 ROUGH OPENING NOTE: VERIFY DIMENSIONS WITH ACTUAL PRODUCT 3 1/16" 5 5/8" 3 1/4" 1/4" 7 9/16" 3 1/4" 4 3/4" PLASTER RETURN DRIP EDGE 3" 11" WAREMA TRACK "ALU2WOOD" WINDOW (OPTIWIN) (OPTIWIN) NOTE: DETAIL IS SUBJECT TO PRIOR REVIEW AND APPROVAL BY SUPPLIER AND INSTALLER, MAINTAIN AIR-TIGHTNESS! TE STUDIO, LTD. PASSIVE HOUSE IN THE WOODS A-8.3.2 3429 BENJAMIN ST. NE TYPICAL WINDOW HEAD WITH SHADE SCALE: 3" = 1-0" MINNEAPOLIS, MN 55418 Date printed: 11/2/10 612-246-4670 office 612-605-3200 fax PH-01 Konkol [testudioserver] www.teStudio.com Drawn by: TDE