Slideshare uses cookies to improve functionality and performance, and to provide you with relevant advertising. If you continue browsing the site, you agree to the use of cookies on this website. See our User Agreement and Privacy Policy.

Slideshare uses cookies to improve functionality and performance, and to provide you with relevant advertising. If you continue browsing the site, you agree to the use of cookies on this website. See our Privacy Policy and User Agreement for details.

Successfully reported this slideshow.

Like this document? Why not share!

- Amrapali Cloud Ville Sector- 76, Noida by Amrapali Group 297 views
- Mathematical models and numerical s... by CaterinaSavoy 63 views
- You too will be excited about mathe... by Rajiv Shrestha 1294 views
- Simulation & Modelling by Saneem Nazim 2499 views
- Simulation and Modeling by anhdbh 14563 views
- Introduction to Simulation by chimco.net 39553 views

990 views

Published on

characteristics of hydraulic governor-turbines during and

following any disturbance, such as occurrence of a fault,

loss of a transmission line or a rapid change of load. Accurate

modelling of hydraulic System is essential to characterize

and diagnose the system response. In this article the

mathematical modeling of hydraulic turbine is presented. The

model is capable to implement the digital systems for

monitoring and control replacing the conventional control

systems for power, frequency and voltage. This paper presents

the possibilities of modeling and simulation of the hydro power

plants and performs an analysis of different control structures

and algorithms.

No Downloads

Total views

990

On SlideShare

0

From Embeds

0

Number of Embeds

2

Shares

0

Downloads

70

Comments

0

Likes

3

No embeds

No notes for slide

- 1. ACEEE Int. J. on Control System and Instrumentation, Vol. 02, No. 02, June 2011 Development and Simulation of Mathematical Modelling of Hydraulic Turbine 1 2 Gagan Singh and D.S. Chauhan 1 Uttarakhand Technical University, Dehradun, (U.K), India. hod_ee@dit.edu.in 2 Uttarakhand Technical University, Dehradun,(U.K),India. pdschauhan@gmail.comAbstract- Power system performance is affected by dynamic low water storage capacity in the reservoir; therefore thecharacteristics of hydraulic governor-turbines during and plant operation requires a permanent balance between thefollowing any disturbance, such as occurrence of a fault, water flow through turbines and the riverloss of a transmission line or a rapid change of load. Accuratemodelling of hydraulic System is essential to characterizeand diagnose the system response. In this article themathematical modeling of hydraulic turbine is presented. Themodel is capable to implement the digital systems formonitoring and control replacing the conventional controlsystems for power, frequency and voltage. This paper presentsthe possibilities of modeling and simulation of the hydro powerplants and performs an analysis of different control structuresand algorithms. Figure 1: Functional block diagram of hydraulic governor-turbineKey words: mathematical modeling, simulation, hydraulic system interconnected with a power system network.turbine. flow in order to maximize the water level in the reservoir for a maximum efficiency of water use. Next, we will determine the I. INTRODUCTION mathematical model for each component of the hydropower system. Usually, a typical hydroelectric power plant consists ofwater tunnel, penstock, surge tank, hydraulic turbine, speed A. Mathematical modeling of Hydraulic turbinegovernor, generator and electric network. Hydrodynamics The representation of the hydraulic turbine and waterand mechanoelectric dynamics are all involved in such a column in stability studies is usually based on the followingnonlinear dynamic system. Generally, a hydroelectric assumptions:-generating unit has many different operating conditions and The hydraulic resistance is negligible.change in any operating condition results in small or large The penstock pipe is inelastic and the water ishydraulic transients. There are many instances of damage to incompressible.penstock or hydraulic turbine which are most probably The velocity of the water varies directly with theoccurring due to large transients. Hydrodynamics is gate opening and with the square root of the netinfluenced by the performance of hydraulic turbine which head.depends on the characteristics of the water column feeding The turbine output power is proportional to thethe turbine. These characteristics include water inertia, water product of head and volume flow.compressibility and pipe wall elasticity in the penstock. The hydraulic turbine can be considered as an elementDifferent construction of hydropower systems and different without memory since the time constants of the turbine areoperating principles of hydraulic turbines make difficult to less smaller than the time constants of the reservoir, penstock,develop mathematical models for dynamic regime, in order to and surge chamber, if exists, which are series connecteddesign the automatic control systems. Also, there are major elements in the system. As parameters describing the massdifferences in the structure of these models. Moreover, there transfer and energy transfer in the turbine we will considerare major differences due to the storage capacity of the the water flow through the turbine Q and the moment Mreservoir and the water supply system from the reservoir to generated by the turbine and that is transmitted to thethe turbine (with or without surge chamber).The dynamic electrical generator. These variables can be expressed as non-model of the plants with penstock and surge chamber is more linear functions of the turbine rotational speed N, the turbinecomplicated than the run-of-the-river plants, since the water gate position Z, and the net head H of the hydro system.feed system is a distributed parameters system. This paper Q = Q (H, N, Z) (1)will present several possibilities for the modeling of the M = M (H, N, Z) (2)hydraulic systems and the design of the control system. Through linearization of the equations (1) and (2) around II. MODELING OF THE HYDRAULIC SYSTEM the steady state values, we obtain: For run-of-the river types of hydropower plants have a 55© 2011 ACEEEDOI: 01.IJCSI.02.02. 1
- 2. ACEEE Int. J. on Control System and Instrumentation, Vol. 02, No. 02, June 2011 Or in non-dimensional form: Where TW is the integration constant of the hydropowerWhere the following notations were used: system and the variables have the following meaning:Which represent the non-dimensional variations of theparameters around the steady state values. It must be noted that this is a simplified method to compute the hydraulic pressure loss, which can be used for run-of-theB. The hydraulic feed system river hydropower plants, with small water head. If an exact The hydraulic feed system has a complex geometrical value of the dynamic pressure is required, then the formulasconfiguration, consisting of pipes or canals with different presented in [8], sub-chapter 8.4 “The calculation of hydroshapes and cross-sections. Therefore, the feed system will energy potential” shall be used.be considered as a pipe with a constant cross-section and Using the Laplace transform in relation (11), it results:the length equal with real length of the studied system. Inorder to consider this, it is necessary that the real system andthe equivalent system to contain the same water mass. Let Replacing (13) in (3) and (4) and doing some simpleconsider m1, m2...mn the water masses in the pipe zones having calculations, we obtain:the lengths l1,l2,...,ln and cross-sections A1, A2,...,An of the realfeed system. The equivalent system will have the lengthL=l1+l2+...+ln and cross-section A, conveniently chosen.In this case, the mass conservation law in both systems willlead to the equation:Since the water can be considered incompressible, the flowQi through each pipe segment with cross-section A i is The mechanical power generated by the turbine can beidentical and equal with the flow Q through the equivalent calculated with the relation P= g.Q.H, which can be used topipe obtain the linearized relations for variations of these values around the steady state values:Where v is the water speed in the equivalent pipe, and vi isthe speed in each segment of the real pipe. Where ? is the turbine efficiency, and g, Q, and H wereFrom the mass conservation law it results: defined previously. On the other hand, the mechanical power can be determined using the relation P=Mù=2 M.N, which can be used to obtainThe dynamic pressure loss can be computed considering the the linearized relations for variations of these values aroundinertia force of the water exerted on the cross-section of the the steady state values:pipe: Where = is the steady state power generated by the turbine for a given steady state flow Q0 and a steadyWhere L is the length of the penstock or the feed canal, A is state head H0, and N0 is the steady state rotational speed.the cross-section of the penstock, g? is the specific gravity Using these relations, the block diagram of the hydraulicof water (1000Kgf/m3), a is the water acceleration in the turbine, for small variation operation around the steady stateequivalent pipe, and g=9.81 m/s 2 is the gravitational point, can be determined and is presented in Figure 2, whereacceleration. The dynamic pressure loss can be expressed the transfer functions for different modules are given by theas: following relation:Using non-dimensional variations, from (9) it results: 56© 2011 ACEEEDOI: 01.IJCSI.02.02.1
- 3. ACEEE Int. J. on Control System and Instrumentation, Vol. 02, No. 02, June 2011For an ideal turbine, without losses, the coefficients a ij TABLE I. VARIATIONS OF THE TIME CONSTANT OF THE HYDRO SYSTEMresulted from the partial derivatives in equations (12 - 16)have the following values: a11=0.5; a12=a13=1; a21=1.5; a23=1.In this case, the transfer functions in the block diagram aregiven by the following relation: the reservoir, for a constant water flow, Q=725m3/s. III. SIMULATION RESULTS Example. Let consider a hydroelectric power system withthe following parameters:-Water flow (turbines): QN=725 m3/s;-Water level in the reservoir: HN=30 m;-The equivalent cross-section of the penstock A=60m2;-Nominal power of the turbine PN=178MW;-Turbine efficiency =0.94;-Nominal rotational speed of the turbine=N=71.43 rot/min;-The length of the penstock l= li=20m; Fig. 2. The block diagram of the hydraulic turbine.It shall be determined the variation of the time constant TW Figure 3. Variation of the integral time constant TW: a) by thefor the hydro power system. flow Q, b) by the water level HFor the nominal regime, using relation (12), where li=20m, It can be seen from the table or from the graphs that thethe time constant of the system is: time constant changes more than 50% for the entire operational range of the water flow through the turbine or if the water level in the reservoir varies. These variations will Next there is a study of the variation of the time constant create huge problems during the design of the control systemdue to the variation of the water flow through the turbine for for the turbine, and robust control algorithms area constant water level in the reservoir, H=30m, as well as the recommended.variation due to the variable water level in the reservoir for a In figure 4 the block diagram of the turbine’s power con-constant flow Q=725 m3/s. In table I, column 3 and figure 3 a) trol system, is presented using a secondary feedback fromare presented the values and the graphical variation of the the rotational speed of the turbine. It can be seen from thistime constant TW for the variation of the water flow between figure that a dead-zone element was inserted in series with500 m3/s and 110 m3/s, for a constant water level in the the rotational speed sensor in order to eliminate the feedbackreservoir, H=30m. In table 1. column 4 and figure 3 b) are for ±0.5% variation of the rotational speed around the syn-presented the values and the graphical variation of the time chronous value. This oscillation has no significant influenceconstant TW for the variation of the water level in on the performance of the system but would have lead to 57© 2011 ACEEEDOI: 01.IJCSI.02.02.1
- 4. ACEEE Int. J. on Control System and Instrumentation, Vol. 02, No. 02, June 2011permanent perturbation of the command sent to the turbine In figure 6 the variations of the turbine power (graph a) andgate. rotational speed (graph b) for the control system a feedback from the turbine power but no feedback from the rotational speed are presented. Figure 4. Block Diagram of the control system for hydraulic turbines The constants of the transfer functions had beencomputed for a nominal regime T W =0.8s. The optimalparameters for a PI controller are: KR=10, TI=0.02s. The resultsof the turbine simulation for different operational regimes arepresented in figure 5, for a control system using feedbacksfrom the turbine power and rotational speed, with a dead-zone on the rotational speed channel for ±0.5% variation ofthe rotational speed around the synchronous value (a) Powervariation with 10% around nominal value, b) Rotational speedvariation for power control). Figure 6 Control structure with only power feedback a) Power variation with 10% around nominal value b) Rotational speed variation for power control IV. CONCLUSIONS The detailed mathematical modeling of hydraulic turbine is vital to capture essential system dynamic behavior .The possibility of implementation of digital systems for monitoring and control for power, frequency and voltage in the cascade hydro power plant was discussed. The simplified mathematical models, capable to accurately describe dynamic and stationary behavior of the hydro units a developed and simulated. These aspects are compared with experimental results. Finally, a practical example was used to illustrate the design of controller and to study the system stability. ACKNOWLEDGEMENT The authors would like to thank Professor S.P. Singh (I.I.T Roorkee, India) for his continuous support and valuable suggestions. Figure 5 Control structure with feedbacks from turbine power and rotational speed: 58© 2011 ACEEEDOI: 01.IJCSI.02.02.1
- 5. ACEEE Int. J. on Control System and Instrumentation, Vol. 02, No. 02, June 2011 REFERENCES [6] Asal H. P., R. Widmer, H. Weber, E. Welfonder, W. Sattinger. Simulation of the restoration process after black Out in the Swiss[1] P. Kundur. Power System Stability and Control. McGraw- grid. Bulletin SEV/VSE 83, 22, 1992, pp. 27-34.Hill, 1994. [7] Weber, H., F. Prillwitz, M. Hladky, H. P. Asal. Reality oriented[2] IEEE. Hydraulic turbine and turbine control models for system simulation models of power plants for restoration studies. Controldynamic studies. IEEE Transactions on Power Systems, 7(1):167– Engineering practice, 9, 2001, pp. 805-811.179, Feb 1992. [8] Weber, H., V. Fustik, F. Prillwitz, A. Iliev. Practically oriented[3] Jiang, J. Design an optimal robust governor for hydraulic turbine simulation model for the Hydro Power Plant “Vrutok” in Macedonia.generating units IEEE Transaction on EC 1, Vol.10, 1995, pp.188- 2nd Balkan Power Conference, 19.-21.06. 2002, Belgrade,194. Yugoslavia[4] IEEE Working Group. Hydraulic turbine and turbine control [9] C. Henderson, Yue Yang Power Station – The Implementation ofmodels for system dynamic studies. IEEE Transactions on Power the Distributed Control System, GEC Alsthom Technical Review,Syst 1992; 7:167–79. Nr. 10, 1992.[5] Nand Kishor, R.P. Saini, S.P. Singh A review on hydropower [10] Prillwitz F., A. Holst, H. W. Weber (2004), “Reality Orientedplant models and control, Renewable and Sustainable Energy Simulation Models of the Hydropower Plants in Macedonia andReviews 11 (2007) 776–796 Serbia/Montenegro” In Proceedings of the Annual Scientific Session TU Verna, Bulgaria. 59© 2011 ACEEEDOI: 01.IJCSI.02.02.1

No public clipboards found for this slide

Be the first to comment