Case study - The Capital - STP exhaust air AHU ozonation
The Capital (Wadhwa Group)– BKC (mumbai)
1. Site Data
2. Present Scenario
4. Offered Solution & Technology
5. General Arrangement Layout & site pictures
8. Operation & Maintenance
9. Consumables & Replacements
10. Ref.-Ozone Chemistry
Site Data :
STP Capacity : 350 KLD
STP Area & Height : 300 m² x 6.0 m
AHU – Air flow : 19,000 cfm (32,200 m3/hr)
Air Flow : Intermittent [Automatic]
AHU Duct Size & Length : 600 x 600 mm x 20 m
Air Changes per Hour : 18 - 20 nos.
Present Scenario :
Sewage Collection Tank & STP Room:
Raw sewage is entering the raw sewage collection tank & being
treated by sewage treatment plant. Since STP is in basement area,
appropriate ventilation is provided. Where fresh air is fed from
ground level & exhaust air is being exhausted in car park area.
1. Prevent foul sewage odor to spread in car park area & subsequently
to surrounding receiving atmosphere.
2. Destroy odor causing gases coming from STP room.
Offered Solution & Technology :
AHU duct air ozonation.
Ozone is a very strong oxidizing agent.
All foul odor generated from sewage are organic in nature, and can very
easily be oxidized (destroyed) by ozone.
After oxidation by products does not cause objectionable odor & are
safe to dispose in surrounding air.
Crucial part of the solution is to trap the foul odor & efficiently mix
with ozone gas to oxidize.
Safety First :
Most Important :
If required Air ozone sensors &
monitors are available.
Ozone sensors can be interlocked
with ozone production & controlled
System can be pre-set for ozone level
Operation & Maintenance :
Ozonator is fully electrical operated.
Ozonator should be operated 24 x 7
For flawless operation three ozonators are operated alternately.
(2 w +1S)
Routine maintenance frequency is once in months
Break-down repair/maintenance will be attained in 48 hrs.
(Under this situation, there is a provision of one standby unit)
Consumables & replacements :
Consumables : Electricity Power - 2,000 watts
Electrical consumption : 2.0 kw x 24 hrs = 48 kw-hr
= 48 units/day x 10/- (rate per unit)
= 480 /- per day
Ozone cell : 2 – 2 ½ yrs : Rs. 20,000/=
Molecular sieves : 1 ½ - 2 yrs : Rs. 15,000/=
STP Odor & Ozone Chemistry :
In an aqueous solution, however, two competing simultaneous reactions occur, one to produce
elemental sulfur, and one to produce sulfuric acid:
H2S + O3 → S + O2 + H2O
3 H2S + 4 O3 → 3 H2SO4
Ozone also oxidizes nitric oxide to nitrogen dioxide:
NO + O3 → NO2 + O2
This reaction is accompanied by chemiluminescence. The NO2 can be further oxidized:
NO2 + O3 → NO3 + O2
Ozone does not react with ammonium salts, but it oxidizes ammonia to ammonium nitrate:
2 NH3 + 4 O3 → NH4NO3 + 4 O2 + H2O
Ozone reacts with carbon to form carbon dioxide, even at room temperature:
C + 2 O3 → CO2 + 2 O2
Ozone reacts with methane to form carbon dioxide, even at room temperature:
3 CH4 + 4 O3 → 3 CO2 + 6 H2O
Thanks For your Precious time
For more Information :
Visit : [www.chemtronicsindia.com ; www.ozonegeneratorindia.com]
Call : Mr. Sunil Shah - +91-9321234527