Upcoming SlideShare
×

# KNX - Exercitii practice 4

838 views

Published on

KNX - Exercitii practice

Published in: Technology
0 Likes
Statistics
Notes
• Full Name
Comment goes here.

Are you sure you want to Yes No
Your message goes here
• Be the first to comment

• Be the first to like this

Views
Total views
838
On SlideShare
0
From Embeds
0
Number of Embeds
13
Actions
Shares
0
49
0
Likes
0
Embeds 0
No embeds

No notes for slide

### KNX - Exercitii practice 4

1. 1. Home and Building Management Systems
2. 2. Exercitii practice – Curs KNX Basic EXERCITIUL PRACTIC NR.4 -Line coupler -Export proiect -Generare rapoarteHome and Building Management Systems
3. 3. Exercitii practice – Curs KNX BasicEXERCITIUL PRACTIC NR.4 Exercitiul practic nr.4 are ca punct de plecare proiectul realizat in cadrul exercitiului nr.3 Se va deschide proiectul rezultat in exercitiul nr.3 in care se vor opera urmatoarele adaugiri/modificari: Se pleaca de la ipoteza ca modulul de intrari binare pentru alarma de efractie si alarma senzorului de vant, este localizat undeva in cladire conectat pe Main Line-ul 1.0. Se va reconfigura proiectul astfel incat telegramele de la acesta sa poata ajunge in continuare la echipamentele cu obiecte de comunicatie in adresele de grup vizate. Inserarea unui nou device in proiect in locatia “Tablou” (Line Coupler)Home and Building Management Systems
4. 4. Exercitii practice – Curs KNX BasicEXERCITIUL PRACTIC NR.4 Alocarea unitatii Line Coupler inserata in fereastra Building la linia noastra 1.1Home and Building Management Systems
5. 5. Exercitii practice – Curs KNX BasicEXERCITIUL PRACTIC NR.4 Alocarea unitatii Line Coupler inserata in fereastra Building la linia noastra 1.1 Main Line 1.0 PS / Ch LC 1 DVC1 PS / Ch DVC1 Gira 1023 00 Line Couplere Ling&Janke TS2 Modul intrari binare Adresa 1.1.0 Adresa 1.0.6 Linia 1 DVC x LC = Line coupler DVC = Echipament de bus PS/Ch = Power supply cu chokeHome and Building Management Systems
6. 6. Exercitii practice – Curs KNX BasicEXERCITIUL PRACTIC NR.4 Mutarea device-ului Lingg&Janke wall switch interface 2fold din linia 1.1. in Main Line 1.0. (drag&drop) Nota: Dupa aceasta operatiune legaturile obiectelor de comunicatie cu adresele de grup se vor pastra , in plus EST va creea automat tabelul de filtrare (Filter Table) al Line Coupler-ului.Home and Building Management Systems
7. 7. Exercitii practice – Curs KNX BasicEXERCITIUL PRACTIC NR.4 Topologia proiectului Observatie: Conectarea fizica a echipamentului Lingg&Janke TS2 pe Main Line se face schimband pozitia cuplei de pe training kit Conectare TS2 Conectare TS2 pe linia 1.1. pe Main Line 1.0.Home and Building Management Systems
8. 8. Exercitii practice – Curs KNX BasicEXERCITIUL PRACTIC NR.4 Vizualizarea tabelului de filtrareHome and Building Management Systems
9. 9. Exercitii practice – Curs KNX BasicEXERCITIUL PRACTIC NR.4 Salvarea proiectului intr-un fisier export cu extensia .knxproj (specific ETS4)Home and Building Management Systems
10. 10. Exercitii practice – Curs KNX BasicEXERCITIUL PRACTIC NR.4 Salvarea proiectului intr-un fisier export cu extensia .knxproj (specific ETS4)Home and Building Management Systems
11. 11. Exercitii practice – Curs KNX BasicEXERCITIUL PRACTIC NR.4 Generare rapoarteHome and Building Management Systems
12. 12. Exercitii practice – Curs KNX BasicEXERCITIUL PRACTIC NR.4 Generare rapoarteHome and Building Management Systems