Successfully reported this slideshow.
Upcoming SlideShare
×

# Ct & vt

2,423 views

Published on

power system proection

Published in: Engineering
• Full Name
Comment goes here.

Are you sure you want to Yes No
• Be the first to comment

### Ct & vt

1. 1. ۱۳۷ Ch 5 : Voltage & Current  Transformers  Eng / Alaa Mohammed Hammadi Hammadi
2. 2. ۱۳۸ ‫؟‬ ‫ﻭﺍﻟﺘﻴﺎﺭ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﻣﻦ‬ ‫ﺍﻟﻐﺮﺽ‬ ‫ﻣﺎ‬ ۱­‫ﻗﻴﻢ‬ ‫ﺇﻟﻰ‬ ‫ﻭﺍﻟﺘﻴﺎﺭ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻗﻴﻤﺔ‬ ‫ﺗﺨﻔﻴﺾ‬‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺃﻭ‬ ‫ﺱ‬ ‫ﺍﻟﻘﻴﺎ‬ ‫ﺑﺄﺟﻬﺰﺓ‬ ‫ﻗﻴﺎﺳﻬﺎ‬ ‫ﻳﻤﻜﻦ‬ ‫ﻣﻨﺎﺳﺒﻪ‬. ۲­‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﺠﺎﻧﺐ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻤﻮﺟﻮﺩﻩ‬ ‫ﺍﻟﺪﻭﺍﺋﺮ‬ ‫ﻋﺰﻝ‬)‫ﻗﻴﺎﺱ‬ ‫ﺃﺟﻬﺰﺓ‬/‫ﻭﻗﺎﻳﻪ‬(‫ﺍﻟﻌﺎﻟﻴﻪ‬ ‫ﻭﺍﻟﺘﻴﺎﺭﺍﺕ‬ ‫ﺍﻟﺠﻬﻮﺩ‬ ‫ﺫﻯ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﺠﺎﻧﺐ‬ ‫ﻋﻦ‬. ۳­‫ﻟﻠﺠﻬﺪ‬ ‫ﻗﻴﺎﺳﻴﻪ‬ ‫ﻗﻴﻢ‬ ‫ﺇﺳﺘﺨﺪﺍﻡ‬/‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﺠﺎﻧﺐ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻤﻮﺟﻮﺩﻩ‬ ‫ﻟﻸﺟﻬﺰﻩ‬ ‫ﻟﻠﺘﻴﺎﺭ‬. ‫ﺍﻟﺠﻬ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﻭﻇﻴﻔﺔ‬ ‫ﻣﺎ‬‫؟‬ ‫ﺃﻧﻮﺍﻋﻬﺎ‬ ‫ﻭﻣﺎ‬ ‫ﺪ‬ ‫ﺇﻟﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺑﺘﺨﻔﻴﺾ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺗﻘﻮﻡ‬100‫ﺃﻭ‬ ‫ﻓﻮﻟﺖ‬110‫ﻣﺜﻞ‬ ‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﻟﺘﻐﺬﻳﺔ‬ ‫ﻓﻮﻟﺖ‬KVARh , KV , KW , KWh‫ﻣﺜﻞ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﺑﺘﻐﺬﻳﺔ‬ ‫ﺃﻳﻀﺎ‬ ‫ﺗﻘﻮﻡ‬ ‫ﻛﻤﺎ‬‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺗﻐﺬﻯ‬ ‫ﻭﻛﺬﻟﻚ‬ ‫ﻣﺜﻞ‬ ‫ﺍﻟﺘﺤﻜﻢ‬ ‫ﺃﻧﻈﻤﺔ‬:Load shedding Intrlock ‫ﻣﺤﻮﻻﺕ‬ ‫ﻋﻦ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺗﺨﺘﻠﻒ‬‫ﺍﻝ‬ ‫ﻗﻴﻤﺔ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻘﺪﺭﻩ‬rated power‫ﺗﻤﺮ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺍﻟﻘﺪﺭﻩ‬ ‫ﺗﺘﻌﺪﻯ‬ ‫ﻻ‬ ‫ﻗﺪ‬ ‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﻓﻤﺤﻮﻻﺕ‬ ‫ﻣﻨﻬﻤﺎ‬ ‫ﻟﻜﻞ‬ ‫ﻣﻦ‬ ‫ﻋﺸﺮﺍﺕ‬ ‫ﻋﺪﺓ‬ ‫ﺧﻼﻟﻬﺎ‬VA‫ﻋﻦ‬ ‫ﻣﺎﻳﺰﻳﺪ‬ ‫ﺇﻟﻰ‬ ‫ﺍﻟﻘﺪﺭﻩ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺧﻼﻝ‬ ‫ﺍﻟﻤﺎﺭﻩ‬ ‫ﺍﻟﻘﺪﺭﻩ‬ ‫ﺗﺼﻞ‬ ‫ﺑﻴﻨﻤﺎ‬300 MVA‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺃﻥ‬ ‫ﻛﻤﺎ‬ ‫ﺃﺳﺎﺳ‬ ‫ﺑﺸﻜﻞ‬ ‫ﺗﺒﺮﻳﺪ‬ ‫ﺇﻟﻰ‬ ‫ﺗﺤﺘﺎﺝ‬ ‫ﺍﻟﻘﻮﻯ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺑﻴﻨﻤﺎ‬ ‫ﺗﺒﻴﺮﻳﺪ‬ ‫ﺇﻟﻰ‬ ‫ﻻﺗﺤﺘﺎﺝ‬‫ﻋﺎﻟﻴﻪ‬ ‫ﺧﻼﻟﻬﺎ‬ ‫ﺍﻟﻤﺎﺭﻩ‬ ‫ﺍﻟﻘﺪﺭﻩ‬ ‫ﻷﻥ‬ ‫ﻰ‬. ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﺠﺎﻧﺐ‬ ‫ﻓﻰ‬ ‫ﺟﻬﺪﺍ‬ ‫ﺗﻨﺘﺞ‬ ‫ﺃﻥ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺃﻭ‬ ‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻤﺴﺘﺨﺪﻣﻪ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﻣﻦ‬ ‫ﻣﻄﻠﻮﺏ‬ ‫ﺃﻧﻪ‬ ‫ﻫﻰ‬ ‫ﻫﺎﻣﻪ‬ ‫ﻣﻠﺤﻮﻇﻪ‬ ‫ﻭﻫﻨﺎﻙ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺟﻬﺪ‬ ‫ﺍﻟﻤﺴﺘﻄﺎﻉ‬ ‫ﻗﺪﺭ‬ ‫ﻳﻤﺎﺛﻞ‬)‫ﺍﻝ‬ ‫ﻗﻴﻤﺔ‬ ‫ﺍﻹﻋﺘﺒﺎﺭ‬ ‫ﻓﻰ‬ ‫ﺍﻷﺧﺬ‬ ‫ﻣﻊ‬turns ratio(٬‫ﺍﻝ‬ ‫ﻳﻜﻮﻥ‬ ‫ﺃﻥ‬ ‫ﻳﺘﻄﻠﺐ‬ ‫ﻭﻫﺬﺍ‬voltage drop ‫ﺍﻝ‬ ‫ﺧﻼﻝ‬VT‫ﺍﻟﺘﺸﺒﻊ‬ ‫ﺣﺪﻭﺩ‬ ‫ﻋﻦ‬ ‫ﺍﻹﻣﻜﺎﻥ‬ ‫ﻗﺪﺭ‬ ‫ﺑﻌﻴﺪﻩ‬ ‫ﻭﺍﻟﻘﻴﺎﺱ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﻟﻤﺤﻮﻻﺕ‬ ‫ﺍﻟﺘﺸﻐﻴﻞ‬ ‫ﻧﻘﻄﺔ‬ ‫ﺗﻜﻮﻥ‬ ‫ﺃﻥ‬ ‫ﻳﺠﺐ‬ ‫ﻛﻤﺎ‬ ‫ﻳﻤﻜﻦ‬ ‫ﻣﺎ‬ ‫ﺃﻗﻞ‬ saturation‫ﺍﻟﺤﺪﻳﺪﻯ‬ ‫ﻟﻠﻘﻠﺐ‬. ‫ﻫﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺃﻧﻮﺍﻉ‬:۱­Potential Transformer ۲­Capacitive Voltage Transformer ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺗﺮﻛﻴﺐ‬ ‫ﻋﻦ‬ ‫ﺗﻜﻠﻢ‬VT‫؟‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻳﺘﻜﻮﻥ‬VT‫ﻣﻦ‬: ۱­‫ﻣﻘﻔﻠﻪ‬ ‫ﻣﻐﻨﺎﻃﻴﺴﻴﻪ‬ ‫ﺩﺍﺋﺮﻩ‬٬‫ﺍﻟﺴﻠﻴﻜﻮﻧﻰ‬ ‫ﺍﻟﺤﺪﻳﺪ‬ ‫ﻣﻦ‬ ‫ﺷﺮﺍﺋﺢ‬ ‫ﻣﻦ‬ ‫ﺗﺘﻜﻮﻥ‬. ۲­‫ﺇﺑﺘﺪﺍﺋﻰ‬ ‫ﻣﻠﻒ‬Primary winding‫ﻣﺤﻮﻝ‬ ‫ﺗﺮﻛﻴﺐ‬ ‫ﺍﻟﻤﺮﺍﺩ‬ ‫ﺍﻟﺪﺍﺋﺮﻩ‬ ‫ﻣﻊ‬ ‫ﺍﻟﺘﻮﺍﺯﻯ‬ ‫ﻋﻠﻰ‬ ‫ﻭﻳﻮﺻﻞ‬ ‫ﺍﻟﻤﻠﻔﺎﺕ‬ ‫ﻣﻦ‬ ‫ﻛﺒﻴﺮ‬ ‫ﻋﺪﺩ‬ ‫ﻋﻠﻰ‬ ‫ﻳﺤﺘﻮﻯ‬ ‫ﻋﻠﻴﻬﺎ‬ ‫ﺍﻟﺠﻬﺪ‬. ۳­‫ﺛﺎﻧﻮﻯ‬ ‫ﻣﻠﻒ‬Secondary Widing‫ﻗﻠﻴ‬ ‫ﻋﺪﺩ‬ ‫ﻋﻠﻰ‬ ‫ﻳﺤﺘﻮﻯ‬‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺑﻤﻠﻔﺎﺕ‬ ‫ﺍﻟﺘﻮﺍﺯﻯ‬ ‫ﻋﻠﻰ‬ ‫ﻭﻳﻮﺻﻞ‬ ‫ﺍﻟﻤﻠﻔﺎﺕ‬ ‫ﻣﻦ‬ ‫ﻞ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺃﻭ‬. ‫ﻋﺰﻝ‬ ‫ﺑﻤﺎﺩﺓ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻋﻦ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻋﺰﻝ‬ ‫ﻳﺘﻢ‬Insulation‫ﺍﻟﻌﺰﻝ‬ ‫ﺯﺍﺩ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺯﺍﺩ‬ ‫ﻓﻜﻠﻤﺎ‬ ‫ﺍﻟﺘﺸﻐﻴﻞ‬ ‫ﺟﻬﺪ‬ ‫ﻋﻠﻰ‬ ‫ﺗﻌﺘﻤﺪ‬ ‫؟‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺇﺧﺘﻴﺎﺭ‬ ‫ﻋﻠﻴﻬﺎ‬ ‫ﺑﻨﺎءﺍ‬ ‫ﻳﺘﻢ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺍﻟﻤﻮﺍﺻﻔﺎﺕ‬ ‫ﻫﻰ‬ ‫ﻣﺎ‬ ‫ﻭﻫﻰ‬ ‫ﺍﻟﻤﻨﺎﺳﺐ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺇﺧﺘﻴﺎﺭ‬ ‫ﻗﺒﻞ‬ ‫ﻣﻨﻬﺎ‬ ‫ﺑﺪ‬ ‫ﻻ‬ ‫ﻣﻮﺍﺻﻔﺎﺕ‬ ‫ﻋﺪﺓ‬ ‫ﻫﻨﺎﻙ‬: ۱­Rated voltage:‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﺠﺎﻧﺐ‬ ‫ﺟﻬﺪ‬ ‫ﺑﻪ‬ ‫ﻭﻳﻘﺼﺪ‬٬‫ﺍﻟﻤﺜﺎﻝ‬ ‫ﺳﺒﻴﻞ‬ ‫ﻋﻠﻰ‬12 KV ۲­Level Voltage:‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﺠﺎﻧﺐ‬ ‫ﺟﻬﺪ‬ ‫ﺑﻪ‬ ‫ﻭﻳﻘﺼﺪ‬٬‫ﺍﻟﻤﺜﺎﻝ‬ ‫ﺳﺒﻴﻞ‬ ‫ﻋﻠﻰ‬12 – 28 – 75 – 100 – 110 KV ۳­Breakdown – pulse Voltage:‫ﺩﺍﺋﻤﻪ‬ ‫ﺑﺼﻮﺭﻩ‬ ‫ﻭﻟﻴﺲ‬ ‫ﻭﻟﺤﻈﻴﻪ‬ ‫ﻣﺆﻗﺘﻪ‬ ‫ﺑﺼﻮﺭﻩ‬ ‫ﺍﻟﻤﺤﻮﻝ‬ ‫ﻳﺘﺤﻤﻠﻌﺎ‬ ‫ﻗﻴﻤﻪ‬ ‫ﺃﻗﺼﻰ‬ ‫ﻭﻫﻰ‬٬‫ﻭﻏﺎﻟﺒﺎ‬ ‫ﺍﻷﻋﻄﺎﻝ‬ ‫ﻟﺤﻈﺎﺕ‬ ‫ﻋﻨﺪ‬ ‫ﺗﻜﻮﻥ‬ ‫ﻣﺎ‬. ٤­Turn Ratio‫ﺍﻟﺘﺤﻮﻳﻞ‬ ‫ﻧﺴﺒﺔ‬ ‫ﻭﻫﻰ‬. ٥­Accuracy Class:‫ﻭﺍﻟﺰﺍﻭﻳﻪ‬ ‫ﺍﻟﻤﻘﺪﺍﺭ‬ ‫ﺣﻴﺚ‬ ‫ﻣﻦ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻗﺮﺍءﻯ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺨﻄﺄ‬ ‫ﻧﺴﺒﺔ‬ ‫ﺗﻮﺻﻒ‬ ‫ﻷﻧﻬﺎ‬ ‫ﺍﻟﻤﻮﺍﺻﻔﺎﺕ‬ ‫ﺃﻫﻢ‬ ‫ﻣﻦ‬ ‫ﻭﻫﺬﻩ‬. ‫ﺗﺤﺪ‬ ‫ﻭﺑﺎﻟﺘﺎﻟﻰ‬‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﺩﻭﺍﺋﺮ‬ ‫ﻳﻨﺎﺳﺐ‬ ‫ﺃﻡ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﻣﻊ‬ ‫ﺍﻹﺳﺘﺨﺪﺍﻡ‬ ‫ﻳﻨﺎﺳﺐ‬ ‫ﺍﻟﻨﻮﻉ‬ ‫ﻫﺬﺍ‬ ‫ﻫﻞ‬ ‫ﺩ‬.
3. 3. ۱۳۹ ‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻤﺴﺘﺨﺪﻣﻪ‬ ‫ﻟﻠﻤﺤﻮﻻﺕ‬ ‫ﺍﻟﺪﻗﻪ‬ ‫ﻟﺪﺭﺟﺔ‬ ‫ﺍﻟﻘﻴﺎﺳﻴﻪ‬ ‫ﺍﻟﻘﻴﻢ‬ ‫ﻭﺃﻫﻢ‬0.1‫ﻭ‬0.2‫ﻭ‬0.5‫ﻭ‬1.0‫ﻭ‬3.0‫ﺍﻟﺪﻗﻪ‬ ‫ﺩﺭﺟﺎﺕ‬ ‫ﺃﻣﺎ‬ ‫ﺣﺮﻑ‬ ‫ﺑﻮﺟﻮﺩ‬ ‫ﺗﺘﻤﻴﺰ‬ ‫ﻓﻬﻰ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﻣﻊ‬ ‫ﺍﻟﻤﺴﺘﺨﺪﻣﻪ‬ ‫ﻟﻠﻤﺤﻮﻻﺕ‬P‫ﻣﺜﻞ‬ ‫ﺍﻟﺮﻗﻢ‬ ‫ﺑﻌﺪ‬3P‫ﻭ‬5P‫ﻟﻞ‬ ‫ﻣﺨﺼﺼﻪ‬ ‫ﺃﻧﻬﺎ‬ ‫ﻋﻠﻰ‬ ‫ﻟﻠﺪﻻﻟﻪ‬ protection.‫ﺃﻋﻠﻰ‬ ‫ﺍﻟﻤﺘﻮﻗﻌﻪ‬ ‫ﺍﻟﺨﻄﺄ‬ ‫ﻧﺴﺒﺔ‬ ‫ﻛﺎﻧﺖ‬ ‫ﻛﻠﻤﺎ‬ ‫ﺍﻟﻘﻴﻤﻪ‬ ‫ﺇﺭﺗﻔﻌﺖ‬ ‫ﻛﻠﻤﺎ‬ ‫ﺃﻧﻪ‬ ‫ﻭﻳﻼﺣﻆ‬. ‫؟‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻟﻤﺤﻮﻻﺕ‬ ‫ﺑﺎﻟﻨﺴﺒﻪ‬ ‫ﺍﻟﺨﻄﺄ‬ ‫ﻧﺴﺒﺔ‬ ‫ﻋﺮﻑ‬ ‫؟‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﻃﺮﻕ‬ ‫ﻋﻦ‬ ‫ﺗﻜﻠﻢ‬ ‫ﻛﻞ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﻳﺘﻢ‬ ‫ﺣﻴﺚ‬ ‫ﻣﻨﻔﺼﻠﻪ‬ ‫ﺑﺼﻮﺭﻩ‬ ‫ﺍﻟﺜﻼﺛﻪ‬ ‫ﺍﻷﻭﺟﻪ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻟﻘﻴﺎﺱ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺗﻮﺻﻞ‬ ‫ﻋﺎﻣﻪ‬ ‫ﺑﺼﻔﻪ‬VT‫ﺑﻴﻦ‬Phase‫ﻭ‬ Neutral٬‫ﺑﻌﻀﻬﺎ‬ ‫ﻋﻦ‬ ‫ﻣﻨﻔﺼﻠﻪ‬ ‫ﺍﻟﺜﻼﺛﻪ‬ ‫ﺍﻷﻭﺟﻪ‬ ‫ﺟﻬﻮﺩ‬ ‫ﻗﻴﻤﺔ‬ ‫ﻳﺮﻯ‬ ‫ﺃﻥ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﻟﺠﻬﺎﺯ‬ ‫ﺗﺘﺎﺡ‬ ‫ﻭﺑﺎﻟﺘﺎﻟﻰ‬)VA , VB , VC(‫ﻭﺍﻟﺸﻜﻞ‬ 1­2‫ﺗﺮﻛﻴﺐ‬ ‫ﻳﻈﻬﺮ‬VT‫ﺍﻝ‬ ‫ﺃﺣﺪ‬ ‫ﻣﻊ‬Phases‫ﺍﻟﻨﻘﻞ‬ ‫ﺧﻄﻮﻁ‬ ‫ﻣﻦ‬ ‫ﻟﺨﻂ‬ ‫ﺍﻟﺜﻼﺛﻪ‬. ‫ﺍﻷﺣﻴﺎﻥ‬ ‫ﺑﻌﺾ‬ ‫ﻓﻰ‬ ‫ﺃﻧﻪ‬ ‫ﻏﻴﺮ‬ ‫ﺍﻝ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺠﻬﻮﺩ‬ ‫ﻣﺠﻤﻮﻉ‬ ‫ﻟﻘﻴﺎﺱ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺗﺴﺘﺨﺪﻡ‬Phases‫ﻋﻠﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻭﻟﻴﺲ‬ ‫ﺍﻟﺜﻼﺛﻪ‬phase ‫ﺍﻟﺸﻜﻞ‬ ‫ﻓﻰ‬ ‫ﻛﻤﺎ‬ ‫ﻣﺤﺪﺩ‬2­2٬‫ﺑـ‬ ‫ﻫﺬﻩ‬ ‫ﺍﻟﺘﻮﺻﻴﻞ‬ ‫ﻃﺮﻳﻘﺔ‬ ‫ﻭﺗﺴﻤﻰ‬Resdual Connection٬‫ﺍﻟﻐﺒﺮ‬ ‫ﺍﻷﻋﻄﺎﻝ‬ ‫ﺇﻛﺘﺸﺎﻑ‬ ‫ﻓﻰ‬ ‫ﻣﻔﻴﺪﻩ‬ ‫ﻭﻫﻰ‬ ‫ﻣﺘﻤﺎﺛﻠﻪ‬Unsymmetrical Faults٬‫ﺍﻟـ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺠﻬﻮﺩ‬ ‫ﻣﺠﻤﻮﻉ‬ ‫ﻳﻜﻮﻥ‬ ‫ﺣﻴﺚ‬Three Phases‫ﺻﻔﺮﺍ‬ ‫ﻳﺴﺎﻭﻯ‬ ‫ﻻ‬ ‫ﺍﻟﻌﻄﻞ‬ ‫ﺣﺎﻟﺔ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻄﺒﻴﻌﻴﻪ‬ ‫ﺍﻟﻈﺮﻭﻑ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺤﺎﻝ‬ ‫ﻫﻮ‬ ‫ﻛﻤﺎ‬٬‫ﻣﻦ‬ ‫ﻧﻮﻉ‬ ‫ﻭﺟﻮﺩ‬ ‫ﻳﺆﻛﺪ‬ ‫ﺫﻟﻚ‬ ‫ﻓﺈﻥ‬ ‫ﺍﻟﺘﻮﺻﻴﻠﻪ‬ ‫ﻫﺬﻩ‬ ‫ﺃﻃﺮﺍﻑ‬ ‫ﻋﻠﻰ‬ ‫ﺟﻬﺪ‬ ‫ﺃﻯ‬ ‫ﻇﻬﻮﺭ‬ ‫ﻓﺒﻤﺠﺮﺩ‬ ‫ﺛﻢ‬ ‫ﻭﻣﻦ‬ ‫ﺍﻟـ‬ ‫ﺃﻧﻮﺍﻉ‬Unsymmetrical Faults.   ‫ﻻ‬ ‫ﺍﻟﺘﻮﺻﻴﻠﻪ‬ ‫ﻫﺬﻩ‬ ‫ﺃﻥ‬ ‫ﻻﺣﻆ‬‫ﺣﺎﻟﺔ‬ ‫ﻓﻰ‬ ‫ﺗﻔﻴﺪ‬Symmetrical Faults٬‫ﻣﺘﻤﺎﺛﻠﻪ‬ ‫ﻛﻠﻬﺎ‬ ‫ﺍﻟﺠﻬﻮﺩ‬ ‫ﻷﻥ‬٬‫ﻳﺴﺎﻭﻯ‬ ‫ﺍﻹﺗﺠﺎﻫﻰ‬ ‫ﻭﻣﺠﻤﻮﻋﻬﺎ‬ ‫ﺻﻔﺮ‬٬‫ﺍﻟﻄﺒﻴﻌﻲ‬ ‫ﺍﻟﻮﺿﻊ‬ ‫ﻋﻦ‬ ‫ﺍﻟﻌﻄﻞ‬ ‫ﺗﻤﻴﻴﺰ‬ ‫ﻳﻤﻜﻦ‬ ‫ﻻ‬ ‫ﻭﺑﺎﻟﺘﺎﻟﻰ‬٬‫ﻳﺴﻤﻰ‬ ‫ﺍﻟﺘﻮﺻﻴﻠﻪ‬ ‫ﻫﺬﻩ‬ ‫ﺃﻃﺮﺍﻑ‬ ‫ﻋﻠﻰ‬ ‫ﻳﻈﻬﺮ‬ ‫ﺍﻟﺬﻯ‬ ‫ﻭﺍﻟﺠﻬﺪ‬Residual Voltage٬‫ﻳﺴﻤﻰ‬ ‫ﻣﺎ‬ ‫ﻗﻴﺎﺱ‬ ‫ﻓﻰ‬ ‫ﺃﻳﻀﺎ‬ ‫ﺗﻔﻴﺪ‬ ‫ﺍﻟﺘﻮﺻﻴﻠﻪ‬ ‫ﻭﻫﺬﻩ‬Zero Sequence Voltage٬‫ﺃﻥ‬ ‫ﺍﻟﻤﻌﻠﻮﻡ‬ ‫ﻣﻦ‬ ‫ﺃﻧﻪ‬ ‫ﺣﻴﺚ‬ Vresidual‫ﺃﻣﺜﺎﻝ‬ ‫ﺛﻼﺛﺔ‬ ‫ﻳﺴﺎﻭﻯ‬Zero Sequence Voltage‫ﺍﻟﺜﻼﺛﻪ‬ ‫ﺍﻟﺠﻬﻮﺩ‬ ‫ﻣﺠﻤﻮﻉ‬ ‫ﻳﺴﺎﻭﻯ‬ ‫ﺍﻟﺬﻯ‬. ‫ﺃﻳﻀﺎ‬ ‫ﺗﺴﻤﻰ‬ ‫ﺍﻟﺘﻮﺻﻴﻠﻪ‬ ‫ﻫﺬﻩ‬ ‫ﺃﻥ‬ ‫ﺇﻟﻰ‬ ‫ﻧﺸﻴﺮ‬ ‫ﻭﺃﺧﻴﺮﺍ‬Broken Delta.‫ﻧﻘﻄﻪ‬ ‫ﻓﻰ‬ ‫ﻣﻔﺘﻮﺣﻪ‬ ‫ﺩﻟﺘﺎ‬ ‫ﺗﺸﺒﻪ‬ ‫ﻓﻬﻰ‬ ‫ﺍﻟﺮﺳﻢ‬ ‫ﻣﻦ‬ ‫ﻭﺍﺿﺢ‬ ‫ﻭﺍﻟﺴﺒﺐ‬ .
4. 4. ۱٤۰ ‫ﻫﻮ‬ ‫ﻣﺎ‬oltage TransformerCapacitive V‫؟‬ ‫ﻳﺴﺘﺨﺪﻡ‬ ‫ﻭﻣﺘﻰ‬ ***‫ﺍﻟﺠﻬﺪ‬ ‫ﻗﻴﺎﺱ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻤﻜﺜﻔﺎﺕ‬ ‫ﺇﺳﺘﺨﺪﺍﻡ‬: ‫ﺟﺪﺍ‬ ‫ﻣﻜﻠﻒ‬ ‫ﺍﻟﻌﺎﺩﻳﻪ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺇﺳﺘﺨﺪﺍﻡ‬ ‫ﻳﺼﺒﺢ‬ ‫ﺍﻟﻌﺎﻟﻴﻪ‬ ‫ﺍﻟﺠﻬﻮﺩ‬ ‫ﺣﺎﻟﺔ‬ ‫ﻓﻰ‬٬‫ﻋﺎﻟﻴﺎ‬ ‫ﺳﻴﻜﻮﻥ‬ ‫ﺍﻟﻤﻄﻠﻮﺏ‬ ‫ﺍﻟﻌﺰﻝ‬ ‫ﻷﻥ‬.‫ﻫﺬﻩ‬ ‫ﻋﻠﻰ‬ ‫ﻭﻟﻠﺘﻐﻠﺐ‬ ‫ﺑـ‬ ‫ﻳﻌﺮﻑ‬ ‫ﻣﺎ‬ ‫ﺇﺳﺘﺨﺪﺍﻡ‬ ‫ﻳﺘﻢ‬ ‫ﺇﻗﺘﺼﺎﺩﻳﻪ‬ ‫ﺑﻄﺮﻳﻘﻪ‬ ‫ﺍﻟﻤﺸﻜﻠﻪ‬Capacitive Voltage Transformer‫ﺑﺎﻟﺮﻣﺰ‬ ‫ﻟﻪ‬ ‫ﻭﻳﺮﻣﺰ‬CVT‫ﻭﻳﺘﻢ‬ ‫ﺑﺎﻟﺸﻜﻞ‬ ‫ﻛﻤﺎ‬ ‫ﺗﻮﺻﻴﻠﻪ‬3­2‫ﺍﻟـ‬ ‫ﺃﺣﺪ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻗﺮﺍءﺓ‬ ‫ﻳﻤﺜﻞ‬ ‫ﺍﻟﺬﻯ‬phases٬‫ﺑـ‬ ‫ﻳﻌﺮﻑ‬ ‫ﻣﺎ‬ ‫ﺍﻟﻮﺍﻗﻊ‬ ‫ﻓﻰ‬ ‫ﺗﻤﺜﻞ‬ ‫ﺍﻟﻨﻮﻉ‬ ‫ﻫﺬﺍ‬ ‫ﻭﻓﻜﺮﺓ‬ Capacitor Divider٬‫ﺍﻟﻤﻜﺜﻔﺎﺕ‬ ‫ﻣﻦ‬ ‫ﻋﺪﺩ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﻌﺎﻟﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻳﺘﻮﺯﻉ‬ ‫ﺣﻴﺚ‬٬‫ﻣﻦ‬ ‫ﺍﻟﻤﻜﺜﻔﺎﺕ‬ ‫ﻫﺬﻩ‬ ‫ﺃﺣﺪ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻗﺮﺍءﺓ‬ ‫ﻭﻳﺘﻢ‬ ‫ﻧﺎ‬‫ﺑﻮﺍﺳﻄﺔ‬ ‫ﺍﻷﺭﺽ‬ ‫ﺣﻴﺔ‬VT‫ﺍﻟﻌﺎﺩﻯ‬٬‫ﺍﻷﺻﻠﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﻦ‬ ‫ﺻﻐﻴﺮﻩ‬ ‫ﻧﺴﺒﻪ‬ ‫ﻳﻤﺜﻞ‬ ‫ﺍﻵﻥ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺃﺻﺒﺢ‬ ‫ﺣﻴﺚ‬٬‫ﻧﺴﺒﺔ‬ ‫ﻧﻔﺲ‬ ‫ﻭﻫﻰ‬ ‫ﺍﻟﻤﻜﺜﻔﺎﺕ‬ ‫ﻣﺠﻤﻮﻋﺔ‬ ‫ﺳﻌﺔ‬ ‫ﺇﻟﻰ‬ ‫ﺍﻷﺧﻴﺮ‬ ‫ﺍﻟﻤﻜﺜﻒ‬ ‫ﺳﻌﺔ‬. ‫ﺍﻟـ‬ ‫ﻣﻦ‬ ‫ﺍﻟﻨﻮﻉ‬ ‫ﻫﺬﺍ‬ ‫ﻳﻌﻴﺐ‬CVT‫ﺍﻟـ‬ ‫ﻣﻦ‬ ‫ﺃﻛﺜﺮ‬ ‫ﺍﻟﻤﻮﺟﻪ‬ ‫ﺷﻜﻞ‬ ‫ﻓﻰ‬ ‫ﺗﺸﻮﻩ‬ ‫ﻭﺟﻮﺩ‬VT‫ﺍﻟﻌﺎﺩﻯ‬٬‫ﺍﻟﻤﻜﺜﻔﺎﺕ‬ ‫ﻭﺟﻮﺩ‬ ‫ﺑﺴﺒﺐ‬ ‫ﻣﺘﻮﻗﻊ‬ ‫ﺷﺊ‬ ‫ﻭﻫﻮ‬ ‫ﺍﻟﺪﺍﺋﺮﻩ‬ ‫ﻓﻰ‬٬‫ﺍﻟﻤﻮﺟﻪ‬ ‫ﺷﻜﻞ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺘﺸﻮﻫﺎﺕ‬ ‫ﻟﻌﻼﺝ‬ ‫ﻃﺮﻕ‬ ‫ﻋﺪﺓ‬ ‫ﻫﻨﺎﻙ‬ ‫ﻟﻜﻦ‬٬‫ﻋﺪﻳﺪﻩ‬ ‫ﻃﺮﻗﺎ‬ ‫ﺗﺴﺘﺨﺪﻡ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺍﻟﺮﻗﻤﻴﻪ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﻣﻊ‬ ‫ﺧﺎﺻﻪ‬ ‫ﺍﻟﻤﻜﺜﻔﺎﺕ‬ ‫ﺗﺄﺛﻴﺮ‬ ‫ﺑﺪﻭﻥ‬ ‫ﺍﻷﺻﻠﻰ‬ ‫ﺍﻟﻤﻮﺟﻪ‬ ‫ﺷﻜﻞ‬ ‫ﻹﺳﺘﺮﺟﺎﻉ‬. *********************************************************** ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﻭﻇﻴﻔﺔ‬ ‫ﻫﻰ‬ ‫ﻣﺎ‬current transformer‫؟‬ ‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﻳﻐﺬﻯ‬ ‫ﺃﻥ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻭﻇﻴﻔﺔ‬/‫ﺍﻟﺪﺍﺋﺮﻩ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻤﺎﺭ‬ ‫ﺍﻷﺻﻠﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﻊ‬ ‫ﻗﻴﻤﺘﻪ‬ ‫ﺗﺘﻨﺎﺳﺐ‬ ‫ﺻﻐﻴﺮ‬ ‫ﺑﺘﻴﺎﺭ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬٬‫ﻭﻳﻔﻀﻞ‬ ‫ﻣﻦ‬ ‫ﺃﻗﻞ‬ ‫ﺣﺪﻭﺩ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺜﺎﻧﻰ‬ ‫ﺍﻟﺠﺎﻧﺐ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻗﻴﻤﺔ‬ ‫ﺗﻜﻮﻥ‬ ‫ﺃﻥ‬ ‫ﺩﺍﺋﻤﺎ‬5‫ﺍﻟﻄﺒﻴﻌﻴﻪ‬ ‫ﺍﻷﺣﻮﺍﻝ‬ ‫ﻓﻰ‬ ‫ﺃﻣﺒﻴﺮ‬٬‫ﻣﻌﻴﻨﻪ‬ ‫ﺗﺤﻮﻳﻞ‬ ‫ﻧﺴﺒﺔ‬ ‫ﺑﺈﺧﺘﻴﺎﺭ‬ ‫ﺫﻟﻚ‬ ‫ﻭﻳﺘﻢ‬ ‫ﺑـ‬ ‫ﺗﻌﺮﻑ‬Turns Ratio٬‫ﺍﻟﻤﺜﺎﻝ‬ ‫ﺳﺒﻴﻞ‬ ‫ﻋﻠﻰ‬ ‫ﺃﺷﻬﺮﻫﺎ‬ ‫ﻗﻴﺎﺳﻴﻪ‬ ‫ﻗﻴﻢ‬ ‫ﻭﻟﻬﺎ‬:100 : 5­200 : 5­300 : 5٬‫ﺇﻟﻰ‬ ‫ﻧﺼﻞ‬ ‫ﺣﺘﻰ‬ ‫ﻭﻫﻰ‬ ‫ﻋﻤﻠﻴﺎ‬ ‫ﻗﻴﻤﻪ‬ ‫ﺃﻗﺼﻰ‬3000 : 1. ‫ﺗﻴﺎﺭﻫﺎ‬ ‫ﻗﻴﺎﺱ‬ ‫ﺍﻟﻤﺮﺍﺩ‬ ‫ﺍﻟﺪﺍﺋﺮﻩ‬ ‫ﻣﻊ‬ ‫ﺍﻟﺘﻮﺍﻟﻰ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻭﻳﻮﺻﻞ‬. ‫ﻋﻦ‬ ‫ﺗﻜﻠﻢ‬‫؟‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺗﺮﻛﻴﺐ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻳﺘﻜﻮﻥ‬)C.T(‫ﻣﻦ‬: ۱­‫ﻭﺍﻟﻨﻴﻜﻞ‬ ‫ﺍﻟﺤﺪﻳﺪ‬ ‫ﻣﻦ‬ ‫ﺳﺒﻴﻜﻪ‬ ‫ﻣﻦ‬ ‫ﺃﻭﻣﺼﻨﻮﻉ‬ ‫ﺍﻟﺴﻠﻴﻜﻮﻧﻰ‬ ‫ﺍﻟﺼﻠﺐ‬ ‫ﻣﻦ‬ ‫ﻣﺼﻨﻮﻉ‬ ‫ﻗﻠﺐ‬٬‫ﺍﻟﻤﻐﻨﺎﻃﻴﺴﻴﻪ‬ ‫ﺍﻟﺪﺍﺋﺮﻩ‬ ‫ﻭﻳﻤﺜﻞ‬. ۲­‫ﻛﺒﻴﺮ‬ ‫ﻣﻘﻄﻊ‬ ‫ﺫﻯ‬ ‫ﻣﻮﺻﻞ‬ ‫ﻋﻦ‬ ‫ﻋﺒﺎﺭﻩ‬ ‫ﺇﺑﺘﺪﺍﺋﻰ‬ ‫ﻣﻠﻒ‬٬‫ﺍﻟﺨﻂ‬ ‫ﻣﻊ‬ ‫ﺍﻟﺘﻮﺍﻟﻰ‬ ‫ﻋﻠﻰ‬ ‫ﻭﻳﺘﺼﻞ‬ ‫ﺃﻛﺜﺮ‬ ‫ﺃﻭ‬ ‫ﻭﺍﺣﺪﻩ‬ ‫ﻟﻔﻪ‬ ‫ﻣﻦ‬ ‫ﻳﺘﻜﻮﻥ‬)line( ‫ﺑـ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺗﺴﻤﻴﺔ‬ ‫ﺟﺎءﺕ‬ ‫ﻫﻨﺎ‬ ‫ﻭﻣﻦ‬ ‫ﻋﻠﻴﻪ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺗﺮﻛﻴﺐ‬ ‫ﺳﻴﺘﻢ‬ ‫ﺍﻟﺬﻯ‬Series Transformer‫ﻣﺤﻮﻝ‬ ‫ﻣﻘﻨﻦ‬ ‫ﻛﺎﻥ‬ ‫ﻭﺇﺫﺍ‬ ‫ﻋﺎﻟﻴﺎ‬ ‫ﺍﻟﺘﻴﺎﺭ‬٬‫ﺍﻟﻤﻐﻨﺎﻃﻴﺴﻴﻪ‬ ‫ﺍﻟﺪﺍﺋﺮﻩ‬ ‫ﺧﻼﻝ‬ ‫ﻳﻤﺮ‬ ‫ﻣﺴﺘﻘﻴﻢ‬ ‫ﻣﻮﺻﻞ‬ ‫ﻋﻦ‬ ‫ﻋﺒﺎﺭﻩ‬ ‫ﻳﻜﻮﻥ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻓﺈﻥ‬. ۳­‫ﻣﻌﺰﻭﻝ‬ ‫ﺳﻠﻚ‬ ‫ﻣﻦ‬ ‫ﻣﺼﻨﻮﻋﻪ‬ ‫ﺍﻟﻠﻔﺎﺕ‬ ‫ﻣﻦ‬ ‫ﻛﺒﻴﺮ‬ ‫ﻋﺪﺩ‬ ‫ﻋﻦ‬ ‫ﻋﺒﺎﺭﻩ‬ ‫ﺛﺎﻧﻮﻯ‬ ‫ﻣﻠﻒ‬٬‫ﺍﻟﻘﻠﺐ‬ ‫ﻋﻠﻰ‬ ‫ﺗﻠﻒ‬٬‫ﺍﻟﻤﻠﻒ‬ ‫ﻋﻦ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻋﺰﻝ‬ ‫ﻳﺘﻢ‬ ‫ﺍﻟﻌﺰﻝ‬ ‫ﺯﺍﺩ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺯﺍﺩ‬ ‫ﻓﻜﻠﻤﺎ‬ ‫ﺍﻟﺘﺸﻐﻴﻞ‬ ‫ﺟﻬﺪ‬ ‫ﻋﻠﻰ‬ ‫ﺗﻌﺘﻤﺪ‬ ‫ﻋﺰﻝ‬ ‫ﺑﻤﺎﺩﺓ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬. ‫ﺟﺪﺍ‬ ‫ﺻﻐﻴﺮﻩ‬ ‫ﻭﺍﻟﺜﺎﻧﻮﻳﻪ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻴﻪ‬ ‫ﺍﻟﻤﻠﻔﺎﺕ‬ ‫ﻭﻣﻤﺎﻧﻌﺔ‬ ‫ﻣﻘﺎﻭﻣﺔ‬ ‫ﻓﻴﻪ‬ ‫ﺗﻜﻮﻥ‬ ‫ﺍﻟﻤﺜﺎﻟﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺃﻥ‬ ‫ﻭﻳﻼﺣﻆ‬
5. 5. ۱٤۱ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺗﻤﺜﻴﻞ‬ ‫ﻃﺮﻳﻘﺔ‬: ‫ﺍﻟﺘﺎﻟﻰ‬ ‫ﺍﻟﺸﻜﻞ‬ ‫ﻓﻠﻰ‬ ‫ﻛﻤﺎ‬ ‫ﺗﻤﺜﻴﻠﻪ‬ ‫ﻳﻤﻜﻦ‬ ‫ﻭﺑﺎﻟﺘﺎﻟﻰ‬ ‫ﺣﺪﻳﺪﻯ‬ ‫ﻭﻗﻠﺐ‬ ‫ﺛﺎﻧﻮﻯ‬ ‫ﻭﻣﻠﻒ‬ ‫ﺇﺑﺘﺪﺍﺋﻰ‬ ‫ﻣﻠﻒ‬ ‫ﻣﻦ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻳﺘﻜﻮﻡ‬ ‫ﺫﻛﻨﺎ‬ ‫ﻛﻤﺎ‬ ‫ﺛﺎﻧﻮﻳﻴﻦ‬ ‫ﻣﻠﻔﻴﻦ‬ ‫ﻋﻠﻰ‬ ‫ﻳﺤﺘﻮﻯ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺍﻟﺘﺎﻟﻰ‬ ‫ﺍﻟﺸﻜﻞ‬ ‫ﻳﺒﻴﻦ‬ ‫ﻛﻤﺎ‬ ‫ﺛﺎﻧﻮﻯ‬ ‫ﻣﻠﻒ‬ ‫ﻣﻦ‬ ‫ﺃﻛﺜﺮ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻳﺤﺘﻮﻯ‬ ‫ﺃﻥ‬ ‫ﻳﻤﻜﻦ‬ ‫ﻛﺎﻵﺗﻰ‬ ‫ﺑﻴﺎﻧﺎﺗﻪ‬ ‫ﻭﺗﻜﺘﺐ‬ ‫ﻟﻪ‬ ‫ﺍﻟﻤﺨﺮﺝ‬ ‫ﻗﺪﺭﺭﺓ‬ ‫ﺍﻟﺜﺎﻧﻮﻳﻴﻦ‬ ‫ﺍﻟﻤﻠﻔﻴﻦ‬ ‫ﺃﺣﺪ‬ ‫ﺃﻥ‬ ‫ﺫﻟﻚ‬ ‫ﻣﻌﻨﻰ‬15 VA‫ﺍﻟﺪﻗﻪ‬ ‫ﻭﺩﺭﺟﺔ‬0.5‫ﺍﻵﺧﺮ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﺑﻴﻨﻤﺎ‬ ‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﻷﺟﻬﺰﺓ‬ ‫ﻭﻳﺘﺨﺪﻡ‬ ‫ﻟﻪ‬ ‫ﺍﻟﻤﺨﺮﺝ‬ ‫ﻗﺪﺭﺓ‬30 VA‫ﺍﻟﺪﻗﻪ‬ ‫ﻭﺩﺭﺟﺔ‬5p20‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﻷﺟﻬﺰﺓ‬ ‫ﻭﻳﺴﺘﺨﺪﻡ‬. ‫ﺛﺎﻧﻮﻳﻴﻦ‬ ‫ﻣﻠﻔﻴﻦ‬ ‫ﻋﻠﻰ‬ ‫ﻳﺤﺘﻮﻯ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻓﻰ‬ ‫ﻣﻘﻄﻊ‬ ‫ﻳﻮﺿﺢ‬ ‫ﺍﻟﺘﺎﻟﻰ‬ ‫ﻭﺍﻟﺸﻜﻞ‬:
6. 6. ۱٤۲ ‫ﺃﻧﻮﺍﻉ‬ ‫ﻫﻰ‬ ‫ﻣﺎ‬‫؟‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﻫﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﻣﻦ‬ ‫ﺃﻧﻮﺍﻉ‬ ‫ﺛﻼﺛﺔ‬ ‫ﻳﻮﺟﺪ‬: ۱­‫ﺷﺒﺎﻙ‬ ‫ﺍﻟﻨﻮﻉ‬ ‫ﻣﻦ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬)‫ﺣﻠﻘﻰ‬(type C.T­type C.T or Through­type C.T or Ring–Window ‫ﺍﻟﺤﺪﻳﺪ‬ ‫ﺷﺮﺍﺋﺢ‬ ‫ﻣﻦ‬ ‫ﻣﺼﻨﻮﻋﻪ‬ ‫ﺃﺳﻄﻮﺍﻧﻴﻪ‬ ‫ﺣﻠﻘﻪ‬ ‫ﺷﻜﻞ‬ ‫ﻋﻠﻰ‬ ‫ﻗﻠﺐ‬ ‫ﻣﻦ‬ ‫ﻳﺘﻜﻮﻥ‬٬‫ﺍﻟﻘﻠﺐ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻟﻒ‬ ‫ﻳﺘﻢ‬–‫ﺃﻭ‬ ‫ﺍﻟﻜﺎﺑﻞ‬ ‫ﻳﻌﺘﺒﺮ‬ ‫ﺑﻴﻨﻤﺎ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻫﻮ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻟﻤﺤﻮﻝ‬ ‫ﺍﻟﺤﻠﻘﻴﻪ‬ ‫ﺍﻟﻔﺘﺤﻪ‬ ‫ﺧﻼﻝ‬ ‫ﺍﻟﻤﺎ‬ ‫ﺍﻟﺨﻂ‬ ‫ﺷﻜﻞ‬)۱۱­٤(‫ﻛﺎﺑﻞ‬ ‫ﺧﻼﻝ‬ ‫ﻳﻤﺮﺍﻥ‬ ‫ﺍﻟﺤﻠﻘﻰ‬ ‫ﺍﻟﻨﻮﻉ‬ ‫ﻣﻦ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﺤﻮﻟﻰ‬ ‫ﻳﻮﺿﺢ‬ ‫ﺃ‬)L,K(‫ﺷﻜﻞ‬ ‫ﻓﻰ‬ ‫ﺑﻴﻨﻤﺎ‬)۱۱­٤(‫ﺍﻟﻤﻠﻔﻴﻦ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﺗﻢ‬ ‫ﺏ‬ ‫ﻗﻴﺎ‬ ‫ﺃﻭ‬ ‫ﺣﻤﺎﻳﻪ‬ ‫ﺟﻬﺎﺯ‬ ‫ﻋﻠﻰ‬ ‫ﻭﺗﻮﺻﻴﻠﻬﻤﺎ‬ ‫ﺍﻟﺘﻮﺍﻟﻰ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻟﻤﺤﻮﻟﻰ‬ ‫ﺍﻟﺜﺎﻧﻮﻳﻴﻦ‬‫ﺱ‬ ‫ﺷﻜﻞ‬ ‫ﻓﻰ‬)۱۱­٤(‫ﻣﺴﺘﻘﻞ‬ ‫ﺟﻬﺎﺯ‬ ‫ﻋﻠﻰ‬ ‫ﺛﺎﻧﻮﻯ‬ ‫ﻣﻠﻒ‬ ‫ﻛﻞ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﺗﻢ‬ ‫ﺟـ‬)‫ﻗﻴﺎﺱ‬ ‫ﺃﻭ‬ ‫ﺣﻤﺎﻳﻪ‬( ۲­‫ﺍﻟﻘﻀﻴﺐ‬ ‫ﺫﻯ‬ ‫ﺍﻟﻨﻮﻉ‬ ‫ﻣﻦ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬Type C.T­Bar ‫ﻣﺼﻤﺖ‬ ‫ﻗﻀﻴﺐ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﻨﻮﻉ‬ ‫ﻫﺬﺍ‬ ‫ﻳﺤﺘﻮﻯ‬)solid Bar(‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻟﻤﺤﻮﻝ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻫﻮ‬٬‫ﺃﻭ‬ ‫ﺍﻟﺨﻂ‬ ‫ﻣﻊ‬ ‫ﺍﻟﺘﻮﺍﻟﻰ‬ ‫ﻋﻠﻰ‬ ‫ﺗﻮﺻﻴﻠﻪ‬ ‫ﻭﻳﺘﻢ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺗﺮﻛﻴﺐ‬ ‫ﺍﻟﻤﺮﺍﺩ‬ ‫ﺍﻟﻜﺎﺑﻞ‬‫ﺍﻟﻤﺮﺗﻔﻌﻪ‬ ‫ﺍﻟﺘﻴﺎﺭﺍﺕ‬ ‫ﻋﻦ‬ ‫ﺍﻟﻨﺎﺗﺠﻪ‬ ‫ﺍﻹﺟﻬﺎﺩﺍﺕ‬ ‫ﺍﻟﻨﻮﻉ‬ ‫ﻫﺬﺍ‬ ‫ﻭﻳﺘﺤﻤﻞ‬ ‫ﻋﻠﻴﻪ‬ ‫ﺍﻟﺘﻴﺎﺭ‬. ۳­‫ﺍﻟﻤﻠﻔﻮﻑ‬ ‫ﺍﻟﻨﻮﻉ‬ ‫ﻣﻦ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬Type C.T­Wound ‫ﻣﻦ‬ ‫ﺃﻛﺜﺮ‬ ‫ﺃﻭ‬ ‫ﻟﻔﻪ‬ ‫ﻋﻦ‬ ‫ﻋﺒﺎﺭﻩ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻳﻜﻮﻥ‬ ‫ﻭﻏﺎﻟﺒﺎ‬ ‫ﻣﻨﻔﺼﻠﻴﻦ‬ ‫ﺛﺎﻧﻮﻯ‬ ‫ﻭﻣﻠﻒ‬ ‫ﺇﺑﺘﺪﺍﺋﻰ‬ ‫ﻭﻣﻠﻒ‬ ‫ﺍﻟﺤﺪﻳﺪ‬ ‫ﺷﺮﺍﺋﺢ‬ ‫ﻣﻦ‬ ‫ﻗﻠﺐ‬ ‫ﻣﻦ‬ ‫ﻳﺘﻜﻮﻥ‬ ‫ﻛﺒﻴﺮ‬ ‫ﻣﻘﻄﻊ‬ ‫ﺫﻯ‬ ‫ﻣﻮﺻﻞ‬٬‫ﻋﻠ‬ ‫ﻭﻳﺘﺼﻞ‬‫ﻋﻠﻴﻬﺎ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺗﺮﻛﻴﺐ‬ ‫ﺍﻟﻤﺮﺍﺩ‬ ‫ﺍﻟﺪﺍﺋﺮﻩ‬ ‫ﻣﻊ‬ ‫ﺍﻟﺘﻮﺍﻟﻰ‬ ‫ﻰ‬ ‫ﺛﻨﺎﺋﻴﻪ‬ ‫ﺗﺤﻮﻳﻞ‬ ‫ﻧﺴﺒﺔ‬ ‫ﻋﻠﻰ‬ ‫ﻳﺤﺘﻮﻯ‬ ‫ﺃﺣﻴﺎﻧﺎ‬ ‫ﺍﻟﻨﻮﻉ‬ ‫ﻫﺬﺍ‬)Dual Ratio(‫ﻋﻠﻰ‬ ‫ﺗﻮﺻﻴﻠﻬﻤﺎ‬ ‫ﻳﺘﻢ‬ ‫ﺇﺑﺘﺪﺍﺋﻴﻴﻦ‬ ‫ﻣﻠﻔﻴﻦ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﻤﺤﻮﻝ‬ ‫ﻳﺤﺘﻮﻯ‬ ‫ﺃﻯ‬ ‫ﺍﻟﺘﺤﻮﻳﻞ‬ ‫ﻧﺴﺒﺔ‬ ‫ﺣﺴﺐ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺘﻮﺍﺯﻯ‬ ‫ﺃﻭ‬ ‫ﺍﻟﺘﻮﺍﻟﻰ‬.‫ﺷﻜﻞ‬)۱۹­٤(‫ﺛﺎﻧﻮﻯ‬ ‫ﻭﻣﻠﻒ‬ ‫ﺇﺑﺘﺪﺍﺋﻴﻴﻦ‬ ‫ﻣﻠﻔﻴﻦ‬ ‫ﻋﻠﻰ‬ ‫ﻳﺤﺘﻮﻯ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻳﻮﺿﺢ‬ ‫ﺍﻟﺘﺤﻮﻳﻞ‬ ‫ﻭﻧﺴﺒﺔ‬)100­200/5(‫ﺗﺤﻮﻳﻞ‬ ‫ﻧﺴﺒﺔ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺤﺼﻮﻝ‬ ‫ﻳﻤﻜﻦ‬ ‫ﺃﻯ‬100/5‫ﻛﻤﺎ‬ ‫ﺍﻟﺘﻮﺍﻟﻰ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻴﻴﻦ‬ ‫ﺍﻟﻤﻠﻔﻴﻦ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﺗﻢ‬ ‫ﺇﺫﺍ‬ ‫ﺷﻜﻞ‬ ‫ﻓﻰ‬)۱۹­٤(‫ﺗﺤﻮﻳﻞ‬ ‫ﻧﺴﺒﺔ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺤﺼﻮﻝ‬ ‫ﺃﻭ‬ ‫ﺃ‬200/5‫ﺍﻹﺑﺘﺪﺍﺋﻴﻴ‬ ‫ﺍﻟﻤﻠﻔﻴﻴﻦ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﺗﻢ‬ ‫ﺇﺫﺍ‬‫ﺷﻜﻞ‬ ‫ﻓﻰ‬ ‫ﻛﻤﺎ‬ ‫ﺍﻟﺘﻮﺍﺯﻯ‬ ‫ﻋﻠﻰ‬ ‫ﻦ‬)۱۹­٤( ‫ﺏ‬.
7. 7. ۱٤۳ ‫ﺷﻜﻞ‬)۱۹­٤( ‫؟‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﻣﻊ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﻳﺘﻢ‬ ‫ﻛﻴﻒ‬ ‫ﺍﻟـ‬ ‫ﺇﻟﻰ‬ ‫ﻣﺒﺎﺷﺮﺓ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﻳﺘﻢ‬ ‫ﺍﻷﺣﻴﺎﻥ‬ ‫ﺑﻌﺾ‬ ‫ﻓﻰ‬Relay‫ﻣﻠﻒ‬ ‫ﻓﻰ‬ ‫ﻣﺒﺎﺷﺮﺓ‬ ‫ﻟﻴﻤﺮ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺇﺳﺘﺨﺪﺍﻡ‬ ‫ﺑﻤﻌﻨﻰ‬ ‫؛‬ ‫ﺍﻟﺸﻜﻞ‬ ‫ﻓﻰ‬ ‫ﻛﻤﺎ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺟﻬﺎﺯ‬4­2‫ﺃ‬٬‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻃﺮﻓﻰ‬ ‫ﺑﻴﻦ‬ ‫ﺟﺪﺍ‬ ‫ﺻﻐﻴﺮﻩ‬ ‫ﻣﻘﺎﻭﻣﻪ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﻳﺘﻢ‬ ‫ﺃﺧﺮﻯ‬ ‫ﺃﺣﻴﺎﻥ‬ ‫ﻭﻓﻰ‬–‫ﺇﻟﻰ‬ ‫ﺗﺼﻞ‬ ‫ﺍﻷﻭﻡ‬ ‫ﻣﻦ‬ ‫ﻋﺸﺮﺓ‬ ‫ﻣﻦ‬ ‫ﺟﺰء‬–‫ﻟﻠـ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻤﺎﺭ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﻊ‬ ‫ﻳﺘﻨﺎﺳﺐ‬ ‫ﺟﻬﺪ‬ ‫ﻭﻳﻨﺸﺄﻋﻠﻴﻬﺎ‬CT٬‫ﺍﻟﺸﻜﻞ‬ ‫ﻓﻰ‬ ‫ﻛﻤﺎ‬4­2‫ﺏ‬ .‫ﺇﻟﻰ‬ ‫ﺗﺤﺘﺎﺝ‬ ‫ﻭﺍﻟﺘﻰ‬ ‫ﺍﻟﺮﻗﻤﻴﻪ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﻣﻊ‬ ‫ﻏﺎﻟﺒﺎ‬ ‫ﻳﺴﺘﺨﺪﻡ‬ ‫ﺍﻷﺳﻠﻮﺏ‬ ‫ﻭﻫﺬﺍ‬‫ﺇﻟﻰ‬ ‫ﻟﺘﺤﻮﻳﻠﻪ‬ ‫ﺗﻤﻬﻴﺪﺍ‬ ‫ﺟﻬﺪ‬ ‫ﺇﻟﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﺗﺤﻮﻳﻞ‬Digital Numbers‫ﺑﻮﺍﺳﻄﺔ‬A/D Converter. ‫؟‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻋﻤﻞ‬ ‫ﻧﻈﺮﻳﺔ‬ ‫ﻫﻰ‬ ‫ﻣﺎ‬ ‫ﺗﻴﺎﺭﻫﺎ‬ ‫ﻗﻴﺎﺱ‬ ‫ﺍﻟﻤﺮﺍﺩ‬ ‫ﺍﻟﺪﺍﺋﺮﻩ‬ ‫ﻣﻊ‬ ‫ﺍﻟﺘﻮﺍﻟﻰ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻟﻤﺤﻮﻝ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻃﺮﻓﻰ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﻳﺘﻢ‬٬‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﺟﻬﺎﺯ‬ ‫ﻳﻮﺻﻞ‬ ‫ﺣﻴﻦ‬ ‫ﻓﻰ‬/ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻃﺮﻓﻰ‬ ‫ﺑﻴﻦ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬. ‫ﺃﻥ‬ ‫ﻳﻌﻨﻰ‬ ‫ﻟﻠﻤﺤﻮﻻﺕ‬ ‫ﺍﻟﻌﺎﻣﻪ‬ ‫ﻟﻠﻨﻈﺮﻳﻪ‬ ‫ﻃﺒﻘﺎ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﻊ‬ ‫ﻳﺘﻨﺎﺳﺐ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺃﻥ‬ ‫ﺍﻟﻤﻌﺮﻭﻑ‬ ‫ﻭﻣﻦ‬: ‫ﺣﻴﺚ‬N‫ﺑـ‬ ‫ﻭﺗﻌﺮﻑ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻟﻔﺎﺕ‬ ‫ﻋﺪﺩ‬ ‫ﺇﻟﻰ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻟﻔﺎﺕ‬ ‫ﻋﺪﺩ‬ ‫ﺑﻴﻦ‬ ‫ﺍﻟﻨﺴﺒﻪ‬ ‫ﻫﻰ‬Turns Ratio ‫ﻣﻌﺎﻭﻗﻪ‬ ‫ﻟﻪ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺃﻭ‬ ‫ﻟﻠﻘﻴﺎﺱ‬ ‫ﻣﺎ‬ ‫ﺟﻬﺎﺯ‬ ‫ﺇﻟﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﻭﻋﻨﺪ‬ZB٬‫ﻳﻨﺸﺄ‬ ‫ﺳﻮﻑ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻤﺎﺭ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻓﺈﻥ‬ ‫ﺟﻬﺪ‬ ‫ﻇﻬﻮﺭ‬ ‫ﻋﻨﻪ‬ ‫ﻳﻨﺘﺞ‬ ‫ﺳﻮﻑ‬ ‫ﻣﻐﻨﺎﻃﻴﺴﻴﺎ‬ ‫ﻓﻴﻀﺎ‬e.m.f‫ﺑﺎﻟﺮﻣﺰ‬ ‫ﻟﻪ‬ ‫ﻭﻳﺮﻣﺰ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﻃﺮﻓﻰ‬ ‫ﺑﻴﻦ‬Es٬‫ﺗﻴﺎﺭ‬ ‫ﻣﺮﻭﺭ‬ ‫ﻓﻰ‬ ‫ﻳﺘﺴﺒﺐ‬ ‫ﺍﻟﺬﻯ‬ ‫ﻭﻫﻮ‬ Is‫ﺍﻟﺸﻜﻞ‬ ‫ﻓﻰ‬ ‫ﻛﻤﺎ‬6­2‫ﻳﻈﻬ‬ ‫ﻭﺑﺎﻟﺘﺎﻟﻰ‬‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺟﻬﺎﺯ‬ ‫ﻃﺮﻓﻰ‬ ‫ﻋﻠﻰ‬ ‫ﺮ‬/‫ﻗﺪﺭﻩ‬ ‫ﺟﻬﺪ‬ ‫ﺍﻟﻘﻴﺎﺱ‬Vo/p‫ﻳﺴﺎﻭﻯ‬ ‫ﺗﻤﺜﻞ‬ ‫ﺣﻴﺚ‬RCT‫ﺍﻟﺘﻮﺻﻴﻞ‬ ‫ﺃﺳﻼﻙ‬ ‫ﻣﻘﺎﻭﻣﺔ‬ ‫ﻟﻬﺎ‬ ‫ﻳﻀﺎﻑ‬ ‫ﻭﻗﺪ‬ ‫ﺍﻟﻤﺴﺘﺨﺪﻡ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻟﻤﺤﻮﻝ‬ ‫ﺍﻟﻤﻜﺎﻓﺌﻪ‬ ‫ﺍﻟﻤﻘﺎﻭﻣﻪ‬RL
8. 8. ۱٤٤ ‫ﺃﻥ‬ ‫ﺑﻤﻌﻨﻰ‬ ‫ﺍﻟﻔﻴﺾ‬ ‫ﺗﻐﻴﺮ‬ ‫ﻣﻌﺪﻝ‬ ‫ﻣﻊ‬ ‫ﻃﺮﺩﺑﺎ‬ ‫ﻳﺘﻨﺎﺳﺐ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻃﺮﻓﻰ‬ ‫ﺑﻴﻦ‬ ‫ﺍﻟﻨﺎﺷﺊ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻫﺬﺍ‬ ‫ﻻﺣﻆ‬ ‫ﺟﻬﺪ‬ ‫ﺃﻗﺼﻰ‬ ‫ﻓﺈﻥ‬ ‫ﻟﻠﻤﺤﻮﻻﺕ‬ ‫ﺍﻟﻌﺎﻣﻪ‬ ‫ﻟﻠﻨﻈﺮﻳﻪ‬ ‫ﻭﻃﺒﻘﺎ‬EK‫ﺑـ‬ ‫ﻭﻳﻌﺮﻑ‬ ‫ﺍﻟﻤﺤﻮﻝ‬ ‫ﻃﺮﻓﻰ‬ ‫ﺑﻴﻦ‬ ‫ﻳﻨﺸﺄ‬Knee­ point Voltage‫ﻳﺴﺎﻭﻯ‬ (1­2) ‫ﺣﻴﺚ‬F‫ﻭ‬ ‫ﺍﻟﺘﺮﺩﺩ‬ ‫ﻫﻰ‬N‫ﺍﻟﻠﻔﺎﺕ‬ ‫ﻋﺪﺩ‬ ‫ﻫﻰ‬. ‫ﻣﻌﺎﻭﻗﻪ‬ ‫ﺃﻗﺼﻰ‬ ‫ﻟﺘﺤﺪﻳﺪ‬ ‫ﺍﻟﻘﻴﻤﻪ‬ ‫ﻫﺬﻩ‬ ‫ﻭﺗﺴﺘﺨﺪﻡ‬ZB‫ﻣﻌﻴﻦ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻃﺮﻓﻰ‬ ‫ﺑﻴﻦ‬ ‫ﺗﻮﺻﻴﻠﻬﺎ‬ ‫ﻳﻤﻜﻦ‬. ‫ﻣﻨﺤﻨﻰ‬ ‫ﻋﻦ‬ ‫ﺗﻜﻠﻢ‬‫؟‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺍﻟﻤﻐﻨﺎﻃﻴﺴﻴﻪ‬ ‫ﻟﻜﻞ‬ ‫ﺃﻥ‬ ‫ﺍﻟﻤﻌﺮﻭﻑ‬ ‫ﻣﻦ‬CT‫ﺍﻟﻤﺴﺒﺐ‬ ‫ﻭﺍﻟﺘﻴﺎﺭ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻓﻰ‬ ‫ﻳﻨﺸﺄ‬ ‫ﺍﻟﺬﻯ‬ ‫ﺍﻟﻔﻮﻟﺖ‬ ‫ﺑﻴﻦ‬ ‫ﺍﻟﻌﻼﻗﻪ‬ ‫ﻳﻮﺿﺢ‬ ‫ﺑﻪ‬ ‫ﺧﺎﺹ‬ ‫ﻣﻐﻨﺎﻃﻴﺴﻴﻪ‬ ‫ﻣﻨﺤﻨﻰ‬ ‫ﻟﻠﻔﻴﺾ‬٬‫ﺑـ‬ ‫ﺍﻟﻤﻌﺮﻭﻑ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻭﻫﻮ‬IeExcitation Current.‫ﺍﻟﺠﺎﻧﺐ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻤﺘﻮﻟﺪ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﻦ‬ ‫ﺻﻐﻴﺮ‬ ‫ﺟﺰء‬ ‫ﻳﻤﺜﻞ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻭﻫﺬﺍ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬٬‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻟﻤﺤﻮﻝ‬ ‫ﺍﻟﺪﺍﺧﻠﻴﻪ‬ ‫ﺍﻟﻤﻌﺎﻭﻗﻪ‬ ‫ﺩﺍﺧﻞ‬ ‫ﻳﺴﺤﺐ‬ ‫ﻭﻫﻮ‬Ze‫ﺍﻟﺘﺎﻟﻰ‬ ‫ﺍﻟﺸﻜﻞ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻟﻤﺤﻮﻝ‬ ‫ﺍﻟﻤﻜﺎﻓﺌﻪ‬ ‫ﺍﻟﺪﺍﺋﺮﻩ‬ ‫ﺿﻤﻦ‬ ‫ﺗﻈﻬﺮ‬ ‫ﺍﻟﺘﻰ‬ .‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺟﻬﺎﺯ‬ ‫ﺃﻥ‬ ‫ﻻﺣﻆ‬/‫ﺍ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﻦ‬ ‫ﺍﻷﻛﺒﺮ‬ ‫ﺍﻟﺠﺰء‬ ‫ﻳﺤﺐ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﻃﺮﻓﻰ‬ ‫ﺑﻴﻦ‬ ‫ﺍﻟﻤﺮﻛﺐ‬ ‫ﺍﻟﻘﻴﺎﺱ‬‫ﻟﺜﺎﻧﻮﻯ‬. ‫ﺑـ‬ ‫ﺍﻟﻤﻐﻨﺎﻃﻴﺴﻴﻪ‬ ‫ﻣﻨﺤﻨﻰ‬ ‫ﻭﻳﻌﺮﻑ‬Magnetization Curve‫ﺑـ‬ ‫ﺃﻳﻀﺎ‬ ‫ﻭﻳﺴﻤﻰ‬Excitation Curve‫ﻧﻘﻄﺔ‬ ‫ﻋﻠﻴﻪ‬ ‫ﻭﺗﻮﺟﺪ‬Knee­ point‫ﺍﻹﻧﻘﻼﺏ‬ ‫ﻧﻘﻄﺔ‬ ‫ﻭﺗﺴﻤﻰ‬. ‫ﻗﺪﺭﻫﺎ‬ ‫ﺯﻳﺎﺩﻩ‬ ‫ﻓﻰ‬ ‫ﺗﺘﺴﺒﺐ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺍﻟﻨﻘﻄﻪ‬ ‫ﺑﺄﻧﻬﺎ‬ ‫ﺍﻟﻨﻘﻄﻪ‬ ‫ﻫﺬﻩ‬ ‫ﻭﺗﻌﺮﻑ‬10%‫ﺍﻟﺠﻬﺪ‬ ‫ﻗﻴﻤﺔ‬ ‫ﻓﻰ‬Es‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻗﻴﻤﺔ‬ ‫ﺇﺭﺗﻔﺎﻉ‬ ‫ﻧﺘﻴﺠﺔ‬Ie‫ﺑﻤﻘﺪﺍﺭ‬50 %.‫ﺁﺧﺮ‬ ‫ﺑﻤﻌﻨﻰ‬٬‫ﺍﻟـ‬ ‫ﺑﻌﺪﻫﺎ‬ ‫ﻳﺒﺪﺃ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺍﻟﻨﻘﻄﻪ‬ ‫ﺃﻧﻬﺎ‬CT‫ﺑﺎﻟـ‬ ‫ﻳﺴﻤﻰ‬ ‫ﻣﺎ‬ ‫ﻣﺮﺣﻠﺔ‬ ‫ﺩﺧﻮﻝ‬ ‫ﻓﻰ‬Saturation.‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﻭﺃﻏﻠﺐ‬ ‫ﻟﻠﻤﺤﻮﻝ‬ ‫ﺗﺸﺒﻊ‬ ‫ﻳﺤﺪﺙ‬ ‫ﻻ‬ ‫ﺣﺘﻰ‬ ‫ﺍﻟﻨﻘﻄﻪ‬ ‫ﻫﺬﻩ‬ ‫ﻗﺒﻞ‬ ‫ﺍﻟﺨﻄﻴﻪ‬ ‫ﺍﻟﻤﻨﻄﻘﻪ‬ ‫ﻓﻰ‬ ‫ﺗﻌﻤﻞ‬ ‫ﺃﻥ‬ ‫ﻳﺠﺐ‬.
9. 9. ۱٤٥ ‫؟‬ ‫ﺍﻟﺘﺸﺒﻊ‬ ‫ﻣﺸﻜﻠﺔ‬ ‫ﻋﻦ‬ ‫ﺗﻜﻠﻢ‬ ‫ﻓﻴﺾ‬ ‫ﻋﻨﻪ‬ ‫ﻳﻨﺘﺞ‬ ‫ﺍﻟﻤﺘﺮﺩﺩ‬ ‫ﺍﻟﻜﻬﺮﺑﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﺃﻥ‬ ‫ﻣﻌﻠﻮﻡ‬‫ﻣﻌﻪ‬ ‫ﻃﺮﺩﻳﺎ‬ ‫ﻳﺘﻨﺎﺳﺐ‬ ‫ﻣﺘﺮﺩﺩ‬ ‫ﻣﻐﻨﺎﻃﻴﺴﻲ‬٬‫ﺍﻟﻔﻴﺾ‬ ‫ﺯﺍﺩ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﺯﺍﺩ‬ ‫ﻛﻠﻤﺎ‬ ‫ﻭﺑﺎﻟﺘﺎﻟﻰ‬٬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻗﻴﻤﺔ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻜﺒﻴﺮﻩ‬ ‫ﺍﻟﺰﻳﺎﺩﻩ‬ ‫ﻣﻊ‬ ‫ﺗﺤﺪﺙ‬ ‫ﺍﻟﺘﺸﺒﻊ‬ ‫ﻭﻣﺸﻜﻠﺔ‬)‫ﺍﻟﻌﻄﻞ‬ ‫ﺣﺪﻭﺙ‬ ‫ﻋﻨﺪ‬(٬‫ﻻ‬ ‫ﺟﺪﺍ‬ ‫ﻋﺎﻟﻰ‬ ‫ﻓﻴﺾ‬ ‫ﻧﺸﻮء‬ ‫ﻓﻰ‬ ‫ﺫﻟﻚ‬ ‫ﻳﺘﺴﺒﺐ‬ ‫ﺣﻴﺚ‬ ‫ﺍﻟﺘﺸﺒﻊ‬ ‫ﻣﺎﻳﺴﻤﻰ‬ ‫ﻟﻪ‬ ‫ﻓﻴﺤﺪﺙ‬ ‫ﺗﺤﻤﻠﻪ‬ ‫ﺍﻟﺤﺪﻳﺪﻱ‬ ‫ﺍﻟﻘﻠﺐ‬ ‫ﻳﺴﺘﻄﻴﻊ‬saturation ‫ﺍﻟﻌﺎﻟﻰ‬ ‫ﺍﻟﻔﻴﺾ‬ ‫ﺯﻳﺎﺩﺓ‬ ‫ﺗﻮﻗﻒ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺤﺪﻳﺪﻯ‬ ‫ﺍﻟﻘﻠﺐ‬ ‫ﺗﺸﺒﻊ‬ ‫ﻳﺘﺴﺒﺐ‬٬‫ﺛﺎﺑﺘﻪ‬ ‫ﻣﻌﻴﻨﻪ‬ ‫ﻗﻴﻤﻪ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﻔﻴﺾ‬ ‫ﻗﻴﻤﺔ‬ ‫ﺗﺜﺒﺖ‬ ‫ﻭﺑﺎﻟﺘﺎﻟﻰ‬)‫ﺍﻟﺘﺸﺒﻊ‬ ‫ﺣﺪ‬(٬ ‫ﺻﻐﻴﺮﺍ‬ ‫ﺃﺻﺒﺢ‬ ‫ﺍﻟﻔﻴﺾ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺘﻐﻴﺮ‬ ‫ﻣﻌﺪﻝ‬ ‫ﺃﻥ‬ ‫ﺑﻤﻌﻨﻰ‬)‫ﺍﻟﻔﻴﺾ‬ ‫ﺗﻐﻴﺮ‬ ‫ﻣﻌﺪﻝ‬ ‫ﻣﻊ‬ ‫ﻃﺮﺩﻳﺎ‬ ‫ﻳﺘﻨﺎﺳﺐ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﺃﻥ‬ ‫ﺗﺬﻛﺮ‬dΦ/dt(٬‫ﻻ‬ ‫ﻭﺑﺎﻟﺘﺎﻟﻰ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻓﻰ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺃﻯ‬ ‫ﻳﻨﺸﺄ‬)‫ﺍﻟﺼﻔﺮ‬ ‫ﺇﻟﻰ‬ ‫ﺗﻘﺮﻳﺒﺎ‬ ‫ﻳﺼﻞ‬( ‫ﺍﻟـ‬ ‫ﻣﺮﻛﺒﺔ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺘﺪﺭﻳﺠﻰ‬ ‫ﺍﻟﻨﻘﺺ‬ ‫ﺫﻟﻚ‬ ‫ﺍﻟﺘﺎﻟﻰ‬ ‫ﺍﻟﺸﻜﻞ‬ ‫ﻓﻰ‬ ‫ﻻﺣﻆ‬DC Componenet‫ﻗﻴﻤﺔ‬ ‫ﺗﺸﻮﻩ‬ ‫ﻓﻰ‬ ‫ﺍﻷﺳﺎﺳﻴﻪ‬ ‫ﺍﻟﻌﻮﺍﻣﻞ‬ ‫ﺃﺣﺪ‬ ‫ﻭﻫﻰ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺑﺘﻴﺎﺭ‬ ‫ﻣﻘﺎﺭﻧﺔ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺗﻴﺎﺭ‬٬‫ﻗﻴﻤﺔ‬ ‫ﻭﻋﻠﻰ‬ ‫ﺍﻟﻘﻔﻞ‬ ‫ﻟﺤﻈﺔ‬ ‫ﻋﻠﻰ‬ ‫ﻗﻴﻤﺘﻬﺎ‬ ‫ﻭﺗﺘﻮﻗﻒ‬X٬R‫ﻋﻠﻰ‬ ‫ﺑﻘﺎﺋﻬﺎ‬ ‫ﻣﺪﺓ‬ ‫ﺗﺘﻮﻗﻒ‬ ‫ﺑﻴﻨﻤﺎ‬ ‫ﻟﻠﺪﺍﺋﺮﻩ‬ ‫ﺍﻟـ‬ ‫ﻗﻴﻤﺔ‬X٬R‫ﻓﻘﻂ‬.‫ﺍﻟـ‬ ‫ﺑﺴﺒﺐ‬ ‫ﻟﻴﺲ‬ ‫ﺍﻟﻘﻴﻤﻪ‬ ‫ﻓﻰ‬ ‫ﺍﻹﺧﺘﻼﻑ‬ ‫ﺃﻥ‬ ‫ﺃﻳﻀﺎ‬ ‫ﻻﺣﻆ‬turns ratio‫ﻓﺤﺴﺐ‬٬‫ﺍﻟـ‬ ‫ﺑﺴﺒﺐ‬ ‫ﺃﻳﻀﺎ‬ ‫ﻭﺇﻧﻤﺎ‬ saturation‫ﻛﺬﻟﻚ‬٬‫ﺗﺸﻮﻩ‬ ‫ﻟﻪ‬ ‫ﺣﺪﺙ‬ ‫ﻗﺪ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﺃﻥ‬ ‫ﻧﻘﻮﻝ‬ ‫ﻭﻟﺬﺍ‬Distortion‫ﻣﻬﻤ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﻟﺠﻬﺎﺯ‬ ‫ﺳﻠﻴﻤﺎ‬ ‫ﺃﺩﺍءﺍ‬ ‫ﻧﺘﻮﻗﻊ‬ ‫ﻻ‬ ‫ﻭﺑﺎﻟﺘﺎﻟﻰ‬‫ﺎ‬ ‫ﺍﻟﻤﺸﻜﻠﻪ‬ ‫ﻫﺬﻩ‬ ‫ﺣﻞ‬ ‫ﻳﺘﻢ‬ ‫ﻟﻢ‬ ‫ﻣﺎ‬ ‫ﺩﻗﺘﻪ‬ ‫ﻛﺎﻧﺖ‬. ­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­ ‫ﺑﺤﻤﻞ؟‬ ‫ﺍﺗﺼﺎﻟﻬﻢ‬ ‫ﻋﺪﻡ‬ ‫ﻋﻨﺪ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻃﺮﻓﻲ‬ ‫ﻗﺼﺮ‬ ‫ﻳﺠﺐ‬ ‫ﻟﻤﺎﺫﺍ‬ ‫ﺍﻻﺑﺘﺪﺍﺋﻲ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻗﻴﻤﺔ‬ ‫ﺗﺘﺤﺪﺩ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻓﻲ‬)‫ﺍﻟﻘ‬ ‫ﺃﻭ‬ ‫ﺍﻟﺨﻂ‬ ‫ﺃﻭ‬ ‫ﺍﻟﻜﺎﺑﻞ‬ ‫ﻓﻲ‬ ‫ﺍﻟﻤﺎﺭ‬‫ﺍﻟﻌﻤﻮﻣﻴﺔ‬ ‫ﻀﺒﺎﻥ‬...‫ﺇﻟﺦ‬(‫ﺩﺧﻞ‬ ‫ﻭﻻ‬ ‫ﺍﻟﺸﺒﻜﺔ‬ ‫ﻇﺮﻭﻑ‬ ‫ﺣﺴﺐ‬ ‫ﻗﻴﻤﺘﻪ‬ ‫ﻓﻲ‬ ‫ﺍﻟﺜﺎﻧﻮﻱ‬ ‫ﻟﺘﻴﺎﺭ‬)‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻋﻜﺲ‬ ‫ﻋﻠﻰ‬.(‫ﺩﺍﺋﺮﺗﻪ‬ ‫ﻇﺮﻭﻑ‬ ‫ﻓﻴﻬﺎ‬ ‫ﺑﻤﺎ‬ ‫ﺍﻟﻤﺤﻮﻝ‬ ‫ﻇﺮﻭﻑ‬ ‫ﻋﻦ‬ ‫ﻣﺴﺘﻘﻞ‬ ‫ﺍﻻﺑﺘﺪﺍﺋﻲ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺃﻥ‬ ‫ﺃﻱ‬ ‫ﺍﻟﺜﺎﻧﻮﻳﺔ‬.‫ﻛﻬﺮ‬ ‫ﺩﺍﻓﻌﺔ‬ ‫ﻗﻮﺓ‬ ‫ﺑﺘﻮﻟﻴﺪ‬ ‫ﻳﻘﻮﻡ‬ ‫ﺍﻟﺬﻱ‬ ‫ﺍﻟﻤﺤﻮﻝ‬ ‫ﻗﻠﺐ‬ ‫ﻓﻲ‬ ‫ﺍﻟﻤﻐﻨﺎﻃﻴﺴﻲ‬ ‫ﺍﻟﻔﻴﺾ‬ ‫ﺑﺈﻧﺘﺎﺝ‬ ‫ﺍﻻﺑﺘﺪﺍﺋﻲ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﻌﻈﻢ‬ ‫ﻳﻘﻮﻡ‬‫ﻣﻠﻔﺎﺕ‬ ‫ﻓﻲ‬ ‫ﺑﻴﺔ‬ ‫ﺍﻟﺜﺎﻧﻮﻱ‬.‫ﻳﻤﺜﻞ‬ ‫ﺍﻻﺑﺘﺪﺍﺋﻲ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺃﻥ‬ ‫ﺃﻱ‬)‫ﺃﻏﻠﺒﻪ‬ ‫ﻓﻲ‬(‫ﺍﻟﻤﻐﻨﻄﺔ‬ ‫ﺗﻴﺎﺭ‬.‫ﺍﻟﺤﻤﻞ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻳﻘﻮﻡ‬)‫ﺍﻟﺜﺎﻧﻮﻱ‬ ‫ﻓﻲ‬(‫ﻣﻐﻨﺎﻃﻴﺴﻲ‬ ‫ﻓﻴﺾ‬ ‫ﺇﻧﺘﺎﺝ‬ ‫ﺑﻤﻬﻤﺔ‬ ‫ﺍﻟﺜﺎﻧﻮﻱ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻃﺮﻓﻲ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﻦ‬ ‫ﻭﺑﺎﻟﺘﺎﻟﻲ‬ ‫ﺍﻟﻤﺤﺼﻞ‬ ‫ﺍﻟﻔﻴﺾ‬ ‫ﻣﻦ‬ ‫ُﺤﺪ‬‫ﻳ‬ ‫ﻣﻤﺎ‬ ‫ﺍﻻﺑﺘﺪﺍﺋﻲ‬ ‫ﻟﻔﻴﺾ‬ ‫ﻣﻌﺎﻛﺲ‬.‫ﺩﺍﺋﺮﺓ‬ ‫ﺍﺗﺼﺎﻝ‬ ‫ﻋﺪﻡ‬ ‫ﺣﺎﻟﺔ‬ ‫ﻭﻓﻲ‬ ‫ﺗﻴ‬ ‫ﻟﻤﺤﻮﻝ‬ ‫ﺍﻟﺜﺎﻧﻮﻱ‬‫ﺍﻟﻜﺒﻴﺮ‬ ‫ﺍﻟﻤﻐﻨﺎﻃﻴﺴﻲ‬ ‫ﻟﻠﻔﻴﺾ‬ ‫ﺍﻟﻤﻀﺎﺩ‬ ‫ﺍﻟﺘﺄﺛﻴﺮ‬ ‫ﻣﻌﻪ‬ ‫ﻭﻳﻨﻌﺪﻡ‬ ٬‫ﻳﻨﻌﺪﻡ‬ ‫ﺍﻟﺜﺎﻧﻮﻱ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻓﺈﻥ‬ ‫ﻣﻔﺘﻮﺣﺔ‬ ‫ﺑﻘﺎﺋﻬﺎ‬ ‫ﻣﻊ‬ ‫ﺑﺤﻤﻞ‬ ‫ﺎﺭ‬ ‫ﺍﻟﻌﺎﻟﻴﺔ‬ ‫ﺍﻟﻘﻴﻤﺔ‬ ‫ﺫﻱ‬ ‫ﺍﻻﺑﺘﺪﺍﺋﻲ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﻦ‬ ‫ﺍﻟﻨﺎﺗﺞ‬)ً‫ﺍ‬‫ﺟﺪ‬ ‫ﺍﻟﻌﺎﻟﻴﺔ‬ ‫ﺃﻭ‬.(‫ﺍﻟﺜﺎﻧﻮﻱ‬ ‫ﻃﺮﻓﻲ‬ ‫ﺑﻴﻦ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻓﺮﻕ‬ ‫ﻳﺮﺗﻔﻊ‬ ‫ﻭﺣﻴﻨﺌﺬ‬)‫ﺍﻟﻤﻔﺘﻮﺣﻴﻦ‬(‫ﺇﻟﻰ‬ ‫ﺍﻟﺬﻱ‬ ‫ﺍﻟﺤﺪ‬ ‫ﺇﻟﻰ‬ ‫ﺗﺼﻞ‬ ‫ﻗﺪ‬ ً‫ﺍ‬‫ﺟﺪ‬ ‫ﻛﺒﻴﺮﺓ‬ ‫ﻣﺴﺘﻮﻳﺎﺕ‬‫ﺗﺤﺘﻮﻱ‬ ‫ﺍﻟﺘﻲ‬ ‫ُﻌﺪﺓ‬‫ﻤ‬‫ﻟﻠ‬ ‫ﺃﻭ‬ ‫ﻣﻌﻪ‬ ‫ﺍﻟﻤﺘﻌﺎﻣﻞ‬ ‫ﻟﻠﺸﺨﺺ‬ ‫ﺃﻭ‬ ‫ﺍﻟﻤﺤﻮﻝ‬ ‫ﻣﻦ‬ ٍ‫ﻞ‬‫ﻟﻜ‬ ‫ﻛﺒﻴﺮﺓ‬ ‫ﻣﺨﺎﻃﺮ‬ ‫ﻳﺴﺒﺐ‬ ‫ﻟﻪ‬ ‫ﺍﻟﻤﺠﺎﻭﺭﺓ‬ ‫ﺃﻭ‬ ‫ﺍﻟﻤﺤﻮﻝ‬.‫ﻣﻦ‬ ‫ﺗﺴﺒﺒﻪ‬ ‫ﺑﻤﺎ‬ ‫ﺍﻟﻤﻐﻨﺎﻃﻴﺴﻲ‬ ‫ﻟﻠﻔﻴﺾ‬ ً‫ﺍ‬‫ﺟﺪ‬ ‫ﺍﻟﻌﺎﻟﻴﺔ‬ ‫ﺑﺎﻟﻘﻴﻤﺔ‬ ‫ﺍﻟﺤﺎﻟﺔ‬ ‫ﻫﺬﻩ‬ ‫ﻓﻲ‬ ‫ﻟﻠﻤﺤﻮﻝ‬ ‫ﺍﻟﺤﺪﻳﺪﻱ‬ ‫ﺍﻟﻘﻠﺐ‬ ‫ﻳﺘﺄﺛﺮ‬ ‫ﻛﻤﺎ‬ ‫ﻣ‬ ‫ﺍﻟﻨﺎﺗﺠﺔ‬ ‫ﺍﻟﺤﺮﺍﺭﺓ‬ ‫ﻣﻦ‬ ‫ﻋﺎﻟﻴﺔ‬ ‫ﻣﺴﺘﻮﻳﺎﺕ‬ ‫ﻭﻛﺬﻟﻚ‬ ‫ﺍﻟﺸﺪﻳﺪ‬ ‫ﻟﻠﺘﺸﺒﻊ‬ ‫ﺗﻌﺮﺿﻪ‬‫ﺍﻟﻤﻐﻨﺎﻃﻴﺴﻲ‬ ‫ﻭﺍﻟﺘﺨﻠﻒ‬ ‫ﺍﻟﺪﻭﺍﻣﻴﺔ‬ ‫ﺍﻟﺘﻴﺎﺭﺍﺕ‬ ‫ﻦ‬. __________________________________________________________________ ‫ﻣﺼﻄﻠﺢ‬ ‫ﻫﻮ‬ ‫ﻣﺎ‬BURDEN‫؟؟‬ ‫ﻛﻠﻤﺔ‬BURDEN‫ﻣ‬ ‫ﻭﻫﻲ‬‫ﺼ‬‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺛﺎﻧﻮﻱ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﻤﻮﺻﻠﺔ‬ ‫ﻭﺍﻟﻮﻗﺎﻳﺔ‬ ‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﺩﻭﺍﺋﺮ‬ ‫ﺣﻤﻞ‬ ‫ﻋﻦ‬ ‫ﻳﻌﺒﺮ‬ ‫ﻄﻠﺢ‬.‫ﺍﻝ‬ ‫ﺗﻘﺎﺱ‬ ‫ﻭ‬ BURDEN‫ﺑﺎﻝ‬Volt Ampere‫ﻣﺤﻮﻝ‬ ‫ﺍﻟﻤﺜﺎﻝ‬ ‫ﺳﺒﻴﻞ‬ ‫ﻓﻌﻠﻰ‬ ‫ﺍﻵﺧﺮ‬ ‫ﺑﺪﻻﻟﺔ‬ ‫ﺃﺣﺪﻫﻤﺎ‬ ‫ﺇﺳﺘﻨﺘﺎﺝ‬ ‫ﻭﻳﻤﻜﻦ‬ ‫ﻣﺘﻜﺎﻓﺌﺎﻥ‬ ‫ﻭﻟﻜﻨﻬﻤﺎ‬ ‫ﺑﺎﻷﻭﻡ‬ ‫ﻭﻟﻴﺲ‬ ‫ﻳﺘﺤﻤﻞ‬ ‫ﺍﻟﺬﻯ‬ ‫ﺍﻟﺘﻴﺎﺭ‬burden‫ﻗﺪﺭﻩ‬12.5 VA‫ﻳﺴﺎﻭﻯ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻄﺒﻴﻌﻰ‬ ‫ﻭﺗﻴﺎﺭﻩ‬5A‫ﺗﻮﺻﻴﻞ‬ ‫ﺗﺤﻤﻞ‬ ‫ﺍﻟﻮﺍﻗﻊ‬ ‫ﻓﻰ‬ ‫ﻳﻤﻜﻨﻪ‬Burden ‫ﻗﺪﺭﻩ‬ ZB = P/ I^2 = 12.5 / 25 = 0.5 Ω ‫ﺍﻝ‬ ‫ﻋﻠﻰ‬ ‫ﺗﻜﺘﺐ‬ ‫ﻣﺎ‬ ‫ﻭﺩﺍﺋﻤﺎ‬Name Plate‫ﻣﺜﻞ‬ ‫ﻛﺮﻗﻢ‬15 VA‫ﺍﻭ‬30 VA‫ﺍﻝ‬ ‫ﺭﻗﻢ‬ ‫ﺑﺠﻮﺍﺭﻫﺎ‬ ‫ﻳﺬﻛﺮ‬ ‫ﻣﺎ‬ ‫ﺩﺍﺋﻤﺎ‬ ‫ﻭ‬Accuracy‫ﻣﺜﻞ‬ 5P20‫ﻣﺜﻼ‬ ‫ﺍﻭ‬ ‫ﻭﻗﺎﻳﺔ‬ ‫ﺩﺍﺋﺮﺓ‬ ‫ﻛﺎﻧﺖ‬ ‫ﺍﺫﺍ‬Cl 0.5‫ﻗﻴﺎﺱ‬ ‫ﺩﺍﺋﺮﺓ‬ ‫ﻛﺎﻧﺖ‬ ‫ﺍﺫﺍ‬ ‫ﻳﻤﺜﻞ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺟﻬﺎﺯ‬ ‫ﻛﺎﻥ‬ ‫ﻭﻛﻠﻤﺎ‬low burden‫ﺍ‬ ‫ﻫﺬﻩ‬ ‫ﻓﻰ‬ ‫ﻧﺤﺘﺎﺝ‬ ‫ﻟﻦ‬ ‫ﻷﻧﻨﺎ‬ ‫ﺃﻓﻀﻞ‬ ‫ﺫﻟﻚ‬ ‫ﻛﺎﻥ‬ ‫ﻛﻠﻤﺎ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻋﻠﻰ‬‫ﺫﻯ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺇﻟﻰ‬ ‫ﻟﺤﺎﻟﻪ‬ ‫ﻋﺎﻟﻴﻪ‬ ‫ﻗﺪﺭﻩ‬.‫ﺗﻤﺜﻞ‬ ‫ﻷﻧﻬﺎ‬ ‫ﺍﻟﺮﻗﻤﻴﻪ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﻷﺟﻬﺰﺓ‬ ‫ﺍﻟﻌﺪﻳﺪﻩ‬ ‫ﺍﻟﻤﻴﺰﺍﺕ‬ ‫ﺇﺣﺪﻯ‬ ‫ﻭﻫﺬﻩ‬Low Burden‫ﺍﻟﺘﻘﻠﻴﺪﻳﻪ‬ ‫ﺍﻷﺟﻬﺰﺓ‬ ‫ﺑﺄﻧﻮﺍﻉ‬ ‫ﻣﻘﺎﺭﻧﺔ‬ )Electromagnetic or static relays. ( ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺟﻬﺎﺯ‬ ‫ﻣﻌﺎﻭﻗﺔ‬ ‫ﻗﻴﻤﺔ‬ ‫ﺍﻟﺘﺎﻟﻰ‬ ‫ﺍﻟﺸﻜﻞ‬ ‫ﻭﻳﻮﺿﺢ‬/‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺗﺸﺒﻊ‬ ‫ﺇﺣﺘﻤﺎﻟﻴﺔ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﻘﻴﺎﺱ‬٬‫ﺍﻟﺠﻬﺎﺯ‬ ‫ﻣﻘﺎﻭﻣﺔ‬ ‫ﺯﺍﺩﺕ‬ ‫ﻓﻜﻠﻤﺎ‬٬‫ﻛﻠﻤﺎ‬ ‫ﺃﻃﺮﺍﻓﻪ‬ ‫ﺑﻴﻦ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺯﺍﺩ‬٬‫ﻳﺘﺸﺒﻊ‬ ‫ﺃﻥ‬ ‫ﻭﺷﻚ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺃﻥ‬ ‫ﻳﻌﻨﻰ‬ ‫ﻭﻫﺬﺍ‬ ‫ﺍﻹﻧﻘﻼﺏ‬ ‫ﻧﻘﻄﺔ‬ ‫ﻣﻦ‬ ‫ﺇﻗﺘﺮﺏ‬ ‫ﻛﻠﻤﺎ‬.
10. 10. ۱٤٦ ­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­ ‫ﺍﻟﺤﻤﺎﻳﻪ‬ ‫ﻓﻲ‬ ‫ﺍﻟﻤﺴﺘﺨﺪﻣﻪ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﻋﻦ‬ ‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﻓﻲ‬ ‫ﺍﻟﻤﺴﺘﺨﺪﻡ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺑﻴﻦ‬ ‫ﺍﻟﻔﺮﻕ‬ ‫ﻣﺎﻫﻮ‬‫؟‬ ‫ﺍﻟﻄﺒﻴﻌﻲ‬ ‫ﺍﻟﺤﻤﻞ‬ ‫ﺣﺎﻻﺕ‬ ‫ﻓﻲ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻗﻴﺎﺱ‬ ‫ﻫﻮ‬ ‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﺑﺄﺟﻬﺰﺓ‬ ‫ﺍﻟﺨﺎﺻﺔ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﻭﻇﻴﻔﺔ‬ ‫ﺍﻷﻋﻄﺎﻝ‬ ‫ﺧﻼﻝ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻗﻴﺎﺱ‬ ‫ﻓﻮﻇﻴﻔﺘﻬﺎ‬ ‫ﺍﻟﺤﻤﺎﻳﻪ‬ ‫ﺑﺄﺟﻬﺰ‬ ‫ﺍﻟﺨﺎﺻﺔ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺃﻣﺎ‬ ‫ﺍﻟ‬ ‫ﻣﻨﺤﻨﻲ‬ ‫ﻓﺈﻥ‬ ‫ﻭﻋﻠﻴﻪ‬‫ﻋﻨﺪ‬ ً‫ﺎ‬‫ﻧﺴﺒﻴ‬ ‫ﻋﺎﻟﻴﻪ‬ ‫ﺑﺪﻗﻪ‬ ‫ﺧﻄﻲ‬ ‫ﺑﻤﻨﺤﻨﻲ‬ ‫ﺗﺘﻤﻴﺰ‬ ‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﻓﻤﺤﻮﻻﺕ‬ ‫ﻭﻇﻴﻔﺘﻬﺎ‬ ‫ﻋﻠﻰ‬ ‫ﺗﻌﺘﻤﺪ‬ ‫ﺍﻟﻤﺤﻮﻻﺕ‬ ‫ﻟﻬﺬﻩ‬ ‫ﻤﻐﻨﻄﺔ‬ ‫ﺍﻟﻤﻨﺤﻨﻰ‬ ‫ﻋﺮﻭﺓ‬ ‫ﻭﺗﻜﻮﻥ‬ ‫ﺍﻟﺼﻐﻴﺮﻩ‬ ‫ﺍﻟﺘﻴﺎﺭﺍﺕ‬)KNEE POINT(‫ﻟﻬﺬﻩ‬ ‫ﺍﻟﺤﺪﻳﺪﻱ‬ ‫ﻟﻠﻘﻠﺐ‬ ‫ﺍﺷﺒﺎﻉ‬ ‫ﻳﺤﺪﺙ‬ ‫ﺃﻱ‬ ‫ﻣﻨﺨﻔﻀﻪ‬ ‫ﺍﻟﻤﺤﻮﻻﺕ‬ ‫ﻟﻬﺬﻩ‬ ‫ﺍﻷﻋﻄﺎﻝ‬ ‫ﺣﺎﻟﺔ‬ ‫ﻓﻲ‬ ‫ﺍﻟﻤﺤﻮﻻﺕ‬. ‫ﻏﻴ‬ ‫ﺑﻤﻨﺤﻨﻲ‬ ‫ﻓﺘﻤﺘﺎﺯ‬ ‫ﺍﻟﺤﻤﺎﻳﻪ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺃﻣﺎ‬‫ﻋﺮﻭﺓ‬ ‫ﻭﺗﻜﻮﻥ‬ ‫ﺍﻟﻌﺎﻟﻴﺔ‬ ‫ﺍﻟﺘﻴﺎﺭﺍﺕ‬ ‫ﻋﻨﺪ‬ ‫ﺧﻄﻲ‬ ‫ﻣﻨﺤﻨﻲ‬ ‫ﻭ‬ ً‫ﺎ‬‫ﻧﺴﺒﻴ‬ ‫ﺍﻟﺼﻐﻴﺮﻩ‬ ‫ﺍﻟﺘﻴﺎﺭﺍﺕ‬ ‫ﻋﻨﺪ‬ ‫ﺧﻄﻲ‬ ‫ﺮ‬ ‫ﺍﻟﻤﻨﺤﻨﻰ‬)KNEE POINT(‫ﺍﻷﻋﻄﺎﻝ‬ ‫ﺣﺎﻟﺔ‬ ‫ﻓﻲ‬ ‫ﺍﻟﻤﺤﻮﻻﺕ‬ ‫ﻟﻬﺬﻩ‬ ‫ﺍﻟﺤﺪﻳﺪﻱ‬ ‫ﻟﻠﻘﻠﺐ‬ ‫ﺍﺷﺒﺎﻉ‬ ‫ﻳﺤﺪﺙ‬ ‫ﻻ‬ ‫ﺃﻳﺄﻧﻪ‬ ‫ﻣﺮﺗﻔﻌﻪ‬ ‫ﺍﻟﻤﺤﻮﻻﺕ‬ ‫ﻟﻬﺬﻩ‬. ‫ﺍﻟﻨﻮﻋﻴﻦ‬ ‫ﺑﻴﻦ‬ ‫ﻣﻘﺎﺭﻧﻪ‬ ‫ﻭﻫﺬﻩ‬ ‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﻣﻊ‬ ‫ﺍﻟﻤﺴﺘﺨﺪﻡ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬‫ﻣﺤﻮﻝ‬‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﻣﻊ‬ ‫ﺍﻟﻤﺴﺘﺨﺪﻡ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ *‫ﻣﻦ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﺣﺪﻭﺩ‬5%‫ﺇﻟﻰ‬120%‫ﺍﻟﻤﻘﻨﻦ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻗﻴﻤﺔ‬ ‫ﻣﻦ‬. *‫ﻋﺎﻟﻴﻪ‬ ‫ﺩﻗﻪ‬ ‫ﺩﺭﺟﺔ‬ ‫ﺫﻭ‬. *‫ﺻﻐﻴﺮﻩ‬ ‫ﺍﻟﻤﺤﻮﻝ‬ ‫ﺧﺮﺝ‬ ‫ﻗﺪﺭﺓ‬. *‫ﺻﻐﻴﺮ‬ ‫ﺍﻟﺘﺸﺒﻊ‬ ‫ﺟﻬﺪ‬Low Saturation Voltage *‫ﺍﻟﻤﻘﻨﻦ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﻦ‬ ‫ﺃﻛﺒﺮ‬ ‫ﻗﻴﻢ‬ ‫ﻋﻨﺪ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﺣﺪﻭﺩ‬. *‫ﻣﻨﺨﻔﻀﻪ‬ ‫ﺩﻗﻪ‬ ‫ﺩﺭﺟﺔ‬ ‫ﺫﻭ‬)‫ﻣﺴﻤﻮﺡ‬‫ﻣﻦ‬ ‫ﺃﻛﺒﺮ‬ ‫ﺗﺤﻮﻳﻞ‬ ‫ﻧﺴﺒﺔ‬ ‫ﺑﺨﻄﺄ‬ ‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﻓﻰ‬ ‫ﺑﻬﺎ‬ ‫ﺍﻟﻤﺴﻤﻮﺡ‬ ‫ﺍﻟﻨﺴﺒﻪ‬. ( *‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﺩﻭﺍﺋﺮ‬ ‫ﻓﻰ‬ ‫ﺗﺴﺘﺨﺪﻡ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺗﻠﻚ‬ ‫ﻣﻦ‬ ‫ﺃﻛﺒﺮ‬ ‫ﺍﻟﻤﺤﻮﻝ‬ ‫ﻣﺨﺮﺝ‬ ‫ﻗﺪﺭﺓ‬
11. 11. ۱٤۷ . *‫ﻋﺎﻟﻰ‬ ‫ﺍﻟﺘﺸﺒﻊ‬ ‫ﺟﻬﺪ‬High Saturation Voltage ­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­ ­­­­ ‫؟‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻣﻮﺍﺻﻔﺎﺕ‬ ‫ﺃﻫﻢ‬ ‫ﻣﺎ‬ ‫ﻳﻠﻰ‬ ‫ﻣﺎ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻣﻊ‬ ‫ﺑﺪﻗﻪ‬ ‫ﺗﻮﺻﻴﻔﻬﺎ‬ ‫ﻳﺠﺐ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺍﻟﻜﻤﻴﺎﺕ‬ ‫ﺃﻫﻢ‬ ‫ﻣﻦ‬: ­‫ﺍﻟﺤﻤﻞ‬Rated Burden‫ﻋﻠﻰ‬ ‫ﺩﺍﺋﻤﺔ‬ ‫ﺑﺼﻔﺔ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺃﻭ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﻋﻠﻰ‬ ‫ﺗﺤﻤﻴﻠﻬﺎ‬ ‫ﻳﻤﻜﻦ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺃﻣﺒﻴﺮ‬ ‫ﺑﺎﻟﻔﻮﻟﺖ‬ ‫ﺍﻟﻘﺪﺭﺓ‬ ‫ﻫﻰ‬‫ﺃﻥ‬ ‫ﺍﻟﺤﺪﻭﺩ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻮﺟﻪ‬ ‫ﻭﺯﺍﻭﻳﺔ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺨﻄﺄ‬ ‫ﻗﻴﻤﺔ‬ ‫ﺗﻈﻞ‬‫ﻟﻠﻤﺤﻮﻻﺕ‬ ‫ﺍﻟﺪﻗﺔ‬ ‫ﻣﺴﺘﻮﻯ‬ ‫ﺣﺴﺐ‬ ‫ﺑﻬﺎ‬ ‫ﺍﻟﻤﺴﻤﻮﺡ‬‫ﺑﺎﻟـ‬ ‫ﺗﻘﺎﺱ‬ ‫ﻭﻫﻰ‬VA ‫ﺍﻟﻤﺴﺘﺨﺪﻣﻪ‬ ‫ﺍﻟﻘﻴﻢ‬ ‫ﺃﺷﻬﺮ‬ ‫ﻭﻣﻦ‬) :2.5 , 5 , 7.5 , 10 , 15 , 30 VA( ­‫ﻳﺘﺤﻤﻠﻪ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺃﻗﺼﻰ‬Continous Rated Current:‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﺠﺎﻧﺐ‬ ‫ﻓﻰ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺃﻗﺼﻰ‬ ‫ﺇﻟﻰ‬ ‫ﻳﺸﺎﺭ‬ ‫ﻭﻏﺎﻟﺒﺎ‬. ­‫ﻭﺟﻴﺰﻩ‬ ‫ﻣﺪﻩ‬ ‫ﻓﻰ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺃﻗﺼﻰ‬nt & duration timeShort circuit curre:‫ﻭﻏﺎﻟﺒﺎ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺇﻟﻰ‬ ‫ﻳﺸﺎﺭ‬ ‫ﻭﻏﺎﻟﺒﺎ‬ ‫ﺛﻮﺍﻧﻰ‬ ‫ﻭﺛﻼﺙ‬ ‫ﺛﺎﻧﻴﻪ‬ ‫ﻧﺼﻒ‬ ‫ﺑﻴﻦ‬ ‫ﺗﺘﺮﺍﻭﺡ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺃﻗﺼﻰ‬ ‫ﻋﻠﻴﻬﺎ‬ ‫ﺍﻟﻤﺤﺴﻮﺏ‬ ‫ﺍﻟﻤﺪﻩ‬ ‫ﺗﻜﻮﻥ‬. ­‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺗﻴﺎﺭ‬Rated:‫ﻳﻜﻮﻥ‬ ‫ﻭﻏﺎﻟﺒﺎ‬1‫ﺃﻭ‬2‫ﺃﻭ‬5‫ﺃﻣﺒﻴﺮ‬.‫ﻋﻦ‬ ‫ﺍﻟﺤﻤﺎﻳﻪ‬ ‫ﺟﻬﺎﺯ‬ ‫ﻭﺑﻴﻦ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺑﻴﻦ‬ ‫ﺍﻟﻤﺴﺎﻓﻪ‬ ‫ﺯﺍﺩﺕ‬ ‫ﺇﺫﺍ‬ ‫ﻭﻏﺎﻟﺒﺎ‬ 30‫ﻳﺴﺎﻭﻯ‬ ‫ﺛﺎﻧﻮﻳﺎ‬ ‫ﺗﻴﺎﺭﺍ‬ ‫ﻧﺴﺘﺨﺪﻡ‬ ‫ﻓﺈﻧﻨﺎ‬ ‫ﻣﺘﺮ‬1A. ­‫ﺍﻟﺘﺤﻮﻳﻞ‬ ‫ﻧﺴﺒﺔ‬Turns ratio:‫ﻋﻤﻠﻴﺎ‬ ‫ﻭﺃﻗﺼﺎﻫﺎ‬3000/1‫ﺫﻟﻚ‬ ‫ﻣﻦ‬ ‫ﺃﺻﻐﺮ‬ ‫ﻗﻴﻢ‬ ‫ﺑﺎﻟﻄﺒﻊ‬ ‫ﻭﻫﻨﺎﻙ‬. ­‫ﺍﻟـ‬Class:‫ﺍﻟﻤﺤﻮﻝ‬ ‫ﺑﻬﺎ‬ ‫ﻳﻮﺻﻒ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺍﻟﻘﻴﻢ‬ ‫ﻭﺃﺷﻬﺮ‬ ‫ﺃﻫﻢ‬ ‫ﻣﻦ‬ ‫ﻭﺗﻌﺘﺒﺮ‬. ‫ﺍﻟـ‬ ‫ﺃﺷﻬﺮ‬ ‫ﻭﻣﻦ‬Classes‫ﻫﻰ‬ ‫ﻓﻘﻂ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻤﺴﺘﺨﺪﻣﻪ‬10P , 5p‫ﺍﻟـ‬ ‫ﺇﻟﻰ‬ ‫ﺑﺎﻹﺿﺎﻓﻪ‬Class X‫ﺃﺟﻬﺰﺓ‬ ‫ﻣﻊ‬ ‫ﻳﺴﺘﺨﺪﻡ‬ ‫ﺍﻟﺬﻯ‬ ‫ﺍﻟﺒﺮﻳﻄﺎﻧﻴﻪ‬ ‫ﻟﻠﻤﻮﺍﺻﻔﺎﺕ‬ ‫ﻃﺒﻘﺎ‬ ‫ﻭﺫﻟﻚ‬ ‫ﺍﻟﺘﻔﺎﺿﻠﻴﻪ‬ ‫ﺍﻟﻮﻗﺎﻳﻪ‬BS.‫ﻳﺴﺘﺨﺪﻡ‬ ‫ﻭﻏﺎﻟﺒﺎ‬Class 5P‫ﻣﻊ‬Instantenous OC relays ‫ﻳﺴﺘﺨﺪﻡ‬ ‫ﺑﻴﻨﻤﺎ‬Class 10P‫ﺍﻟـ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﻣﻊ‬overcurrent‫ﺑـ‬ ‫ﺍﻟﻤﻌﺮﻭﻑ‬ ‫ﺍﻟﻨﻮﻉ‬ ‫ﻣﻦ‬IDMT٬‫ﺍﻟﻤ‬ ‫ﺍﻟﺪﻗﻪ‬ ‫ﻛﺎﻧﺖ‬ ‫ﻛﻠﻤﺎ‬ ‫ﺃﻧﻪ‬ ‫ﺑﻤﻌﻨﻰ‬‫ﻄﻠﻮﺑﻪ‬ ‫ﺍﻟـ‬ ‫ﺗﻤﻴﺰﺕ‬ ‫ﻛﻠﻤﺎ‬ ‫ﻋﺎﻟﻴﻪ‬Class‫ﺃﺻﻐﺮ‬ ‫ﺑﺮﻗﻢ‬ ‫ﺍﻟﻤﺴﺘﺨﺪﻣﻪ‬٬‫ﺑـ‬ ‫ﻓﻴﻬﺎ‬ ‫ﻓﻴﻜﺘﻔﻰ‬ ‫ﻋﺎﻟﻴﻪ‬ ‫ﻟﺪﻗﻪ‬ ‫ﺗﺤﺘﺎﺝ‬ ‫ﻻ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺍﻟﺘﻄﺒﻴﻘﺎﺕ‬ ‫ﺃﻣﺎ‬Class X ­Accuracy limit Factor ALF:‫ﻓﻰ‬ ‫ﺍﻟﻘﺮﺍءﻩ‬ ‫ﺩﻗﺔ‬ ‫ﺗﺘﺄﺛﺮ‬ ‫ﺃﻥ‬ ‫ﺩﻭﻥ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﺠﺎﻧﺐ‬ ‫ﻓﻰ‬ ‫ﻳﻤﺮ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺃﻗﺼﻰ‬ ‫ﻋﻦ‬ ‫ﺗﻌﺒﺮ‬ ‫ﻗﻴﻤﻪ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﺠﺎﻧﺐ‬٬‫ﺗ‬ ‫ﺃﻗﺼﻰ‬ ‫ﺁﺧﺮ‬ ‫ﺑﻤﻌﻨﻰ‬‫ﺍﻟﻘﻠﺐ‬ ‫ﻳﺘﺸﺒﻊ‬ ‫ﺃﻥ‬ ‫ﻗﺒﻞ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﻓﻰ‬ ‫ﻳﻤﺮ‬ ‫ﻴﺎﺭ‬٬‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻭﻳﺘﺸﻮﻩ‬. ‫ﺗﺤﻮﻳﻞ‬ ‫ﻧﺴﺒﺔ‬ ‫ﻟﻪ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺃﻥ‬ ‫ﻟﻮ‬ ‫ﺍﻟﻤﺜﺎﻝ‬ ‫ﺳﺒﻴﻞ‬ ‫ﻋﻠﻰ‬200/1‫ﻗﻴﻤﺔ‬ ‫ﻭﻛﺎﻧﺖ‬ALF = 5٬‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﻟﺘﻴﺎﺭ‬ ‫ﻗﻴﻤﻪ‬ ‫ﺃﻗﺼﻰ‬ ‫ﺃﻥ‬ ‫ﻳﻌﻨﻰ‬ ‫ﻓﻬﺬﺍ‬ ‫ﺗﺴﺎﻭﻯ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻓﻰ‬ ‫ﺗﺸﻮﻩ‬ ‫ﻳﺤﺪﺙ‬ ‫ﺃﻥ‬ ‫ﺩﻭﻥ‬200*5 = 1000. ‫ﻋﻠﻰ‬ ‫ﺗﻌﺘﻤﺪ‬ ‫ﻭﺍﻟﺘﻰ‬ ‫ﺟﺪﺍ‬ ‫ﺍﻟﻤﻔﻴﺪﻩ‬ ‫ﺍﻟﺼﻴﻎ‬ ‫ﻭﻣﻦ‬ALF‫ﺍﻟﻤﻌﺎﺩﻟﻪ‬ ‫ﻓﻰ‬ ‫ﺗﻈﻬﺮ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺗﻠﻚ‬)2­2(‫ﻃﺮﻓﻰ‬ ‫ﺑﻴﻦ‬ ‫ﻳﻨﺸﺄ‬ ‫ﺟﻬﺪ‬ ‫ﺃﻗﺼﻰ‬ ‫ﻗﻴﻤﺔ‬ ‫ﺗﺤﺪﺩ‬ ‫ﻭﺍﻟﺘﻰ‬ ‫ﺍﻟـ‬CT‫ﺍﻟـ‬ ‫ﺑﺪﻻﻟﺔ‬ALF: ‫ﺍﻟـ‬ ‫ﻟﻘﻴﻤﺔ‬ ‫ﻗﺮﻳﺒﻪ‬ ‫ﻗﻴﻤﻪ‬ ‫ﺗﻌﻄﻰ‬ ‫ﻭﻫﻰ‬VK‫ﺍﻟﻤﻌﺎﺩﻟﻪ‬ ‫ﻣﻦ‬ ‫ﻭﺣﺴﺒﻨﺎﻫﺎ‬ ‫ﺳﺒﻖ‬ ‫ﻭﺍﻟﺘﻰ‬)1­2(‫ﺍﻟﻤﻌﺎﺩﻟﻪ‬ ‫ﺃﻥ‬ ‫ﻣﻼﺣﻈﺔ‬ ‫ﻣﻊ‬)1­2(‫ﻳﺪﻻﻟﺔ‬ ‫ﻛﺎﻧﺖ‬ Bmax‫ﺍﻟﺘﻘﺮﻳﺒﻴﻪ‬ ‫ﺍﻟﻤﻌﺎﺩﻟﻪ‬ ‫ﻫﺬﻩ‬ ‫ﻗﻴﻤﺔ‬ ‫ﺟﺎءﺕ‬ ‫ﻫﻨﺎ‬ ‫ﻭﻣﻦ‬ ‫ﻣﻌﺮﻓﺘﻬﺎ‬ ‫ﺃﻭ‬ ‫ﺣﺴﺎﺑﻬﺎ‬ ‫ﻳﺴﻬﻞ‬ ‫ﻻ‬ ‫ﺑﻘﻴﻤﻪ‬ ‫ﻭﻫﻰ‬. ­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­ ‫ﺍﻟﺘﺎﻟﻰ‬ ‫ﺑﺎﻟﺮﻣﺰ‬ ‫ﺍﻟﻤﻘﺼﻮﺩ‬ ‫ﻣﺎ‬100/1٬5P10٬30 VA‫؟‬ 100/1)(‫ﺍﻟﺘﺤﻮﻳﻞ‬ ‫ﻧﺴﺒﺔ‬ ‫ﻫﻰ‬Turns ratio 5P10)(‫ﺍﻟﺤﺮﻑ‬ ‫ﻳﺴﺎﺭ‬ ‫ﻋﻠﻰ‬ ‫ﻳﻈﻬﺮ‬ ‫ﺍﻟﺬﻯ‬ ‫ﻭﺍﻟﺮﻗﻢ‬ ‫ﻟﻠﻮﻗﺎﻳﻪ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﺃﻧﻪ‬ ‫ﺗﻌﻨﻰ‬P‫ﺭﻗﻢ‬ ‫ﻭﻫﻮ‬5‫ﻣﺴﺘﻮﻯ‬ ‫ﻳﻌﻨﻰ‬‫ﺍﻟﺪﻗﻪ‬Accuracy class‫ﺍﻟﺤﺮﻑ‬ ‫ﻳﻤﻴﻦ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺬﻯ‬ ‫ﻭﺍﻟﺮﻗﻢ‬P‫ﺍﻟﺪﻗﻪ‬ ‫ﺣﺪﻭﺩ‬ ‫ﺃﻗﺼﻰ‬ ‫ﻣﻌﺎﻣﻞ‬ ‫ﻳﻤﺜﻞ‬Accuracy limit Factor ALF )30 VA(‫ﺍﻟـ‬ ‫ﻫﻮ‬rated burden ‫ﺍﻟـ‬ ‫ﻫﺬﺍ‬ ‫ﺃﻥ‬ ‫ﺗﻌﻨﻰ‬ ‫ﺍﻟﻤﻌﻠﻮﻣﺎﺕ‬ ‫ﻫﺬﻩ‬CT‫ﻗﻴﺎﺱ‬ ‫ﺩﻗﺔ‬ ‫ﻟﻪ‬)‫ﺧﻄﺄ‬ ‫ﻧﺴﺒﺔ‬(‫ﻗﺪﺭﻫﺎ‬5%‫ﻗﺪﺭﻩ‬ ‫ﻣﺪﻯ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺪﻗﻪ‬ ‫ﻫﺬﻩ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﻤﺤﺎﻓﻈﻪ‬ ‫ﻭﻳﻤﻜﻨﻪ‬10 ‫ﻳﺴﺎﻭﻯ‬ ‫ﺍﻟﺬﻯ‬ ‫ﺍﻟﻄﺒﻴﻌﻰ‬ ‫ﺗﻴﺎﺭﻩ‬ ‫ﺃﻣﺜﺎﻝ‬1A‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﻓﻰ‬. ‫ﺁﺧﺮ‬ ‫ﺑﻤﻌﻨﻰ‬:‫ﺍﻟـ‬ ‫ﻫﺬﺍ‬ ‫ﺃﻥ‬CT‫ﺃﻗﺼﻰ‬ ‫ﺑﺤﺪ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺗﺤﻤﻞ‬ ‫ﻳﻤﻜﻨﻪ‬10 A‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﻓﻰ‬٬‫ﻳﻌﺎﺩ‬ ‫ﻭﻫﻮ‬‫ﻝ‬1000 A‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﻓﻰ‬٬‫ﺑﻘﺎء‬ ‫ﻣﻊ‬ ‫ﻋﻠﻴﻪ‬ ‫ﺍﻟﻤﻮﺻﻠﻪ‬ ‫ﺍﻷﺣﻤﺎﻝ‬ ‫ﺗﻜﻮﻥ‬ ‫ﺃﻥ‬ ‫ﺷﺮﻳﻄﺔ‬ ‫ﻟﻬﺎ‬ ‫ﺍﻟﻤﻘﺮﺭﻩ‬ ‫ﺍﻟﺤﺪﻭﺩ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺨﻄﺄ‬ ‫ﻧﺴﺒﺔ‬30 VA. ­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­ ‫ﻣﺤﻮﻻ‬ ‫ﻋﻠﻰ‬ ‫ﺇﺟﺮﺍﺅﻫﺎ‬ ‫ﻳﺠﺐ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺍﻷﺧﺘﺒﺎﺭﺍﺕ‬ ‫ﻫﻰ‬ ‫ﻣﺎ‬‫؟‬ ‫ﺍﻟﺨﺪﻣﻪ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺇﺩﺧﺎﻝ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺒﺪء‬ ‫ﻗﺒﻞ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﺕ‬ ۱­‫ﺍﻟﺘﺤﻮﻳﻞ‬ ‫ﻧﺴﺒﺔ‬ ‫ﺇﺧﺘﺒﺎﺭ‬Turns ratio:‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻭﻗﻴﺎﺱ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻓﻰ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺑﺈﻣﺮﺍﺭ‬ ‫ﻭﺫﻟﻚ‬ ۲­‫ﺍﻟﻘﻄﺒﻴﻪ‬ ‫ﺇﺧﺘﺒﺎﺭ‬Polarity test:‫ﺟﻬﺪﻫﺎ‬ ‫ﺑﻄﺎﺭﻳﻪ‬ ‫ﺑﺘﻮﺻﻴﻞ‬ ‫ﻭﺫﻟﻚ‬6 V‫ﻟﻠـ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻃﺮﻓﻰ‬ ‫ﺑﻴﻦ‬CT‫ﻓﻮﻟﺘﻤﻴﺘﺮ‬ ‫ﻭﺗﻮﺻﻴﻞ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﻃﺮﻓﻰ‬ ‫ﺑﻴﻦ‬٬‫ﺍﻟﻤﻮﺟﺒﻪ‬ ‫ﺍﻟﺠﻬﻪ‬ ‫ﺇﻟﻰ‬ ‫ﺍﻟﻔﻮﻟﺘﻤﻴﺘﺮ‬ ‫ﻣﺆﺷﺮ‬ ‫ﻳﻨﺤﺮﻑ‬ ‫ﺍﻟﺪﺍﺋﺮﻩ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺒﻄﺎﺭﻳﻪ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﻓﻌﻨﺪ‬٬‫ﺍﻟﺒﻄﺎﺭﻳﻪ‬ ‫ﻓﺼﻞ‬ ‫ﻭﻋﻨﺪ‬ ‫ﺍﻵﺧﺮ‬ ‫ﺍﻹﺗﺠﺎﻩ‬ ‫ﻓﻰ‬ ‫ﻳﻨﻌﻜﺲ‬٬‫ﺗﻜﻮﻥ‬ ‫ﻭﻋﻨﺪﻫﺎ‬S1‫ﺍﻟﻔﻮﻟﺘﻤﻴﺘﺮ‬ ‫ﻣﻮﺟﺐ‬ ‫ﺇﻟﻰ‬ ‫ﺍﻟﻤﻮﺻﻞ‬ ‫ﺍﻟﻄﺮﻑ‬ ‫ﻫﻰ‬.
12. 12. ۱٤۸ ‫ﻣﻠﺤﻮﻇﻪ‬:‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺗﻴﺎﺭ‬)‫ﻣﻦ‬S1‫ﺇﻟﻰ‬S2‫ﺍﻟﺪﺍﺋﺮﻩ‬ ‫ﻓﻰ‬‫ﺍﻟﺨﺎﺭﺟﻴﻪ‬(‫ﻣﻦ‬ ‫ﺍﻟﻤﺎﺭ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺇﺗﺠﺎﻩ‬ ‫ﻧﻔﺲ‬ ‫ﻓﻰ‬ ‫ﺩﺍﺋﻤﺎ‬ ‫ﻳﻜﻮﻥ‬P1‫ﺇﻟﻰ‬P2 ‫ﺍﻟﺸﻜﻞ‬ ‫ﻓﻰ‬ ‫ﻛﻤﺎ‬12­2.‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺇﺗﺠﺎﻩ‬ ‫ﻋﻜﺲ‬ ‫ﻓﻰ‬ ‫ﻳﺴﻴﺮ‬ ‫ﻧﻔﺴﻪ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﺃﻥ‬ ‫ﻻﺣﻆ‬. ۳­‫ﺍﻟﺘﺸﺒﻊ‬ ‫ﺇﺧﺘﺒﺎﺭ‬Saturation test:‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻓﻰ‬ ‫ﻳﻨﺸﺄ‬ ‫ﺍﻟﺬﻯ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻗﻴﺎﺱ‬ ‫ﻣﻊ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﻋﻠﻰ‬ ‫ﺟﻬﺪ‬ ‫ﺑﺘﺴﻠﻴﻂ‬ ‫ﻭﺫﻟﻚ‬ ‫ﺍﻹﺧﺘﺒﺎﺭ‬ ‫ﺃﺛﻨﺎء‬ ‫ﺣﻤﻞ‬ ‫ﺃﻯ‬ ‫ﺑﺪﻭﻥ‬ ‫ﻣﻔﺘﻮﺣﺎ‬ ‫ﻳﻈﻞ‬ ‫ﺍﻹﺑﺘﺪﺍﺋﻰ‬ ‫ﺍﻟﺠﺎﻧﺐ‬ ‫ﺑﺄﻥ‬ ‫ﻋﻠﻤﺎ‬. ‫ﺗﺪﺭﻳﺠﻴﺎ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺑﺰﻳﺎﺩﺓ‬ ‫ﺍﻹﺧﺘﺒﺎﺭ‬ ‫ﻭﻳﺒﺪﺃ‬‫ﺯﺍﺩ‬ ‫ﺇﺫﺍ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺍﻟﻨﻘﻄﺔ‬ ‫ﻣﻦ‬ ‫ﺗﺒﺪﺃ‬ ‫ﺍﻟﺘﻰ‬ ‫ﺍﻟﺘﺸﺒﻊ‬ ‫ﻣﺮﺣﻠﺔ‬ ‫ﺇﻟﻰ‬ ‫ﺗﺼﻞ‬ ‫ﺣﺘﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻗﻴﻤﺔ‬ ‫ﻭﻗﻴﺎﺱ‬‫ﻓﻴﻬﺎ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺑﻨﺴﺒﺔ‬۱۰%‫ﺑﻨﺴﺒﺔ‬ ‫ﻳﺰﻳﺪ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻤﻠﻒ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻓﺄﻥ‬٥۰%‫ﺯﻳﺎﺩﺓ‬ ‫ﺇﻟﻰ‬ ‫ﺗﺆﺩﻯ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻓﻰ‬ ‫ﺻﻐﻴﺮﺓ‬ ‫ﺯﻳﺎﺩﺓ‬ ‫ﺃﻯ‬ ‫ﻓﺎﻥ‬ ‫ﺍﻟﻨﻘﻄﺔ‬ ‫ﻫﺬﻩ‬ ‫ﻭﺑﻌﺪ‬ ‫ﺍﻟﺘﺸﺒﻊ‬ ‫ﻣﺮﺣﻠﺔ‬ ‫ﺍﻟﻤﺤﻮﻝ‬ ‫ﻳﺪﺧﻞ‬ ‫ﻭﺑﺬﻟﻚ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻓﻰ‬ ‫ﺟﺪﺍ‬ ‫ﻛﺒﻴﺮﺓ‬. ‫ﺍﻟﻘﺮﺍءﺍﺕ‬ ‫ﺗﺴﺠﻴﻞ‬ ‫ﻳﺒﺪﺃ‬ ‫ﻭﻋﻨﺪﺋﺬ‬:‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻗﻴﻢ‬ ‫ﻭﺗﺴﺠﻴﻞ‬ ‫ﺗﺪﺭﻳﺠﻴﺎ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻗﻴﻤﺔ‬ ‫ﺧﻔﺾ‬ ‫ﻓﻰ‬ ‫ﻧﺒﺪﺃ‬ ‫ﺣﻴﺚ‬‫ﺍﻟﺠﻬﺪ‬ ‫ﻗﻴﻢ‬ ‫ﻣﻦ‬ ‫ﻗﻴﻤﻪ‬ ‫ﻟﻜﻞ‬ ‫ﺍﻟﻤﻘﺎﺑﻠﻪ‬ ‫ﺣﺪﻭﺙ‬ ‫ﻣﻦ‬ ‫ﻟﻠﺘﺄﻛﺪ‬ ‫ﺍﻟﻨﻬﺎﻳﻪ‬ ‫ﻓﻰ‬ ‫ﺻﻔﺮ‬ ‫ﺇﻟﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻭﺻﻮﻝ‬ ‫ﻣﻦ‬ ‫ﻭﺍﻟﺘﺄﻛﺪ‬Demagnetization‫ﻣﻨﺤﻨﻰ‬ ‫ﺭﺳﻢ‬ ‫ﻳﻤﻜﻨﻚ‬ ‫ﻭﺍﻵﻥ‬ ‫ﻟﻠﻘﻠﺐ‬ ‫ﺍﻟﻤﻐﻨﺎﻃﻴﺴﻴﻪ‬. ٤­‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﻟﻠﻤﻠﻒ‬ ‫ﺍﻟﺪﺍﺧﻠﻴﻪ‬ ‫ﺍﻟﻤﻘﺎﻭﻣﻪ‬ ‫ﻗﻴﺎﺱ‬:‫ﻣﻘﺎﻭﻣﺔ‬ ‫ﻃﺮﻳﻖ‬ ‫ﻋﻦ‬ ‫ﻓﻴﻪ‬ ‫ﺍﻟﺘﺤﻜﻢ‬ ‫ﻳﻤﻜﻦ‬ ‫ﻣﺴﺘﻤﺮ‬ ‫ﺟﻬﺪ‬ ‫ﻣﺼﺪﺭ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﻃﺮﻳﻖ‬ ‫ﻋﻦ‬ ‫ﻭﺫﻟﻚ‬ ‫ﺍﻟﻤﻘﺎﻭﻣﺔ‬ ‫ﺑﺎﻟﻌﻼﻗﺔ‬ ‫ﺃﻭﻡ‬ ‫ﻗﺎﻧﻮﻥ‬ ‫ﺣﺴﺐ‬ ‫ﺍﻟﻤﻘﺎﻭﻣﺔ‬ ‫ﻭﺗﺤﺴﺐ‬ ‫ﺍﻟﻤﺴﺘﻤﺮ‬ ‫ﻭﺍﻟﺠﻬﺪ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻗﻴﻢ‬ ‫ﻭﻗﻴﺎﺱ‬ ‫ﺗﺪﺭﻳﺠﻴﺎ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺭﻓﻊ‬ ‫ﻭﻳﺘﻢ‬ ‫ﻣﺘﻐﻴﺮﺓ‬= ‫ﺍﻟﺠﻬﺪ‬ ‫ﻗﻴﻤﺔ‬ ‫ﻣﺘﻮﺳﻂ‬÷‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻗﻴﻤﺔ‬ ‫ﻣﺘﻮﺳﻂ‬ ٥­‫ﺍﻟﻤﻴﺠﺮ‬ ‫ﺑﻮﺍﺳﻄﺔ‬ ‫ﺍﻟﻌﺰﻝ‬ ‫ﺍﺧﺘﺒﺎﺭ‬۱۰۰۰‫ﻓﻮﻟﺖ‬:‫ﻋﻦ‬ ‫ﺍﻷﺭﺿﻰ‬ ‫ﻣﻊ‬ ‫ﺍﻟﺜﺎﻧﻮﻳﺔ‬ ‫ﻟﻠﻤﻠﻔﺎﺕ‬ ‫ﺍﻟﻌﺰﻝ‬ ‫ﻣﻘﺎﻭﻣﺔ‬ ‫ﺗﻘﻞ‬ ‫ﻭﻻ‬۱۰‫ﺗﻘﻞ‬ ‫ﻭﻻ‬ ‫ﺃﻭﻡ‬ ‫ﻣﻴﺠﺎ‬ ‫ﻋﻦ‬ ‫ﺍﻷﺭﺿﻰ‬ ‫ﻣﻊ‬ ‫ﺍﻻﺑﺘﺪﺍﺋﻴﺔ‬ ‫ﻟﻠﻤﻠﻔﺎﺕ‬ ‫ﺍﻟﻌﺰﻝ‬ ‫ﻣﻘﺎﻭﻣﺔ‬۲۰‫ﺃﻭﻡ‬ ‫ﻣﻴﺠﺎ‬ ٦­‫ﺍﻟﺜﺎﻧﻮﻳﺔ‬ ‫ﻟﻠﻤﻠﻔﺎﺕ‬ ‫ﺍﻻﺳﺘﻤﺮﺍﺭﻳﺔ‬ ‫ﻗﻴﺎﺱ‬)continuity( ­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­ ‫ﺣﻤﻮﻟﺔ‬ ‫ﻗﻴﺎﺱ‬ ‫ﻳﻤﻜﻦ‬ ‫ﻛﻴﻒ‬rated burden‫؟‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻟﻤﺤﻮﻻﺕ‬ ‫ﺍﻟﺜﺎﻧﻮﻳﺔ‬ ‫ﺍﻷﻃﺮﺍﻑ‬ ‫ﻓﺼﻞ‬ ‫ﻳﺘﻢ‬S2 , S1‫ﺃﻭ‬K , L‫ﺍﻟﺘﺤﻜﻢ‬ ‫ﻳﻤﻜﻦ‬ ‫ﺍﻟﻤﺘﺮﺩﺩ‬ ‫ﻟﻠﺠﻬﺪ‬ ‫ﻣﺼﺪﺭ‬ ‫ﺗﻮﺻﻴﻞ‬ ‫ﻭﻳﺘﻢ‬ ‫ﺭﻭﺯﺗﺔ‬ ‫ﺃﻗﺮﺏ‬ ‫ﻣﻦ‬ ‫ﻭﻧﻼﺣﻆ‬ ‫ﺗﺪﺭﻳﺠﻴﺎ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺭﻓﻊ‬ ‫ﻭﻳﺘﻢ‬ ‫ﺍﻟﻮﻗﺎﻳﺔ‬ ‫ﺃﺟﻬﺰﺓ‬ ‫ﺗﻐﺬﻯ‬ ‫ﻭﺍﻟﺘﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻟﻤﺤﻮﻻﺕ‬ ‫ﺍﻟﺜﺎﻧﻮﻳﺔ‬ ‫ﻟﻸﻃﺮﺍﻑ‬ ‫ﺍﻟﻤﻘﺎﺑﻠﺔ‬ ‫ﺍﻟﺘﻮﺻﻴﻞ‬ ‫ﻧﻘﻂ‬ ‫ﺇﻟﻰ‬ ‫ﻗﻴﻤﺘﻪ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻟﻤﺤﻮﻻﺕ‬ ‫ﺍﻟﺮﺍﺗﺒﺔ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻗﻴﻤﺔ‬ ‫ﺇﻟﻰ‬ ‫ﻧﺼﻞ‬ ‫ﺣﺘﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻗﻴﻢ‬In‫ﺍﻟ‬ ‫ﻗﻴﻤﺔ‬ ‫ﺗﺴﺠﻴﻞ‬ ‫ﻭﻳﺘﻢ‬‫ﻭﻳﺘﻢ‬ ‫ﻟﻬﺎ‬ ‫ﺍﻟﻤﻨﺎﻇﺮ‬ ‫ﺠﻬﺪ‬ ‫ﺍﻟﺤﻤﻮﻟﺔ‬ ‫ﺣﺴﺎﺏ‬=‫ﺍﻟﻤﻘﺎﺱ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻗﻴﻤﺔ‬)‫ﺍﻟﺮﺍﺗﺐ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺮﻭﺭ‬ ‫ﻋﻨﺪ‬(×‫ﻟﻠﻤﺤﻮﻝ‬ ‫ﺍﻟﺮﺍﺗﺐ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻟﺤﻤﻮﻟﺔ‬ ‫ﺍﻟﺮﺍﺗﺒﺔ‬ ‫ﺑﺎﻟﻘﻴﻤﺔ‬ ‫ﻭﺗﻘﺎﺭﻥ‬rated burden‫ﻋﻠﻴﻪ‬ ‫ﻭﺍﻟﻤﺪﻭﻧﺔ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­­ ‫ﺍﻟ‬ ‫ﺗﻮﺻﻴﻠﺔ‬ ‫ﻭﻇﻴﻔﺔ‬ ‫ﻫﻲ‬ ‫ﻣﺎ‬‫ـ‬Open delta‫؟‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻓﻰ‬ ‫ﺗﺴﺨﺪﻡ‬‫ﻻﺳﺘﺨﺪﺍﻣﺔ‬ ‫ﺍﻷﺭﺽ‬ ‫ﻭ‬ ‫ﺍﻷﻭﺟﻪ‬ ‫ﺍﺣﺪ‬ ‫ﺑﻴﻦ‬ ‫ﻗﺼﺮ‬ ‫ﺣﺪﻭﺙ‬ ‫ﺣﺎﻟﺔ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺼﻔﺮﻳﺔ‬ ‫ﺍﻟﻤﺮﻛﺒﺔ‬ ‫ﺟﻬﺪ‬ ‫ﻋﻠﻰ‬ ‫ﻟﻠﺤﺼﻮﻝ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﺯﻳﺎﺩﺓ‬ ‫ﻣﻦ‬ ‫ﺍﻟﻮﻗﺎﻳﺔ‬ ‫ﺍﻭ‬ ‫ﺍﻟﻤﺴﺎﻓﻴﺔ‬ ‫ﺍﻟﻮﻗﺎﻳﺔ‬ ‫ﻓﻰ‬ ‫ﺍﻟﻘﺼﺮ‬ ‫ﺗﻴﺎﺭ‬ ‫ﺍﺗﺠﺎﻩ‬ ‫ﻓﻯﺘﺤﺪﻳﺪ‬
13. 13. ۱٤۹ ۰ ‫ﻋﻨﺪﻩ‬ ‫ﻳﺤﺪﺙ‬ ‫ﺍﻟﺬﻱ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺣﺴﺎﺏ‬ ‫ﻳﻤﻜﻦ‬ ‫ﻫﻞ‬Knee Point‫ﺗﺴﺎﻭﻱ‬ ‫ﺣﺴﺎﺑﻴﺔ‬ ‫ﺑﻄﺮﻳﻘﺔ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻣﻌﺮﻓﺔ‬ ‫ﺍﻱ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻻﺕ‬ ‫ﻓﻲ‬ ‫ﺍﻟﺘﺸﺒﻊ‬ ‫ﻣﻨﺤﻨﻰ‬ ‫ﻣﻦ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺗﻘﺮﻳﺒﺎ‬     ‫ﺍﻝ‬ ‫ﺗﻌﺮﻳﻒ‬ ‫ﻭ‬ ‫ﺗﻮﺿﻴﺢ‬Knee Point ‫ﺍﻝ‬Knee Point‫ﻋﻨﺪﻫﺎ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺍﺯﺩﺍﺩ‬ ‫ﺍﺫﺍ‬ ‫ﺍﻟﺘﻲ‬ ‫ﺍﻟﻨﻘﻄﺔ‬ ‫ﻫﻲ‬۱۰%‫ﺑﻤﻘﺪﺍﺭ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻳﺰﺩﺍﺩ‬٥۰%‫ﺑﻌﺪ‬ ‫ﻭ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻓﻲ‬‫ﻳﺪﺧﻞ‬ ‫ﺍﻟﻨﻘﻄﺔ‬ ‫ﻫﺬﻩ‬ ‫ﺍﻟﺘﺸﺒﻊ‬ ‫ﻓﻲ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻝ‬ ‫ﺍﻟﺘﻘﺮﻳﺒﻲ‬ ‫ﺍﻟﺤﺴﺎﺏ‬Knee Point: ‫ﻛﺎﻟﺘﺎﻟﻲ‬ ‫ﺑﻴﺎﻧﺎﺗﻪ‬ ‫ﺗﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻋﻨﺪﻧﺎ‬ ‫ﻟﻮ‬: C.T.R = 300/5٬Is=5٬A , 5 P۱۰٬٦۰VA Knee Point=۱۰*٦۰/Is=۱۰*٦۰/٥=۱۲۰Volt Vcallculated = ( ALF*Rated burden ) / In where In = nominal secondary current   *******************************************************************   ‫ﺍﺳﺘﺨﺪﺍﻡ‬ ‫ﻋﻨﺪ‬current transformer‫ﻳﻘﻮﻡ‬ ‫ﺍﻟﻌﺎﻟﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺧﻄﻮﻁ‬ ‫ﻓﻰ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻟﻘﻴﺎﺱ‬c.t.‫ﻟﻴﺘﻢ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﺑﺨﻔﺾ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﻳﺰﺩﺍﺩ‬ ‫ﻻ‬ ‫ﻟﻤﺎﺫﺍ‬ ‫ﺍﺫﻥ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﻊ‬ ‫ﻋﻜﺴﻴﺎ‬ ‫ﻳﻨﺎﺳﺐ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺍﻥ‬ ‫ﻧﻌﺮﻑ‬ ‫ﻭﻧﺤﻦ‬ ‫ﺍﻟﻘﻴﺎﺱ‬ ‫ﺍﺟﻬﺰﺓ‬ ‫ﻋﻠﻰ‬ ‫ﺫﻟﻚ‬ ‫ﺑﻌﺪ‬ ‫ﺍﺩﺧﺎﻟﻪ‬ ‫ﻟﻠــ‬ ‫ﺍﻟﺜﺎﻧﻮﻯ‬ ‫ﺍﻟﻄﺮﻑ‬ ‫ﻋﻠﻰ‬c.t‫ﺍﻟﻰ‬ ‫ﻳﺼﻞ‬ ‫ﻗﺪ‬ ‫ﺍﻟﺨﻄﻮﻁ‬ ‫ﻫﺬﻩ‬ ‫ﻋﻠﻰ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺍﻥ‬ ‫ﻣﻦ‬ ‫ﺍﻟﺮﻏﻢ‬ ‫ﻋﻠﻰ‬٥۰۰kv‫؟‬    ‫ﻓﻴﻜ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺧﻂ‬ ‫ﻓﻰ‬ ‫ﻣﻌﻴﻨﻪ‬ ‫ﻧﻘﻄﻪ‬ ‫ﻋﻠﻰ‬ ‫ﻳﺴﺨﺪﻡ‬ ‫ﺍﻟﺘﻴﺎﺭ‬ ‫ﻣﺤﻮﻝ‬ ‫ﻻﻥ‬ ‫ﺫﻟﻚ‬‫ﻮﻥ‬voltage drop‫ﻳﻘﻮﻡ‬ ‫ﻭﻋﻨﺪﻣﺎ‬ ‫ﺿﺌﻴﻴﻞ‬ ‫ﺍﻟﻨﻘﻄﻪ‬ ‫ﻫﺬﻩ‬ ‫ﻋﻨﺪ‬c.t ‫ﺍﻻﺟﻬﺰﻩ‬ ‫ﻋﻞ‬ ‫ﺧﻄﻮﺭﻩ‬ ‫ﺗﻤﺜﻞ‬ ‫ﻻ‬ ‫ﺻﻐﻴﺮ‬ ‫ﺍﻟﻤﻜﺒﺮﻩ‬ ‫ﺍﻟﻘﻴﻤﻪ‬ ‫ﺗﻜﻮﻥ‬ ‫ﺍﻟﺠﻬﺪ‬ ‫ﺑﺘﻜﺒﻴﺮ‬.  ****************************************************************************************