14 Journal of Electrical Engineering & Technology Vol. 6, No. 1, pp. 14~24, 2011DOI: 10.5370/JEET.2011.6.1.014 Available Transfer Capability Enhancement with FACTS Devices in the Deregulated Electricity Market B.V. Manikandan†, S. Charles Raja* and P. Venkatesh* Abstract – In order to facilitate the electricity market operation and trade in the restructured environ- ment, ample transmission capability should be provided to satisfy the demand of increasing power transactions. The conflict of this requirement and the restrictions on the transmission expansion in the restructured electricity market has motivated the development of methodologies to enhance the avail- able transfer capability (ATC) of existing transmission grids. The insertion of flexible AC transmission System (FACTS) devices in electrical systems seems to be a promising strategy to enhance single area ATC and multi-area ATC. In this paper, the viability and technical merits of boosting single area ATC and multi-area ATC using Thyristor controlled series compensator (TCSC), static VAR compensator (SVC) and unified power flow controller (UPFC) in single device and multi-type three similar and dif- ferent device combinations are analyzed. Particle swarm optimization (PSO) algorithm is employed to obtain the optimal settings of FACTS devices. The installation cost is also calculated. The study has been carried out on IEEE 30 bus and IEEE 118 bus systems for the selected bilateral, multilateral and area wise transactions. Keywords: Available transfer capability, Flexible AC transmission systems, Particle swarm optimiza- tion, Power transfer dsistribution factors, Participation factors, Installation cost 1. Introduction the increasingly difficult economic, environmental, and social problems, have led to a much more intensive shared The restructuring of the electric industry throughout the usage of existing transmission facilities by utilities andworld aims to create competitive markets to trade electric- independent power producers (IPPs). These concerns haveity and generates a host of new technical challenges to motivated the development of strategies and methodologiesmarket participants and power system researchers. For to boost the ATC of existing transmission networks.transmission networks, one of the major consequences of FACTS technology enables line loading to increasethe non-discriminatory open-access requirement is a sub- flexibly, in some cases, even up to the thermal limits.stantial increase of power transfers, which demand ade- Therefore, it can theoretically offer an effective and prom-quate available transfer capability (ATC) to ensure all ising alternative to conventional methods for ATC en-transactions are economical. Researchers have proposed hancement. Undoubtedly, it is very important and impera-the computation of ATC using AC power transfer distribu- tive to carry out studies on exploitation of FACTS technol-tion factors (ACPTDF) -. New methods of evaluating ogy to enhance ATC -. The modeling of FACTSATC in a competitive environment are proposed in previ- devices for power flow studies, the role of such modelingous research, . With the introduction of competition for power flow control and the integration of these devicesin the utility industry, it is possible for customers to buy into power flow studies were reported in the literature ,less expensive electrical energy from remote location. As a . Modeling and the role of important FACTS devicesresult, system operators face the need to monitor and coor- like static VAR compensator (SVC), Thyristor controlleddinate power transactions taking place over long distances series compensator(TCSC) and unified power flow control-in different areas. Therefore, it becomes essential to evalu- ler (UPFC) in solving power system restructuring issuesate multi-area ATC, and a novel method for determining have been previously reported -.multi-area ATC has been presented in the literature. Some well established search algorithms such as GA Sufficient ATC should be guaranteed to support free  and evolutionary programming (EP) ,  weremarket trading and maintain an economical and secure successfully implemented to solve simple and complexoperation over a wide range of system conditions. However, problems efficiently and effectively. Most of the populationtight restrictions on the construction of new facilities due to based search approaches are motivated by evolution as seen in nature. Particle Swarm Optimization (PSO), on the† Corresponding Author: Mepco Schlenk Engineering College, other hand, is motivated from the simulation of social be- Sivakasi Tamilnadu, India. (firstname.lastname@example.org) havior and was introduced by Eberhart and Kennedy .* Thiagarajar College of Engineering, Madurai, TamilNadu, India. Instead of using evolutionary operators to manipulate indi- (email@example.com, firstname.lastname@example.org) viduals, like in other evolutionary computational algo-Received: March 25, 2010; Accepted: June 7, 2010
B.V.Manikandan, S.Charles Raja and P.Venkatesh 15rithms, each individual in PSO flies in the search space Pijmax Pij0 with velocity that is dynamically adjusted according to its ; ACPTDFij , mn 0 own and its companion’s flying experience. The velocity of ACPTDFij , mn the particle that is updated according to its own previous Tij , mn (infinite ) ; ACPTDFij , mn 0 (3)best position and the previous best position of its compan- ( Pij Pij ) ; max 0 ACPTDFij , mn 0 ions and more information are available in previous re-search . PSO is now applied for solving electrical en- ACPTDFij , mn gineering related problems . In this paper, single area ATC is calculated using Where the following holds true:ACPTDF and multi-area ATC with ACPTDF and participa-tion factors (PFs) in combined economic emission dispatch Pijmax is the MW power limit of a line between bus i and j.(CEED) environment , . An attempt is made to en- Pijo is the base case power flow in line between bus i and j.hance ATC using TCSC, SVC and UPFC in single device NL is the total number of lines.and multi-type three similar and different device combina- ACPTDFij,mn is the power transfer distribution factor fortions. Limiting element strategy is proposed for placement the line between bus i and j when a transaction is takingof FACTS devices. Both bilateral and multilateral transac- place between bus m and n.tions are considered for single area ATC and area- wisetransaction is considered for multi-area ATC enhancement. ACPTDF as given in equation (3) is operating point de-The optimal settings of FACTS devices are obtained from pendent and was computed using Jacobian inverse.PSO Algorithm. The installation cost of FACTS devices ACPTDFs remain fairly constant for reasonable variations has also been calculated. For the selected transactions, in power injections. The method of formulating ACPTDFthe best single device type and multi-type device combina- is common for both single area and multi-area ATC evalua-tion have been suggested with reference to ATC enhanced tion and this is explained in section 2.2. For multi-areavalue and installation cost. The results are illustrated on ATC calculation, in addition to ACPTDFs, PFs should alsoboth IEEE 30 bus and IEEE 118 bus systems. be included and it is explained in section 2.3. In this paper, the optimal settings of generators under CEED environ- ment are considered as a base case power flow, which is 2. ATC explained in section 2.1. ATC is a measure of the transfer capability remaining in 2.1 CEED Problem Formulationthe physical transmission network for further commercialactivity over and above the already committed uses. It can In the restructured environment, generator companiesbe expressed as follows: are generally responsible for the re-dispatch of power by considering the emissions according to state laws and sub- ATC TTC Existing Transmissi on Commitment s (1) mit their bids to the transmission system operator, which is responsible for calculating ATC before committing the Where, Total Transfer Capability (TTC) is defined as the transactions. However, in most developing countries, theamount of electric power that can be transferred over the restructuring process of power industry is still in the infantinterconnected transmission network or particular path or stage wherein the structure is vertically integrated but theinterface in a reliable manner while meeting all of a spe- power is purchased from IPPs to meet the growing demand.cific set of defined pre and post contingency conditions. Hence, the regional transmission operator is responsible for the re-dispatch of generator power by considering the ATC at the base case, between bus m and bus n using physical limits of the system and the emissions standards.line flow limit (thermal limit) criterion is mathematically Furthermore, there are some power markets that supportformulated using ACPTDF as given in the below equation: both bilateral transactions based on ATC and centralized dispatch based on bids. In these markets, assured firm ATCmn min Tij , mn , ij N L (2) transactions are implemented first and then they will fol- low centralized dispatch mechanism with the remaining transfer capacity. Therefore the proposed CEED based ATC Where Tij,mn denotes the transfer limit values for each calculation method can be well suited for such cases de-line in the system. It is given by the following: scribed above. The optimization of CEED problem has been mathe- matically formulated and is given by the following equa- tion: Ng min fi ( FC , EC ) (4) i 1
16 Available Transfer Capability Enhancement with FACTS Devices in the Deregulated Electricity Market Where is the optimal cost of generation (US$/h) and Pi t k Pj t k (8)Ng represents the number of generators connected in thenetwork. FC represents the total fuel cost of generation in With the above mismatch vector elements, the change inUS$/h and EC denotes the total emission of generation in voltage angle and magnitude at all buses can be computedlb/h. The cost is optimized with the constraints such as from (7) & (8) and, hence, the new voltage profile can bepower flow equation of the power network, satisfying calculated. These can be utilized to compute all the trans-power balance equation, inequality constraint on real mission quantities ql and hence the corresponding in thesepower generation of each generator i, inequality constraint quantities ∆ql from the base case. Once the ∆ql for all theon voltage of each PQ bus and power flow limit on each lines corresponding to a change in transaction ∆tk is known,transmission line. PTDFs can be obtained from (6). These ACPTDFs, which The bi-objective optimization problem (4) is converted are computed at a base load flow condition, have been util-into single optimization problem by introducing price pen- ized for computing change in transmission quantities atalty factor, h in $/lb, which blends fuel cost with emission, other operating conditions as well.as expressed by the following: 2.3. PF for Multi-area ATC Calculation Minimize ( FC h EC ) (5) For transaction taking place between two areas i.e. one is CEED optimization problem is solved using EP, subject the seller area and the other is the buyer area, the multi-to the constraints mentioned above. More information is areaalso available in the literature , . ATC problem formulation is as follows: For each generator inside the area, the actual participa-2.2 ACPTDF Formulation tion factor used is the following; ACPTDFs determine the linear impact of a transfer (or Geni PFi (9)changes in power injection) on the elements of the power All Geni in an area system. These values provide a linearized approximation ofhow the flow on the transmission lines and interfaces Where Geni represents the real power generation capac-change in response to transaction between the seller and ity of generator i. Assuming the inverse of Jacobian i.e.,the buyer. Considering a bilateral transaction tk between a [JT]-1 is [ST], equation (7) can be written as follows:seller bus m and buyer bus n, line l carries the part of thetransacted power and is connected between buses i and j. P For a change in real power in the transaction between the V S T Q (10)above buyer and seller by ∆tk MW, if the change in a transmission line quantity q1 is ∆q1 , power transfer distri-bution factors can be defined as follows: In the above equation, Pk = 0, where k = 1. . . . h, k i, j and Q = 0. In the transaction matrix for seller area, in ql the place of generators, the PF value assigned is as follows: ACPTDFij ,mn (6) t k n The transmission quantity ql can be either real power PSi = + PFi subject to PF i 1 i 1 (11)flow from bus i to bus j (Pij ) (or) real power flow frombus j to bus i (Pji ). The above factors have been proposed Meanwhile, in the transaction matrix for the buyer area,to compute at a base case load flow with results using the in the place of generators, the PF value assigned is the fol-sensitivity properties of NRLF Jacobian. Consider full lowing:Jacobian in polar coordinates [JT], which is defined to in-clude all the buses except slack (also including ∆Q-∆V nequations for PV buses), we get the following: PBj = - PFj subject to PF j 1 j 1 (12) 1 P P Where n = the number of generators in the buyer and V P J 1 P V Q Q Q T Q (7) seller areas. All other entries in the buyer and seller area transaction matrices other than PSi and PBj are zeros. V The change in voltage angle and magnitude at all buses present in the areas are calculated and hence the new volt- In a base case load flow, if only one of the kth bilateral age profile can be determined. Area wise PTDF is simplytransactions is changed by ∆tk MW, only the following two a function of these voltages and angle sensitivities, there-entries in the mismatch vector on right hand side of (7) will fore, the calculation of multi-area ATC is similar to thebe non zero.
B.V.Manikandan, S.Charles Raja and P.Venkatesh 17procedure followed for single area ATC. More information 3.3 Device Placement Strategyabout multi-area ATC is available in a previous study . ATC value is greatly influenced by the power flow in the limiting line of the system. Therefore, a FACTS device is 3. FACTS Devices placed in the limiting line or at the corresponding bus to which the limiting line is connected depending on the type The insertion of FACTS devices in electrical systems of device. Only one FACTS device per line is allowed. Ifseems to be a promising strategy to increase available only one device is used, it is placed in the first limiting linetransfer capability (ATC) -. of the system. If three devices are to be inserted, then the first three limiting lines are selected. For this purpose, the3.1 Selection of Devices limiting lines in the considered test systems are ranked and ordered based upon the power carrying capacity in the line. FACTS devices are categorized under four different head- For the multi-type device category, TCSC is considered asings as series controllers, shunt controllers, combined series- the first device, SVC as the second and UPFC as the third .shunt controllers and combined series-series controllers. In If the device is TCSC, it is connected in series with thethis paper, one device from each category is selected i.e., limiting line. If the device is SVC, then the type of origi-TCSC from series controllers, SVC from shunt controllers nating bus and terminating bus of the limiting line isand UPFC from combined series-shunt controllers. checked. If the one end bus is PV bus, it is discarded and if TCSC is connected in series with the line conductors to the other end bus is PQ bus, then SVC is connected. Sup-compensate for the inductive reactance of the line. It may pose if two end buses happen to be PV buses, then the nexthave one of the two possible characteristics namely capaci- limiting line in the order is selected and checked for type oftive or inductive, respectively to decrease or increase the bus. For UPFC, the series device TCSC is connected inreactance of the line XL respectively. Moreover, in order series with the limiting line and the shunt device SVC isnot to overcompensate the line, the maximum value of the connected at PQ bus after checking the type of the endcapacitance is fixed at -0.8XL while that for inductance, it is buses where the limiting line is connected.0.2XL. Although TCSC is not usually installed for voltagecontrol purpose, it does contribute for better voltage profileand reactive power control. 4. Problem Formulation SVC is used for voltage control applications. It helps tomaintain a bus voltage at a desired value during load varia- The aim of the optimization is to perform the best utili-tions. The SVC may have two characteristics namely, in- zation of the existing transmission lines. The objective is toductive or capacitive. In the inductive mode, it absorbs maximize the ATC i.e., uncommitted active transfer capac-reactive power, whereas in the capacitive mode, reactive ity of the prescribed interface, when a transaction is takingpower is injected. It may take values characterized by the place between a seller bus (m) and buyer bus(n). It is repre-reactive power injected or absorbed at the voltage of 1 p.u. sented as follows:The values are between -100 Mvar and 100 Mvar. The UPFC is capable of providing active and reactive Maximize ( ATCm n ) (13)power control, as well as adaptive voltage magnitude con-trol and regulates all the three variables simultaneously or Whereany combination of them, provided no operating limitsare violated. The UPFC may act as an SVC, a TCSC or aphase shift controller. The versatility afforded by the UPFC ATCmn min Tij , m n , ij N L as given in equation (2)makes it a prime contender to provide many of the controlfunctions required to solve a wide range of dynamic and 4.1 FACTS device’s constraintssteady state problems encountered in electrical power net-works . UPFC can be modeled as a combination of one The constraints on the FACTS devices used in this workseries element i.e., TCSC and a shunt element i.e., SVC are given below:. Hence the operational range limits of TCSC and SVCcan be applied to UPFC as well. i) 0.8 X L X TCSC 0.2 X L p.u (14)3.2 Modeling of FACTS Devices ii) 100 MVAR QSVC 100 MVAR (15) iii) Equations (20) & (21) for UPFC (16) TCSC has been modeled as a variable reactance insertedin the transmission line connected between buses. SVC is Where XTCSC is the reactance added to the line by placingmodeled as a reactive power source added or connected at TCSC, XL is the reactance of the line where TCSC is lo-the bus. Based on previous research , UPFC is modeled cated and QSVC is the reactive power injected at the bus byas combination of an SVC at a bus and a TCSC in the line placing SVC.connected to the same bus.
18 Available Transfer Capability Enhancement with FACTS Devices in the Deregulated Electricity Market4.2 Power Flow Constraints 5. Overview of PSO The power flow constraint is given by: PSO is a population-based optimization method that was first proposed by Kennedy and Eberhart . This tech- g ( v , ) 0 (17) nique finds the optimal solution using a population of par- ticles. PSO is developed through the simulation of bird Where flocking in two-dimensional space. The position of each agent is represented in the X-Y plane with position (Sx, Sy), Vx (velocity along X-axis), and Vy (velocity along Y-axis). Pi ( v , ) Pi net Modification of the agent position is realized by the posi- Q ( v , ) Q net For each PQ bus i tion and velocity information. Bird flocking optimizes a g (V , ) i i (18) certain objective function. Each agent knows its best value, Pm ( v , ) Pmnet For each PV bus m , thus called “Pbest”, which contains the information on posi- not including ref . bus tion and velocities. This information is the analogy of per- sonal experience of each agent. Moreover, each agent knows the best value so far in the group, “Gbest” among all Pi , Qi represents calculated real and reactive power for “Pbest”. This information is the analogy of knowledge, onPQ bus i respectively. Pi net and Qinet denotes specified how the other neighboring agents have performed. Each agent tries to modify its position by considering currentreal and reactive power PQ bus i respectively. Pm and positions (Sx, Sy), current velocities (Vx, Vy), the individual netPm represents calculated and specified real power for PV intelligence (Pbest), and the group intelligence (Gbest). The following equations are utilized, in computing thebus m, respectively. v and represents voltage magni- position and velocities, in the X-Y plane:tude and phase angles at different buses, respectively. Vi k 1 W Vi k C1 rand1 ( Pbesti Sik ) 4.3 Installation Cost (22) C2 rand 2 ( Gbest Sik ) The installation cost of the corresponding FACTS de-vices are given by, Sik 1 Sik Vi k 1 (23) IC C * S *1000 (19) Where,Vik+1 is the velocity of ith individual at (k + 1 )thwhere IC denotes optimal installation cost of FACTS de- iteration, Vik is the velocity of ith individual at kth iteration,vices in US$. C represents cost of installation of FACTS W is the inertia weight, C1 and C2 are the positive con-devices in US $/KVar. stants having values (0,2.5), rand1 and rand2 are the random The cost of installation of UPFC, TCSC and SVC are numbers selected between 0 and 1, Pbesti is the best posi-taken from Siemens data base and reported in . The tion of the ith individual, Gbest is the best position amongcost of installation of various FACTS devices are given by the individuals (group best) and Sik is the position of iththe following equations: individual at kth iteration. The acceleration coefficients C1, and C2 control how far a particle will move in a single it- CUPFC 0.0003 S 2 0.2691S 188.22 eration. Typically, these are both set to a value of 2.5. CTCSC 0.0015 S 2 0.7130S 153.75 (20) The velocity of each particle is modified according to (22) and the minimum and maximum velocity of each vari- CSVC 0.0003 S 0.3051S 127.38 2 able in each particle is set within the limits of Vmin and Vmax respectively. The position is modified according to (23). Where S is the operating range of the FACTS devices in The inertia weight factor “W” is modified using (24) toMVAR and it is given by: enable quick convergence . S Q2 Q1 (21) (Wmax Wmin ) W Wmax iter (24) itermax Where Q2 is the reactive power flow in the line afterinstalling FACTS device in Mvar and Q1 represents reac- Where Wmax is the initial value of inertia weight equal to 0.9, Wmin is the final value of inertia weight equal to 0.4,tive power flow in the line before installing FACTS device iter is the current iteration number and itermax is the maxi-in Mvar. mum iteration number. Small values of w result in more rapid convergence usually on a suboptimal position, while a too large value may prevent divergence of solution. The
B.V.Manikandan, S.Charles Raja and P.Venkatesh 19PSO system combines two models; a social-only model considered in this test system.and a cognition-only model. These models are representedby the velocity update, shown in (22). More information is Bilateral Transactionalso available in . ATC value at the base case without employing FACTS device is determined first, afterwards ATC is determined by 6. Simulation Results and Discussions employing FACTS devices in the single and multi-type three similar and different device combinations. Table 1 In this paper, for the single and multi-area ATC determi- shows the results. The first four limiting lines are obtainednation, the generator settings of the test systems are ob- for this transaction and the order of limiting lines are linestained from CEED environment as explained in [6, 18]. 6-28, 2-6, 6-8 and 22-24. The PSO convergence curve forThe thermal limit of each line is considered as a constraint. this transaction utilizing single UPFC is shown in Fig. 1.Three types of FACTS device i.e., TCSC, SVC and UPFC In the multi-type, similar devices combination, threeare employed separately first and in three similar and dif- TCSCs are placed in the first three limiting lines i.e., 6-28,ferent device combinations to enhance ATC. One set of 2-6 and 6-8. Similarly, three SVCs are placed at buses 28, 6bilateral and multi-lateral transaction is considered for the and 8. For the three UPFCs, the placement of three TCSCstwo IEEE test systems in the single area configuration and and three SVCs are similar to the three similar devices. Inone area-wise transaction is considered for the two IEEE the single device type, UPFC is providing maximum en-test systems in the multi-area configuration. The optimal hancement of ATC. Considering multi-type similar andsettings of FACTS devices are obtained from PSO Algo- different device combinations, three UPFCs are providingrithm. Installation cost of FACTS devices has also been maximum enhancement of ATC. However, considering thecalculated and the best single and multi-type device is sug- cost of installation, TCSC-SVC-UPFC combination seemsgested for each transaction with reference to ATC value to be very effective for this transaction.and cost of installation. The simulation studies are carriedout on Intel Pentium Dual Core, 2.40 GHz system inMATLAB 7.3 environment.6.1 Single area ATC Enhancement The bus data and line data of the two IEEE test systemsare taken from  and the CEED base case values of thegenerators are obtained as explained in [6, 18].6.1.1 IEEE 30 Bus System One bilateral transaction between buses (2-28) and amultilateral transaction between buses (2, 11)-(28, 26) are Fig. 1. PSO convergence curve for single UPFC. Table 1. ATC enhancement results for bilateral transaction (2-28) Settings and placement ATC without ATC with Type of FACTS UPFC Installation Cost ( 106 US $) FACTS FACTS TCSC SVC device(s) TCSC SVC (MW) (MW) (p.u) (Mvar) (p.u) (Mvar) 0.030 TCSC 27.614 - - - 0.29 (6-28) -92.772 SVC 25.413 - - - 4.66 (Bus 28) 0.030 -49.313 UPFC 31.004 - - 3.82 (6-28) (Bus 28) TCSC 0.030 TCSC 24.756 -0.074 - - - 1.67 TCSC -0.021 24.821 SVC -100 SVC 25.637 - 59.258 - - 9.00 SVC -96.432 UPFC 0.026 -99.544 UPFC 33.516 - - 0.088 -99.127 12.27 UPFC -0.021 -50.472 TCSC 0.029 95.651 -0.021 97.228 SVC 30.938 3.21 (6-28) (Bus 6) (6-8) (Bus 8) UPFC
20 Available Transfer Capability Enhancement with FACTS Devices in the Deregulated Electricity Market Multilateral Transaction The order of the first four limiting lines based on thepower flow capacity is 6-28, 25-27, 9-11 and 27-30. Thebase case ATC value is found to be 16.951 MW. In the sin-gle device type, TCSC is placed in series with line 6-28and its settings is 0.104 p.u. SVC is connected at bus 28and its settings is -55.022 Mvar. For UPFC, the series ele-ment is connected in the line 6-28, while the shunt elementis connected at bus 28. The settings of the shunt and serieselements are 0.046 p.u and -53.637 Mvar respectively. Forthe three similar device combinations, three TCSCs are Fig. 2. ATC results - multilateral transaction of IEEE 30placed in series with the lines 6-28, 25-27 and 9-11 with bus system.settings of 0.104 p.u, 0.030 p.u and -0.083 p.u respectively.Similarly, three SVCs are connected at buses 28, 25 and 9with settings of -60.013 Mvar, -11.584 Mvar and 100 Mvar.For the three UPFCs, the settings of the series elements are-0.104 p.u, 0.030 p.u and -0.104 p.u. The three shuntelements have the settings are -53.081 Mvar, -91.774 Mvarand 100 Mvar respectively. For the three different devicecombination, TCSC is connected in the line 6-28 withsetting of 0.029 p.u, SVC is connected at bus 25 withsetting of -97.643 Mvar and for UPFC, the series elementin the line 9-11and shunt element at bus 9. Thecorresponding settings are -0.046 p.u and 89.225 Mvar. Fig.2 shows the ATC enhancement results with single and Fig. 3. Installation Cost - multilateral transaction of IEEEmulti-type three similar and different device combinations. 30 bus system. The installation cost details are shown in Fig. 3. For themulti-lateral transaction, in the single device category, 6.1.2 IEEE 118 Bus SystemTCSC is considered to be the best since it provides One bilateral transaction between buses (49-100) and amaximum improvement of ATC with minimum cost of multilateral transaction between buses (25,59,46)- (89,100,installation. In multi-type similar and different device 103,111) are considered in this large test system.combinations, three UPFCs are providing maximum en-hancement of ATC at very high installation cost. However, Bilateral Transactionconsidering the cost of installation, three SVCs are sug- The first four limiting lines for this transaction is foundgested to be the best for this transaction. to be lines 81-80, 68-81, 94-100 and 69-77. The results are given in Table 2. Table 2. ATC enhancement results for bilateral transaction (49-100) Settings and placement ATC without ATC with Type of FACTS UPFC Installation Cost ( 106 US $) FACTS FACTS TCSC SVC device(s) (MW) (MW) (p.u) (Mvar) TCSC SVC (p.u) (Mvar) TCSC 425.984 0.019 (81-80) - - - 5.63 -97.025 SVC 395.940 - - - 3.02 (Bus 81) UPFC 425.986 - - 0.018(81-80) -68.213 (Bus 81) 10.18 TCSC 0.018 TCSC 448.845 0.010 - - - 11.90 TCSC 0.007 393.851 SVC -100 SVC 397.085 - -93.664 - - 7.69 SVC 98.335 UPFC 0.019 -90.644 UPFC 447.789 - - 0.010 -81.233 9.67 UPFC -0.018 -85.301 TCSC 0.018 -95.972 -0.027 91.766 SVC 428.891 11.35 (81-80) (Bus 81) (94-100) (Bus 94) UPFC
B.V.Manikandan, S.Charles Raja and P.Venkatesh 21 In the multi-type, similar devices combination, threeTCSCs are placed in the first three limiting lines i.e., 81-80,68-81 and 94-100. Similarly, three SVCs are connected atbuses 81, 68 and 94. For the three UPFCs, the placement ofthree TCSCs and three SVCs are the same as that of thethree similar devices mentioned above. In the single device category, UPFC and TCSC are pro-viding equal improvement in ATC value. However, theinstallation cost for UPFC is almost twice times when com-pared with that for TCSC. Therefore, TCSC is the effectivedevice for this transaction. Considering multi-type similarand different device combinations, three TCSCs are pro- Fig. 5. Installation cost– multilateral transaction of IEEEviding maximum enhancement compared to all other com- 118 bus system.binations. Therefore, for this transaction, the combinationof three TCSCs combination is the most effective followed For this multi-lateral transaction, UPFC is the bestby the three UPFCs. device in the single device type. SVC and three SVC combinations are proved to be ineffective for this Multilateral Transaction multilateral transaction. In the multitype, similar and The four limiting lines in the order of power flow for different device combinations, three UPFCs and TCSC-this transaction are 100-103, 81-80, 69-77 and 68-81. The SVC-UPFC combinations are producing equal enhancement.ATC value without FACTS device is 51.072 MW. The ob- Cosidering the cost details, the TCSC-SVC-UPFCtained ATC enhancement results are shown in Fig. 4. The combination is proved to most promising one.installation cost details are shown in Fig. 5. In the singledevice type, TCSC is placed in series with the line 100-103 6.2 Multi- area ATC Enhancementwith settings of 0.026 p.u. Since buses 100 and 103 are PVbuses, SVC is connected at bus 81 with settings of 65.773 For the multi-area ATC determination, two areas areMvar. For UPFC, since buses 100 and 103 are PV buses, considered for the IEEE 30 bus system and three areas arethe series element is connected in the line 81-80 and the considered for the IEEE 118 bus system.shunt element is connected at the bus 81. The settings ofthe shunt and series elements are 0.026 p.u and -58.961 6.2.1 IEEE 30 Bus SystemMvar respectively. For the three similar device combinations,three TCSCs are placed in series with the lines 100-103, There are six generators present in this system. Genera-81-80 and 69-77 with settings of 0.026 p.u, -0.008 p.u and tors at buses 8, 11 and 13 are considered in area 1, while-0.010 p.u. Similarly, three SVCs are connected at buses 81, the remaining generators at buses 1, 2 and 5 are considered77 and 68 with settings of 43.882 Mvar, 85.406 Mvar and in area 2. The tie-lines existing between the two areas are100 Mvar respectively. For the three UPFCs, the settings of shown in Fig. 6. Transaction is carried out between Area 1the series elements are 0.0262 p.u, 0.003 p.u and -0.010 p.u and Area 2. The first four limiting lines are lines 12-13, 15-respectively. The settings of the three shunt elements are 23, 6-8 and 15-18. Table 3 shows the ATC improvement15.048 Mvar, -72.141 Mvar and 81.511Mvar. For the three results for this area- wise transaction.different device combination, TCSC is connected in the line In the multi-type, similar devices combination, three100-103 with setting of 0.027 p.u, SVC is connected at bus TCSCs are placed in the first three limiting lines i.e., 12-13,81 with setting of -66.458 Mvar and for UPFC, the series 15-23 and 6-8. Similarly, three SVCs are connected atelement in the line 69-77 and shunt element at bus 77. The buses 12, 23 and 8. For the three UPFCs, placement ofcorresponding settings are -0.010 p.u and 90.973 Mvar. three TCSCs and three SVCs is the same as that of the three similar devices. In the single device type, TCSC is providing maximum enhancement of ATC with minimum cost. Considering multi-type similar and different device combinations, three UPFCs are providing the maximum enhancement of ATC but its cost is moderately high. In addition, the combinationFig. 4. ATC results- multilateral transaction of IEEE 118 bus system. Fig. 6. Tie-lines between areas – IEEE 30 Bus system.
22 Available Transfer Capability Enhancement with FACTS Devices in the Deregulated Electricity MarketTable 3. Multi-area ATC Enhancement results for IEEE 30 Bus system Settings and placement ATC without Type of FACTS ATC with FACTS UPFC Installation cost ( 106 US $) FACTS TCSC SVC device(s) (MW) TCSC SVC (MW) (p.u) (Mvar) (p.u) (Mvar) 0.067 TCSC 94.552 - - - 2.28 (12-13) -95.771 SVC 93.258 - - - 2.69 (Bus 12) 0.070 -83.788 UPFC 94.053 - - 3.06 (12-13) (Bus 12) -0.0346 TCSC -0.0128 TCSC 95.710 - - - 2.67 0.010 92.613 TCSC SVC 15.589 5.53 SVC 95.299 - -83.552 - - SVC 11.077 UPFC 0.048 -100 UPFC 98.038 - - 0.017 3.446 6.12 UPFC 0.021 -85.638 TCSC -0.054 -57.017 0.021 -69.293 SVC 96.371 3.55 (12-13) (Bus 23) (6-8) (Bus 6) UPFCTCSC-SVC-UPFC seems to be the next best as it has pro-vided marginal improvement of ATC at minimum cost ofinstallation.6.2.2 IEEE 118 Bus system For the multi-area ATC evaluation, three areas are con-sidered in the IEEE 118 bus system. This system has 19generators. The generators and buses allocation for eacharea is given in Table 4. The lines between area 1 and area2 are the lines between buses 15-33, 19-34, 30-38, 75-69,75-118, 75-77 and 70-69. The lines connecting area 2 and Fig. 7. Multi-area ATC enhancement results- IEEE 118 busarea 3 are the lines between buses 77-82, 80-96, 97-96, 98- system.100 and 99-100. Similarly, the lines connecting area 1 andarea 3 are the lines between buses 70-24, 72-24 and 23-24.Transactions are carried out between area 1 and area 2;area 1 and area 3; and area 2 and area 3. The order of first four limiting lines is 81-80, 68-81, 69-77 and 100-103. Transaction is carried out between area 2-area 3. The enhanced multi-area ATC results are shown inFig. 7 and the installation cost details are shown in Fig. 8.In the single device type, TCSC is connected in series withthe first limiting line 81-80 and its setting is 0.018 p.u.SVC is connected at bus 81 and the Mvar settings obtainedfrom the PSO is -99.231 Mvar. For UPFC, the series ele-ment in the line 81-80 has the setting of 0.019 p.u and theshunt element at bus 81 has the setting of -67.144 Mvar. Fig. 8. Installation cost details –IEEE 118 bus system. Table 4. Area-wise generators / buses allocation for IEEE 118 bus system Area / Generators Area / Buses Area 1 Area 2 Area 3 Area 1 Area 2 Area 3 46, 49, 54, 59, 61, 1-23, 25-35, 33-69, 76-81, 97-99, 10, 12, 25, 26, 31 87, 89, 100, 103, 111 24, 82-96, 100-112 65, 66, 69, 80 70-75, 113-115, 117 116, 118
B.V.Manikandan, S.Charles Raja and P.Venkatesh 23 In the three similar device combinations, three TCSCs  A.M. Leite da silva, J.G.C. Costa, L.A.F. Manso andare placed in series with the lines 81-80, 68-81 and 69-77 G.J. Anders, “Evaluation of transfer capabilities ofwith settings of -0.019 p.u, 0.010 p.u and 0.050 p.u. transmission systems in competitive environments”,respectively. Similarly, three SVCs are connected at buses Electrical Power and Energy systems, Vol. 26, No. 4,81, 68 and 77 with settings of -47.897 Mvar, -100 Mvar pp. 257-263, 2004.and 95.846 Mvar respectively. For the three UPFCs, the  M.M Othman, A. Mohamed and A. Hussain, “Fastsettings of the series elements are 0.018 p.u, -0.0003 p.u Evaluation of Available Transfer Capability usingand -0.0005 p.u. The settings of the three shunt elements Cubic-spline interpolation technique”, Electric Powersettings are -82.951 Mvar, -50.133 Mvar and -12.484 Mvar. systems research, Vol. 73, No. 3, pp. 335-342, 2005.For the TCSC-SVC-UPFC combination, the TCSC is con-  B.V. Manikandan, S. Charles Raja, P. Venkatesh andnected in series with the line 81-80, the SVC is connected P.S Kannan, “Available Transfer Capability Determi-at bus 81, the series device of UPFC in the line 69-77 and nation in the Restructured Electricity Market. Electri-the shunt device of UPFC at bus 77. The corresponding cal Power Components and Systems, Vol. 36, No. 9,settings are 0.017 p.u, -90.763 Mvar, 0.002 p.u and -29.18 pp. 941-959, 2008.Mvar.  Y. Xiao and Y.H. Song, “Application of Stochastic For this transaction, in the single device type, UPFC has Programming for Available Transfer Capability En-been proven to be more effective since it enhances ATC to hancement using FACTS Devices”, Proceedings ofthe maximum. Considering all multi-type combinations, 2000 IEEE/PES Summer Meeting, Seattle, WA, Vol. 1,three TCSCs and three UPFCs are equally effective since pp. 508-515, 2000.the corresponding ATC values and installation costs are  Y. Xiao, Y.H.Song and Y.Z. Sun, “Application ofsimilar. However, three UPFCs have a slight edge over Unified Power Flow Controller to Available TransferTCSCs. Capability Enhancement” IEEE Power Engineering Review, Vol. 72, pp.66-68, 2001.  K.S.Verma, S.N. Singh and H.O. Gupta, “FACTS 7. Conclusion device Location for Enhancement of Total Transfer Capability”, IEEE Power Winter meeting, January, FACTS devices can boost the single area ATC and multi- Ohio, USA, Vol. 2, pp. 522-527, 2001.area ATC substantially. The considerable difference be-  Y. Xiao, Y.H. Song, C.C. Liu and Y.Z. Sun, “Avail-tween ATC values with and without FACTS devices for the able transfer capability enhancement using FACTSconsidered transactions justifies that the FACTS technol- devices” IEEE Transactions on Power Systems, Vol.ogy can offer an effective and promising solution to en- 18, No. 1, pp. 305-312, 2003.hance the usable power transfer capability, thereby improv-  D.J. Gotham and G.T. Heydt, “ Power Flow controling transmission services of the competitive electricity and power flow studies for systems with FACTS de-market. vices” IEEE Transactions on Power Systems, Vol. 13, The effect of FACTS devices on ATC enhancement is No. 1, pp. 60-65, 1998.system dependent. For the bilateral, multilateral and area-  D. Povh, “Modeling of FACTS in power system stud-wise transactions considered in the two IEEE test systems, ies. IEEE Power Engineering Society Winter Meeting,the role played separately by TCSC, SVC and UPFC for Vol. 2, pp. 1435-1439, 2000.boosting ATC in single device type and multi-type three  A. Kazemi and B. Badrzadeh, “Modeling and simula-similar and three different devices combinations are ana- tion of SVC and TCSC to study their limits on maxi-lyzed. Effective single device and effective combination of mum loadability point”, Electrical Power and Energydevices have also been suggested for the considered trans- Systems, Vol. 26, pp. 619-626, 2004.actions.  S.N. Singh, “Role of FACTS devices in competitive power market. Proceeding of short term course on Electric Power system operation and management in References restructured environment (IIT, Kanpur), pp. A.71- A.80, 2003.  H. Sawhney and B. Jeyasurya, B, “Application of J.Weber, “Efficient Available Transfer Capability Unified Power Flow Controller for Available Transfer Analysis using Linear methods”, PSERC internet capability enhancement”, Electric Power Systems Re- seminar, UL, USA, Nov 7, 2000. search, Vol. 69, No. 2-3, pp. 155-160, 2004. A.Kumar and S.C. Srivatsava, “AC Power Distribu-  S. Gerbex, R. Cherkaoui and A.J. Germond, “Optimal tion Factors for allocating Power transactions in a de- Location of Multi-type FACTS devices by Means of regulated environment”, IEEE Power Engineering Genetic Algorithm”, IEEE Transactions on Power Review, pp. 42-43, 2002. Systems, Vol. 16, No. 3, pp. 537-544, 2001. A. Kumar, S.C. Srivatsava and S.N.Singh, “ATC de-  T.T. Ma, “Enhancement of Power Transmission sys- termination in a competitive electricity market using tems by using multiple UPFC on Evolutionary Pro- AC Distribution Factors”, Electrical Power compo- gramming”, IEEE Bologna Power Technical Confer- nents and Systems, Vol. 32, No. 9, pp. 927-939, 2004.
24 Available Transfer Capability Enhancement with FACTS Devices in the Deregulated Electricity Market ence, Vol. 4, pp. 23-26, 2003. S. Charles Raja is presently working P. Venkatesh, R. Gnanadass and N.P. Padhy, “Com- as Lecturer in the Department of parison and application of Evolutionary programming Electrical and Electronics Engineering techniques to combined economic emission dispatch of Thiagarajar College of Engineering, with line flow constraint”, IEEE Transactions on Madurai. He obtained his B.E., in Power systems, Vol. 18, No. 2, 688-697, 2003. Electrical and Electronics Engineering J.Kennedy and R. Eberhart, “Particle Swarm Optimi- in 2005 and M.E., in Power Systems zation”, Proceedings of IEEE international confer- Engineering in 2007 from Anna ence on Neural Networks, Piscataway, NJ, Vol. IV, pp. University, Chennai. His topics of interest include Power 1942-1948, 1995. system security, Power system optimization techniques, M.A.Abido,“Optimal Power Flow using Particle control systems, application of FACTS controllers for all Swarm Optimisation”, Electrical Power and Energy power system problems and power system deregulation. Systems, Vol. 24, 563-571, 2002. S.Kannan, S.M.R.Slochanal, P.Subbaraj and N.P.Padhy, “Application of Particle swarm optimization tech- nique and its variants to generation expansion plan- P. Venkatesh received his degree in ning problem”, Electric Power Systems Research, Vol. Electrical and Electronics Engineering, 70, pp. 203-210, 2004. Masters in Power System Engineering L.J. Cai, I. Erlich and G. Stamtsis, “Optimal choice with distinction and Ph.D from and allocation of FACTS devices in deregulated elec- Madurai Kamaraj University, India in tricity market using genetic algorithms”, IEEE PES 1991, 1994 and 2003, respectively, His Power system conference and Exposition, USA, pp. area of interest is the application of 10-13, 2004. evolutionary computation techniques to M. Saravanan, S.M.R. Sulochanal, P.Venkatesh and power system problems and power system restructuring. J.P.S.Abraham, “Application of particle swarm opti- He has received the Boyscast Fellowship award in 2006 mization technique for optimal location of FACTS from the Department of Science and Technology, India for devices considering cost of installation and system carrying out research work at Pennsylvania State Univer- loadability”, Electric Power Systems Research, Vol. sity, USA. He has more than 16 papers published in repu- 77, No. 3-4, pp. 276-283, 2005. table journals to his credit. He has chaired many techni- http://www.ee.washington.edu/research/ pstca cal sessions in seminars/workshops and gave number of invited lectures in many forums. He is currently, an Asso- ciate Professor in the Department of Electrical and Elec- B.V. Manikandan obtained his B.E., tronics Engineering, Thiagarajar College of Engineering, in Electrical and Electronics Engineering Madurai, India. and M.E., in Power Systems Engineer- ing from Madurai Kamaraj University in 1990 and in 1992 respectively, and Ph.D., degree from Anna University, Chennai in 2010. His Ph.D., work deals with issues of power system restructuring.His special fields of interest includes power system restruc-turing issues and application of FACTS controllers topower system. He is presently working as Assistant Profes-sor in the Department of Electrical and Electronics Engi-neering of Mepco Schlenk Engineering College, Sivakasi.